Вы находитесь на странице: 1из 5

FS300 Specifications

For Bare Panels On Corner-Lock System

NOTE: These specifications conform to CSI MasterFormat 2004/2005 Edition, AIA MasterSpec Section
096900 and to CSI MasterFormat 1995 Edition, AIA MasterSpec Section 10270



A. Drawings and general provisions Contract, including General and Supplementary Conditions and Division
01 Specifications Sections, apply to this section.

A. This section includes:
1. Access flooring panels and understructure
2. Various accessories, including, but not limited to ramps, steps and electrical boxes.
B. Related Sections include the following:
1. Division 3 Section “Cast-In-Place Concrete” for concrete floor sealer.
2. Division 26 Section “Grounding and Bonding for Electrical Systems” for connection to ground of access
flooring understructure.
Note: The electrical contractor shall provide the necessary labor and materials to electrically connect the
access flooring to the building ground to comply with this section.
C. Quantity Allowances: Provide the following as specified in Division 01 Section “Allowances.”
1. Cutouts in floor panels
2. Service outlets

A. Access flooring: A complete portable assembly of modular floor panels on an elevated support system
(understructure), forming an accessible under-floor cavity to accommodate electrical and mechanical
B. ESD: Electrostatic Discharge. The transfer of electric charge between bodies at different potentials.


A. Access Flooring System: Assemblies composed of modular floor panels that are fastened to adjustable
height pedestals.


A. Structural Performance: Provide access flooring system capable of supporting the following loads and
stresses within limits and under conditions indicated, as demonstrated by testing manufacturer’s current
standard products according to referenced procedures in latest revised edition of Ceilings and Interior
Systems Construction Associates (CISCA) “Recommended Test Procedures for Access Floors” referenced
elsewhere in this section as CISCA/AF or, if not specified, manufacturers standard method
1. Concentrated Loads: Provide floor panels, including those with cutouts, capable of withstanding a
concentrated design load of 1,500 lbf. (6672 N) with a top-surface deflection under load not to exceed
0.100 inch (2.54) and a permanent set not to exceed 0.010 inch (0.25) according to CISCA/AF Section
1, “Concentrated Loads”.
2. Ultimate Load: Provide access flooring system capable of withstanding a minimum ultimate load of
three times the concentrated load without failing, according to CISCA/AF, Section 2, “Ultimate
3. Rolling Loads: Provide access flooring system capable of withstanding rolling loads of the following
magnitude, with a combination of local and overall deformation not to exceed 0.040 inch (1.02) mm
after exposure to rolling over CISCA/FA Path A or B, whichever path produced the greatest top surface
deformation, , according to CISCA/AF, Section 3, “Rolling Loads”.
a. CISCA/AF Wheel 1 Rolling Load: 1,250 lbf. (5560 N)
b. CISCA/AF Wheel 2 Rolling Load: 1,000 lbf. (4448 N)
4. Pedestal Axial Load Test: Provide pedestal assemblies, without panels in place, capable of withstanding
a 9,000 lbf (40,034 N) axial load per pedestal, according to CISCA/AF Section 5, “Pedestal Axial Load
Test”, without any permanent deformation.
5. Pedestal Overturning Moment Test: Provide pedestal assemblies, without panels in place, capable of
withstanding an overturning moment of 1,000 inch-pounds (113 NM) per pedestal, according to
CISCA/AF Section 6, “Pedestal Overturning Moment Test”, when glued to a clean, sound, uncoated
concrete surface.
6. Uniform Load Test: Provide access flooring system capable of withstanding a uniform load of 500
lbf/ft2 (23,940 N/M2) placed the over area one panel with a permanent set not to exceed 0.010 inch (0.25
mm) after the load is removed, according to CISCA/AF Section 7, “Uniform Load Test”
Note: The uniform load rating of an access floor panel shall not be confused with the “uniform live
load” as specified for use in seismic calculations for seismic zone applications.
7. Drop Impact Load Test: Provide access flooring system capable of withstanding a drop impact load of
175 lb. (79 kg) dropped from a height of 36 inches (914 mm) without a failure of the system, according
to CISCA/AF Section 8, “Drop Impact Load Test”.
8. Panel Drop Test: Provide access flooring system with panels capable of meeting all structural
performance requirements specified, after the panel is dropped from a height of 36 inches onto a
concrete surface.
B. Seismic Performance: Provide access flooring system capable of withstanding the effects of seismic motions
as calculated for the area of installation according to <insert applicable building code requirement>.
C. ESD-Control Properties:
1. Provide access flooring system with Panel-to-Understructure resistance of not more than 10 ohms as
measured without floor coverings, according to test method as specified in ASTM F 150 with 500-V
applied voltage with one electrode on the top face of the panel and one electrode attached to the tube of
the pedestal.
a. Panel must have a permanently attached positive grounding device (PGD) to assure electrical
continuity between panel and understructure to maintain compliance to required maximum resistance
of 10 ohms.

