Current transformer current transformers" are also used (usually with an oscilloscope) to measure waveforms of high frequency or pulsed currents within pulsed power systems. Unlike CTs used for power circuitry, wideband CTs are rated in output volts per ampere of primary current. If the burden resistance is much less than inductive impedance of the secondary winding at the measurement frequency then the current in the secondary tracks the primary current and the transformer provides a current output that is proportional to the measured current. On the other hand, if that condition is not true, then the transformer is inductive and gives a
Electrical wiring in the United Kingdom 1, 1.5, 2.5, 4, 6 and 10 mm. Sizes of 1 or 1.5 mm are typically used for 6 or 10 ampere lighting circuits and 2.5 mm for socket circuits. The earthing conductor is uninsulated since it is not intended to have any voltage difference from surrounding earthed articles. Additionally, if the insulation of a or neutral wire becomes damaged, then the wire is more likely to earth itself on the bare earth conductor and in doing so either trip the RCD or burn the fuse out by drawing too much current. Earthing and Bonding are used together to provide