The HRSG can be designed to burn supplementary fuel after the gas turbine. Supplementary burners are also called "duct burners". Duct burning is possible because the turbine exhaust gas (flue gas) still contains some oxygen. Temperature limits at the gas turbine inlet force the turbine to use excess air, above the optimal stoichiometric ratio to burn the fuel. Often in gas turbine designs part of the compressed air flow bypasses the burner in order to cool the turbine blades. The turbine exhaust is already hot, so a regenerative air preheater is not required as in a conventional steam plant. However, a fresh air fan blowing directly into the duct permits a duct-burning steam plant to operate even when the gas turbine cannot.