A. Product Data: For each type of product indicated.
1. Shop Drawings: Include complete layout of access flooring system based of field verified dimensions.
a. Details and sections with descriptive notes indicating materials, finishes, fasteners, typical and
special edge conditions, accessories and understructure.
b. Detail Cut Sheets for each type of product indicated, including accessories, to show the information
necessary to make a full evaluation of the entire flooring system.
c. For installed products indicated to comply with seismic design loads, include calculated structural
analysis data signed by the qualified engineer responsible for their preparation.
2. Samples for Initial Selection: For each type of flooring material indicated and exposed finish indicated,
submit samples in the form of manufacturers color charts consisting of actual units or sections of units
showing full range of colors, textures and patterns
B Product Certificates: For each type of access flooring system indicated, to certify that the flooring system
meets the requirements of these written specifications and signed by a qualified employee of the
C. Product Test Reports: Based on evaluation of comprehensive tests performed by a qualified testing agency,
or performed by access flooring manufacturer and witnessed by a qualified testing agency, for each type of
flooring material and exposed finish.


A. Installer Qualifications: Engage an experienced installer who is approved by the access flooring
manufacturer for installations of the type of access flooring indicated for this project.
B. Source Limitations: Obtain access flooring system through one source from a single manufacturer.
C. Regulatory Requirements: Fabricate and install access flooring system to comply with NFPA 75
requirements for raised flooring.
D. Provide floor panels that are clearly marked with manufacturer’s name and panel type.
E. Mockups (if required): Build mockups to verify selections made under sample submittals and to
demonstrate aesthetic effects and set quality standards for materials and execution.
1. Build mockup of typical access flooring assembly as shown on Drawing. Size to be an area no less than
[three] <Insert number> floor panels in length by [three] <Insert number> floor panels in width.
2. Approved mockups may become part of the completed Work if undisturbed at time of Substantial
G. Pre-installation Conference: Conduct conference at Project site to comply with requirements in Division 01
Section "Project Management and Coordination."
1. Review connection with mechanical and electrical systems.
2. Review and finalize construction schedule and verify availability of materials, Installer's personnel,
equipment, and facilities needed to make progress and avoid delays.


A. Deliver access flooring components in original, unopened packages, clearly labeled with manufacturer’s
name and item description.
B. Handle and store packages containing access flooring in a manner which avoids overloading building


A. Environmental Limitations: Do not install access flooring until installation area is enclosed and has an
ambient temperature of between 50 degrees Fahrenheit and 85 degrees Fahrenheit (10 0 C to 290 C) and a
relative humidity of not less than 20 percent and not more than 80 percent.

A. Coordinate locations of mechanical and electrical work in under-floor cavity to prevent interferences with
access flooring pedestals
B. Pre-mark pedestal locations on a grid of 10’ x 10’ on sub-floor so that mechanical and electrical work can
take place without interfering with pedestals.
C. Do not proceed with installation of access flooring until after substantial completion of other performable
construction within affected spaces.


