These systems depend on the proper operation of thermostatic air-venting valves located on radiators throughout the heated area. When the system is not in use, these valves are open to the atmosphere, and radiators and pipes contain air. When a heating cycle begins, the boiler produces steam, which expands and displaces the air in the system. The air exits the system through the air-venting valves on the radiators and on the steam pipes themselves. The thermostatic valves close when they become hot; in the most common kind, the vapor pressure of a small amount of alcohol in the valve exerts the force to actuate the valve and prevent steam from leaving the radiator. When the valve cools, air enters the system to replace the condensing steam.