Conventional voltage regulation equipment works under the assumption that line voltage changes predictably with distance along the feeder. Specifically, feeder voltage drops with increasing distance from the substation due to line impedance and the rate of voltage drop decreases farther away from the substation. However, this assumption may not hold when DG is present. For example, a long feeder with a high concentration of DG at the end will experience significant current injection at points where the voltage is normally lowest. If the load is sufficiently low, current will flow in the reverse direction (i.e. towards the substation), resulting in a voltage profile that increases with distance from the substation. This inverted voltage profile may confuse conventional controls. In one such scenario, load tap changers expecting voltage to decrease with distance from the substation may choose an operating point that in fact causes voltage down the line to exceed operating limits.