Fire extinguisher CO types have the test information stamped on the cylinder, all other types get a sticker on the back of the cylinder. Once dry, the units are recharged. Unlike the UK, the US does not rebuild extinguishers and replace valves at specific intervals unless parts are found to be defective, with the exception of halon. Halon types are often given new o-rings and valve stems at every internal maintenance to minimize any leakage potential. OEM equipment must be used for replacement parts for the extinguisher to maintain its UL rating. If parts are unavailable, replacement is recommended, keep in mind
Fire extinguisher extinguisher has passed the 35 kV test it will also bear the same electrical pictogramme – however, any water-based extinguisher is only recommended for inadvertent use on electrical fires. There is no official standard in the United States for the color of fire extinguishers, though they are typically red, except for class D extinguishers which are usually yellow, water and Class K wet chemical extinguishers which are usually silver, and water mist extinguishers which are usually white. Extinguishers are marked with pictograms depicting the types of fires that the extinguisher is approved to fight. In the past, extinguishers were marked