idc comptia pinouts faceplates 8p8c n10 connectors insulation wiring terminations dulaney crosstalk lsa topology closets cabling krone displacing cram jumper keystone sockets terminate telephony cables 6a screw unusable harwood whence
what is the difference between a 66 block and a 110 block
110 block - wikipedia 110 block This article needs additional citations for verification . Please help improve this article by adding citations to reliable sources . Unsourced material may be challenged and removed . ( September 2014 ) ( Learn how and when to remove this template message ) A 110 punch block . A 110 block is a type of punch block used to terminate runs of on - premises wiring in a structured cabling system . The designation 110 is also used to describe a type of insulation displacement contact ( IDC ) connector used to terminate twisted pair cables , which uses a punch - down tool similar to the older 66 block . Contents 1 Usage 1.1 Telephone distribution 1.2 Computer networks 2 Advantages 3 Problems 4 See also 5 References Usage ( edit ) Telephone distribution ( edit ) Early residential telephone systems used simple screw terminals to join cables to sockets in a tree topology . These screw - terminal blocks have been slowly replaced by 110 blocks and connectors . Modern homes usually have phone service entering the house to a single 110 block , whence it is distributed by on - premises wiring to outlet boxes throughout the home in star topology . At the outlet box , cables are punched down IDC type connectors , which fit in special faceplates . In commercial settings , this style of home run or star topology wiring was already in use on 66 blocks in telecom closets and switchrooms . The 110 block has been slowly replacing the 66 block , especially for data communications usage . Computer networks ( edit ) The 110 style IDC connection is often used at both ends of Category 5 cable runs through buildings , as shown in the image . In switch rooms , 110 blocks are often built into the back of patch panels to terminate cable runs . At the other end , 110 connections may be used with keystone modules that are attached to wall plates . 110 blocks are preferred over 66 blocks in high - speed networks because they introduce less crosstalk and many are certified for use in Category 5 , Category 6 and Category 6a wiring systems . Individual cat5e and better rated 8P8C jacks ( keystone and patch panel ) with IDC connectors commonly use the same punchdown ' teeth ' dimensions and tools as a full size 110 block . Advantages ( edit ) 110 style blocks allow a much higher density of terminations in a given space than older style termination blocks ( 66 style or wire wrap ) . Some 110 blocks meet specifications for higher bandwidth data protocols such as Category 5 and higher . Problems ( edit ) During regular usage , small pieces of insulation can become stuck inside the 110 block contacts ; this renders that given pair unreliable or unusable , until the pieces are removed . A tool known as a spudger can be used to remove excess insulation pieces . The wire hook which comes on many punch down tools can also be used to remove wire pieces . A new wire inserted over an existing insulation remnant may be unreliable , as the 110 IDC was designed to hold only a single wire per contact . For testing it is more difficult to reliably connect to a working circuit on a 110 block than on older style blocks . The circuit must be broken , or insulation displacing contacts may be used on jumper wires . Repeated use of insulation displacing contacts may lead to a difficult to locate broken or intermittent jumper wire . See also ( edit ) 66 block Telecommunications Industry Association Electronic Industries Alliance Electrical wiring Krone LSA - PLUS References ( edit ) Jump up ^ Termination Diagram http://www.cabling-design.com/references/pinouts/110-block-4-pair.shtml Jump up ^ Dulaney & Harwood . CompTIA Network+ N10 - 005 Exam Cram . p. 236 . Retrieved from `` https://en.wikipedia.org/w/index.php?title=110_block&oldid=750728007 '' Categories : Telephony equipment Local loop Networking hardware Hidden categories : Articles needing additional references from September 2014 All articles needing additional references All articles with unsourced statements Articles with unsourced statements from February 2015 Talk Contents About Wikipedia Add links This page was last edited on 21 November 2016 , at 14 : 06 ( UTC ) . Text is available under the Creative Commons Attribution - ShareAlike License ; additional terms may apply . By using this site , you agree to the Terms of Use and Privacy Policy . Wikipedia ® is a registered trademark of the Wikimedia Foundation , Inc. , a non-profit organization . About Wikipedia