A. Furnish extra materials described below that match products installed, are packaged with protective
covering for storage and identified with labels clearly describing contents.
1. Standard field panels – 2%
2. Pedestals – 2%



A. Manufacturers: Subject to compliance with requirements, provide access flooring by ASM Modular
Systems, Inc., consisting of FS300 access floor panels supported on a corner-bolted understructure.

B. Floor Panels General: Provide modular panels complying with the following requirements, that are
interchangeable with other standard field panels, and can be easily relocated by one person, using a lifting
device, without disturbing adjacent panels or understructure. Installed panels with floor covering in place
are to be free of exposed metal edges.
1. Nominal Panel Size: 24” x 24” (610 mm x 610 mm) <or 600 mm x 600 mm>
2. Fabrication Tolerances: Fabricate panels to the following tolerances with squareness tolerances
expressed as the difference between diagonal measurements from corner to corner.
a. Size and Squareness: Plus or minus 0.010” (0.12 mm) of required size, with squareness tolerance of
plus or minus 0.015” (0.38 mm).
b. Flatness: Plus or minus 0.020” (0.50 mm), measured on a diagonal on top of the panel.
3. Panel Attachment to Understructure: By Bolting to pedestal head. Provide panels with holes in corners
to align precisely with threaded holes in pedestal heads and to accept countersunk screws with heads
flush with top of panel.
C. Cementitious–Filled, Formed-Steel Panels: Fabricate panels with a die formed all-steel bottom pan
consisting of a minimum 64 embossments, fully welded to a die-cut full-hard steel top sheet to form a
structural unitized construction. Completed panels to be filled with light-weight cementitious fill. Panels
to be cleaned with 3-part wash and rinse system, prior to applying a protective powder-coat epoxy finish.
1. Solid Panels: Flat, solid top surface
2. Perforated Panels: Perforated top surface with holes of number, spacing and size standard with
manufacturer to produce a nominal open area of 25%. [Provide mechanical dampers with each
panel unit]
a. Quantity: [2% of total panels] <Insert number>
b. Finish: Provide perforated panels with manufacturer’s standard finish to match solid panels.
3. Grates: Grating ribs arranged in manufacturer’s standard pattern to produce a nominal open area of
56%. [Provide mechanical dampers with each panel unit]
b. Finish: Provide grate panels with manufacturer’s standard finish.
D. Pedestals: Provide manufactures standard pedestal assembly including base, column with provisions for
height adjustments, and head (Cap), made of steel.
1. Base: Square base plate with not less than 16 square inches (103 sq. mm) of bearing area.
2. Column: Welded to base plate and of height required to bring finished floor to elevations indicated.
3. Provide vibration-proof leveling mechanism for making and holding fine adjustments in height
over a range of not less than 2 inches (50 mm) and for locking at a selected height, so deliberate
action is required to change height setting and prevents vibratory displacement.
4. Construct pedestal adjusting rod of minimum 3/4” (19 mm) diameter solid steel, and vertical
column of minimum 7/8” (22 mm) square steel tubing. All steel components to have
manufacturer’s standard galvanized finish.
5. Head: Pedestal head with four holes aligned with holes in floor panels for bolting of panels to
6. Dual Panel Support: Pedestal head shall be designed to provide a combined support of the panel
edge lip and the bottom corner of the panel.


