{"action":"closed","issue":{"url":"https://api.github.com/repos/msimerson/330-NE-193rd-St/issues/15","repository_url":"https://api.github.com/repos/msimerson/330-NE-193rd-St","labels_url":"https://api.github.com/repos/msimerson/330-NE-193rd-St/issues/15/labels{/name}","comments_url":"https://api.github.com/repos/msimerson/330-NE-193rd-St/issues/15/comments","events_url":"https://api.github.com/repos/msimerson/330-NE-193rd-St/issues/15/events","html_url":"https://github.com/msimerson/330-NE-193rd-St/issues/15","id":144736007,"number":15,"title":"electrical system upgrades & capacity planning","user":{"login":"msimerson","id":261635,"avatar_url":"https://avatars.githubusercontent.com/u/261635?v=3","gravatar_id":"","url":"https://api.github.com/users/msimerson","html_url":"https://github.com/msimerson","followers_url":"https://api.github.com/users/msimerson/followers","following_url":"https://api.github.com/users/msimerson/following{/other_user}","gists_url":"https://api.github.com/users/msimerson/gists{/gist_id}","starred_url":"https://api.github.com/users/msimerson/starred{/owner}{/repo}","subscriptions_url":"https://api.github.com/users/msimerson/subscriptions","organizations_url":"https://api.github.com/users/msimerson/orgs","repos_url":"https://api.github.com/users/msimerson/repos","events_url":"https://api.github.com/users/msimerson/events{/privacy}","received_events_url":"https://api.github.com/users/msimerson/received_events","type":"User","site_admin":false},"labels":[{"url":"https://api.github.com/repos/msimerson/330-NE-193rd-St/labels/Building","name":"Building","color":"fbca04"},{"url":"https://api.github.com/repos/msimerson/330-NE-193rd-St/labels/electrical","name":"electrical","color":"fef2c0"}],"state":"closed","locked":false,"assignee":{"login":"msimerson","id":261635,"avatar_url":"https://avatars.githubusercontent.com/u/261635?v=3","gravatar_id":"","url":"https://api.github.com/users/msimerson","html_url":"https://github.com/msimerson","followers_url":"https://api.github.com/users/msimerson/followers","following_url":"https://api.github.com/users/msimerson/following{/other_user}","gists_url":"https://api.github.com/users/msimerson/gists{/gist_id}","starred_url":"https://api.github.com/users/msimerson/starred{/owner}{/repo}","subscriptions_url":"https://api.github.com/users/msimerson/subscriptions","organizations_url":"https://api.github.com/users/msimerson/orgs","repos_url":"https://api.github.com/users/msimerson/repos","events_url":"https://api.github.com/users/msimerson/events{/privacy}","received_events_url":"https://api.github.com/users/msimerson/received_events","type":"User","site_admin":false},"assignees":[{"login":"msimerson","id":261635,"avatar_url":"https://avatars.githubusercontent.com/u/261635?v=3","gravatar_id":"","url":"https://api.github.com/users/msimerson","html_url":"https://github.com/msimerson","followers_url":"https://api.github.com/users/msimerson/followers","following_url":"https://api.github.com/users/msimerson/following{/other_user}","gists_url":"https://api.github.com/users/msimerson/gists{/gist_id}","starred_url":"https://api.github.com/users/msimerson/starred{/owner}{/repo}","subscriptions_url":"https://api.github.com/users/msimerson/subscriptions","organizations_url":"https://api.github.com/users/msimerson/orgs","repos_url":"https://api.github.com/users/msimerson/repos","events_url":"https://api.github.com/users/msimerson/events{/privacy}","received_events_url":"https://api.github.com/users/msimerson/received_events","type":"User","site_admin":false}],"milestone":null,"comments":2,"created_at":"2016-03-30T22:15:23Z","updated_at":"2016-08-20T19:30:13Z","closed_at":"2016-08-20T19:30:13Z","body":"### present electrical system\r\n\r\n* SFR built in 1952. Addition & garage added in 197_.\r\n* 200 amp main service panel located in front of house.\r\n    * Upgraded to 200 amp with 1970s addition\r\n    * 12 open breaker slots\r\n* 100 amp subpanel in the garage, on the wall adjoining the house\r\n    * ~65' from service panel\r\n    * 7 open breakers\r\n    * 2? gage braided aluminum wire in plastic conduit.\r\n* 125 amp subpanel in the crawl space #48\r\n    * 4 tandem breakers (4x 15a, 4x 20a)\r\n    * 4 open breaker slots\r\n* Branch circuits are copper. Both feeders are braided aluminum. Yes, they have antioxidant paste.\r\n\r\n### near term electrical forecast\r\n\r\n* [x] get [permit](http://www.lni.wa.gov/TradesLicensing/Electrical/FeePermInsp/PermitInspect/GetPermit.asp) (expires May 10, 2017)\r\n* [ ] request inspection within 3 days of completion or 1 day after energized\r\n* [x] microwave (12 gage wire, 15A breaker, issue #38)\r\n* [x] solar panels (40A breaker) #13\r\n    * [x] inspection\r\n* [x] car charger in garage #51\r\n* [x] heat pump water heater (20A circuit?)\r\n* [ ] two mini split heat pumps\r\n    * two 220V 15A runs to [main / crawl /  garage] panel\r\n    * dependent on outdoor unit siting\r\n* [x] remove unused hot tub wiring #50\r\n* [x] fridge circuit\r\n* [x] dishwasher circuit\r\n\r\n### anticipated future changes\r\n\r\n* car charger 2 in garage (40A)\r\n* attic rooms, light circuit (15A)\r\n* attic rooms, outlets (20A)\r\n\r\n### anticipated peak garage loads\r\n\r\n* 32A car charger (usually evenings)\r\n* 30A car charger (random usage)\r\n* 40A solar panels (generating during daylight)\r\n\r\n### anticipated peak main panel loads\r\n\r\n* 15 amp heat pump water heater\r\n* 30 amp - (2) mini-split heat pumps in mid-winter\r\n* 30 amp - oven\r\n* 30 amp - clothes dryer\r\n* 100 amp - garage\r\n\r\n### misc todo\r\n\r\n* [x] #49 grounding wire not attached to water main\r\n* [x] loose ground strap near water heater"}}
{"actor":{"display_login":"msimerson"}}