Firestops in occupancy separations are also more likely to require an equal fire protection rating (a fire resistance rating for closures). They also must provide a temperature rating ensuring that the components of the firestop systems, including the penetrants are not permitted to rise in temperature above 140°C (284°F) on average or 180°C (356°F) at any single point, to lower the likelihood of auto-ignition on the unexposed side. In this manner, occupancy separations are treated similarly to fire walls which are structurally stable in case of a fire, thus limiting the danger of fire-induced building collapse.