A. General: Provide bare panels without wear-surface covering.

A. Service Cutouts: Fabricate cutouts in floor panels to accommodate cable penetrations and service outlets.
Comply with requirements indicated for size, shape, number, and location. Provide reinforcement or
additional support, if needed, to make panels with cutouts comply with standard performance requirements.
1. Fit cutouts with manufacturer’s standard grommets in size indicated or, where size of cutouts exceeds
maximum grommet size available, trim edge of cutouts with manufacture's standard plastic molding
having tapered top flange. Furnish removable covers for grommets.
2. Provide foam-rubber pads for sealing annular space formed in cutouts by cables. Trim edge of cutout
with molding having a double-flanged internal edge for containing and supporting foam pads.
B. Vertical Closures (Fascia): Where under floor cavity is not enclosed by abutting walls or other construction,
provide manufacturer’s standard metal closure plates with manufacturer’s standard finish.
C. Ramps: Manufacturer’s standard ramp construction of width and slope indicated, but not steeper than 1 : 12,
with non-slip raised-disc runner or vinyl floor covering, and of same materials, performance, and
construction requirements as the access flooring.
D. Steps: Provide steps of size and arrangement indicated with floor covering to match access flooring. Apply
non-slip aluminum nosing to treads, unless otherwise indicated.
E. Panel Lifting Device: Manufacture's standard portable lifting device of type and number required for lifting
1. Provide the following quantity: [one lifting device per room] <Insert quantity>
F. Perforated Panels: Provide perforated panels as indicated in previous section.
1. Provide the following quantity: [2% of total panels] <Insert quantity>
G. Grate Panels: Provide grate panels as indicated in previous section.


A. Examine sub-floor for any problems that would prevent a satisfactory installation of access
floor, such as moisture an unevenness of top surface. Do not proceed with installation until
sub-floor is clean, dry and level as completed by other trades.
B. Verify field dimensions to contract drawings for size of area of installation, height and level of
recessed slabs, door openings, ledges, etc.
C. Floor Sealers: Verify that any concrete sealer that has been used is compatible with pedestal
D. Access To Installation Area: General Contractor shall provide clear access to installation area
throughout entire duration of installation of access floor that is free of construction debris and
other trades.
E. Storage Of Materials: Area to receive and store access floor materials shall be enclosed and dry.
Storage area shall be maintained at a temperature of not less than 40 0 F and not more than 95 0 F
(4 0 C to 35 0 C), with a relative humidity level between 20% min. to 80% max.
F. Area Of Installation: Shall be maintained throughout entire duration of installation of access
floor at a temperature of 50 0 F min. to 85 0 F max. (10 0 C to 29 0 C) and at 20% min. to 80 %
max. relative humidity.

Prior to installation, all floor panels shall be stored for at least 24 hours in a dry enclosed area at no
less than 40 0 F and no more than 95 0 F (4 0 C to 35 0 C).

A. Install access floor system and accessories under supervision of the access flooring manufactures authorized
representative to ensure rigid, firm installation that complies with performance requirements and is free of
vibration, rocking, rattles and squeaks.
B. Layout floor panel installation to keep the number of cut panels at the floor perimeter to a minimum.
C. Set pedestal in adhesive as recommended by the access flooring manufacturer to provide full bearing of the
pedestal base on the sub floor.
1. Pedestal locations shall be established from approved shop drawings to allow mechanical and electrical
work to be installed without interfering with pedestal installation.
2. Pedestals shall be attached to sub-floor using manufacturer’s approved method.
D. Secure grid member to pedestal heads in accordance with access floor manufacturer’s instructions.
E. Install floor panels securely in place and properly seated with panel edges flush. Do not force panels into
F. Scribe panels at perimeter to provide a close fit with adjoining construction with no voids greater than 1/18”
(3 mm) where panels abut vertical surfaces.
G. Install accessories according Manufacturer’s instructions.
H. Clean up dust, dirt and construction debris caused by floor installation, and vacuum the sub-floor area, as
installation of floor panel proceeds. Extend cleaning under installed panels as far as possible.
I. Level installed access floor to within 0.10” (2.5 mm) over the entire access flooring area and within 0.060”
(1.5 mm) of true level in any 10 ft. (3 M) distance.


A. During installation, all traffic on access floor shall be directed by access floor installer.
1. No traffic, other than access floor installer, shall be allowed on the floor area for 24 hours after
installation to allow the pedestal adhesive to set.
2. No access floor panels shall be removed by other trades for 72 hours after installation.
B. After completing installation, vacuum clean access flooring.
C. Replace any flooring panels that are stained, scratched, or otherwise damaged or that do not comply
with specified requirements.
D. General contractor and/or owner shall provide and maintain suitable protection to prevent damage to
completed access floor throughout entire duration of installation.


All specifications are subject to change without notice or obligation.

Похожие интересы