Some manufacturers commonly design higher joule-rated surge protectors by connecting multiple MOVs in parallel and this can produce a misleading rating. Since individual MOVs have slightly different voltage thresholds and non-linear responses when exposed to the same voltage curve, any given MOV might be more sensitive than others. This can cause one MOV in a group to conduct more (a phenomenon called current hogging), leading to possible overuse and eventual premature failure of that component. However the other MOVs in the group do help a little as they start to conduct as the voltage continues to rise as it does since a MOV does not have a sharp threshold. It may start to short at 270 volts but not reach full short until 450 or more volts. A second MOV might start at 290 volts and another at 320 volts so they all can help clamp the voltage, and at full current there is a series ballast effect that improves current sharing, but stating the actual joule rating as the sum of all the individual MOVs does not accurately reflect the total clamping ability. The first MOV may bear more of the burden and fail earlier. One MOV manufacturer recommends using fewer but bigger MOVs (e.g.60 mm vs 40 mm diameter) if they can fit in the device and to match them and derate them. In some cases it may take four 40 mm MOVs to be equivalent to one 60 mm MOV.