"Equipment bonding conductors" or "equipment ground conductors" (EGC) provide a low impedance path between normally non-current-carrying metallic parts of equipment and one of the conductors of that electrical system's source. If any exposed metal part should become energized (fault), such as by a frayed or damaged insulator, it creates a short circuit, causing the overcurrent device (circuit breaker or fuse) to open, clearing (disconnecting) the fault. It is important to note this action occurs regardless of whether there is a connection to the physical ground (earth); the earth itself has no role in this fault-clearing process since current must return to its source; however, the sources are very frequently connected to the physical ground (earth). (see Kirchhoff's circuit laws). By bonding (interconnecting) all exposed non-current carrying metal objects together and to other metallic objects such as pipes or structural steel, they should remain near the same voltage potential, thus reducing the chance of a shock. This is especially important in bathrooms where one may be in contact with several different metallic systems such as supply and drain pipes and appliance frames. When a system needs to be connected to the physical ground (earth), the equipment bonding conductor also becomes the grounding electrode conductor (see above).