At 9:40 a.m., the plant operators declared a site area emergency (SAE) per existing procedures which called for an SAE whenever "vital" power is lost for more than 15 minutes. At 9:56 a.m., after trying multiple times to start the 1-A EDG normally, plant operators performed an emergency startup of the EDG by activating the generator's emergency start "break-glass" which bypassed most of the EDG's safeties and forced it to start. The startup was successful. RHR-A was then started using power from EDG-A. With core cooling restored, the SAE was downgraded to an alert at 10:15 a.m. At 11:40 a.m., crews energized RAT 1-B which had been shut down for maintenance, restoring power to the "B" safety electrical train. At 12:57 p.m., the "A" safety train was switched from the EDG to RAT 1-B and the EDG was shut down. With both trains receiving offsite power, the alert was terminated at 1:47 p.m.