Translocation itself has been shown to be an exergonic reaction (56, 57), but with a high free energy of activation [ÎG â  â 96 kJ/mol for factor-free translocation (58, 59)].
High chilled water temperature: Normally chilled water is delivered into the piping system at a temperature between 42Â°F and 46Â°F. This is the water temperature that should be present at the supply connection on the air handler. Some buildings vary the temperature of chilled water with outdoor temperature change.
Sentinel taps. The water temperature should be below 20Â°C after running the water for up to 2 minutes. The water temperature should be at least 50Â°C within one minute of running the water. This check makes sure that the supply and return temperatures on each loop are unchanged i.e. the loop is functioning as required.