The characteristics of this device are attributable to the relationship between the physical size of the unit, in particular the air path distance, and the spacing of the plates. For an equal air pressure drop through the device, a small unit will have a narrower plate spacing and a lower air velocity than a larger unit, but both units may be just as efficient. Because of the cross-flow design of the unit, its physical size will dictate the air path length, and as this increases, heat transfer will increase but pressure drop will also increase, and so plate spacing is increased to reduce pressure drop, but this in turn will reduce heat transfer.