The other type of explosions is the combustible gases explosion. For this to happen the fuel and the air have to be mixed before the ignition. Typical conditions are either a blackout (loss of flame) without purge of furnace or continuous operation in a substoichiometric state. To detect blackout flame monitoring devices are installed, with subsequent interlocked purge and startup. Combustible gas explosions are connected with oil/gas firing in the boiler. As also continuous O2 monitoring is practiced in virtually every boiler the noncombustible gas explosions have become very rare.