{"action":"created","issue":{"url":"https://api.github.com/repos/NREL/OpenStudio/issues/2043","labels_url":"https://api.github.com/repos/NREL/OpenStudio/issues/2043/labels{/name}","comments_url":"https://api.github.com/repos/NREL/OpenStudio/issues/2043/comments","events_url":"https://api.github.com/repos/NREL/OpenStudio/issues/2043/events","html_url":"https://github.com/NREL/OpenStudio/issues/2043","id":128424142,"number":2043,"title":"CoilHeatingWaterToAirHeatPump:EquationFit forward translator sets hard sized rated water flow rate as air flow rate","user":{"login":"eringold","id":10799524,"avatar_url":"https://avatars.githubusercontent.com/u/10799524?v=3","gravatar_id":"","url":"https://api.github.com/users/eringold","html_url":"https://github.com/eringold","followers_url":"https://api.github.com/users/eringold/followers","following_url":"https://api.github.com/users/eringold/following{/other_user}","gists_url":"https://api.github.com/users/eringold/gists{/gist_id}","starred_url":"https://api.github.com/users/eringold/starred{/owner}{/repo}","subscriptions_url":"https://api.github.com/users/eringold/subscriptions","organizations_url":"https://api.github.com/users/eringold/orgs","repos_url":"https://api.github.com/users/eringold/repos","events_url":"https://api.github.com/users/eringold/events{/privacy}","received_events_url":"https://api.github.com/users/eringold/received_events","type":"User","site_admin":false},"labels":[],"state":"open","locked":false,"assignee":null,"milestone":null,"comments":1,"created_at":"2016-01-24T20:49:20Z","updated_at":"2016-01-25T15:28:45Z","closed_at":null,"body":"Found this in v1.10.0, Windows x64. Looks like this is happening [here](https://github.com/NREL/OpenStudio/blob/a477c2f00aa05e37813d0aedab3ddbaf8d2881be/openstudiocore/src/energyplus/ForwardTranslator/ForwardTranslateCoilHeatingWaterToAirHeatPumpEquationFit.cpp#L112). This hurts the simulation. \r\n\r\n@kbenne @macumber "},"comment":{"url":"https://api.github.com/repos/NREL/OpenStudio/issues/comments/174543684","html_url":"https://github.com/NREL/OpenStudio/issues/2043#issuecomment-174543684","issue_url":"https://api.github.com/repos/NREL/OpenStudio/issues/2043","id":174543684,"user":{"login":"eringold","id":10799524,"avatar_url":"https://avatars.githubusercontent.com/u/10799524?v=3","gravatar_id":"","url":"https://api.github.com/users/eringold","html_url":"https://github.com/eringold","followers_url":"https://api.github.com/users/eringold/followers","following_url":"https://api.github.com/users/eringold/following{/other_user}","gists_url":"https://api.github.com/users/eringold/gists{/gist_id}","starred_url":"https://api.github.com/users/eringold/starred{/owner}{/repo}","subscriptions_url":"https://api.github.com/users/eringold/subscriptions","organizations_url":"https://api.github.com/users/eringold/orgs","repos_url":"https://api.github.com/users/eringold/repos","events_url":"https://api.github.com/users/eringold/events{/privacy}","received_events_url":"https://api.github.com/users/eringold/received_events","type":"User","site_admin":false},"created_at":"2016-01-25T15:28:45Z","updated_at":"2016-01-25T15:28:45Z","body":"Example: here's an object from 'out.osm' in /run/1-UserScript-0: \r\n\r\n    OS:Coil:Heating:WaterToAirHeatPump:EquationFit,\r\n    {53fa062d-bfb4-4d0f-9441-9ca44d591cf6}, !- Handle\r\n    Coil Heating Water To Air Heat Pump Equation Fit 46, !- Name\r\n    {775c9dfc-c8d6-4014-aeec-758f001ef3f5}, !- Water Inlet Node Name\r\n    {546283ca-4da4-41ef-97a7-f2016828badf}, !- Water Outlet Node Name\r\n    ,                                       !- Air Inlet Node Name\r\n    ,                                       !- Air Outlet Node Name\r\n    0.757475646336,                         !- Rated Air Flow Rate {m3/s}\r\n    0.00102018189948096,                    !- Rated Water Flow Rate {m3/s}\r\n    15591.3809331622,                       !- Rated Heating Capacity {W}\r\n    4.1,                                    !- Rated Heating Coefficient of Performance {W/W}\r\n    -1.361311959,                           !- Heating Capacity Coefficient 1\r\n    -2.471798046,                           !- Heating Capacity Coefficient 2\r\n    4.173164514,                            !- Heating Capacity Coefficient 3\r\n    0.640757401,                            !- Heating Capacity Coefficient 4\r\n    0,                                      !- Heating Capacity Coefficient 5\r\n    -2.176941116,                           !- Heating Power Consumption Coefficient 1\r\n    0.832114286,                            !- Heating Power Consumption Coefficient 2\r\n    1.570743399,                            !- Heating Power Consumption Coefficient 3\r\n    0.690793651,                            !- Heating Power Consumption Coefficient 4\r\n    0;                                      !- Heating Power Consumption Coefficient 5\r\n\r\nAnd the same object from 'in.idf' in /run/2-ModelToIdf-0: \r\n\r\n    Coil:Heating:WaterToAirHeatPump:EquationFit,\r\n    Coil Heating Water To Air Heat Pump Equation Fit 46, !- Name\r\n    Node 455,                               !- Water Inlet Node Name\r\n    Node 456,                               !- Water Outlet Node Name\r\n    HP-15 Cooling Coil Outlet Node,         !- Air Inlet Node Name\r\n    HP-15 Heating Coil Outlet Node,         !- Air Outlet Node Name\r\n    0.757475646336,                         !- Rated Air Flow Rate {m3/s}\r\n    0.757475646336,                         !- Rated Water Flow Rate {m3/s}\r\n    15591.3809331622,                       !- Gross Rated Heating Capacity {W}\r\n    4.1,                                    !- Gross Rated Heating COP\r\n    -1.361311959,                           !- Heating Capacity Coefficient 1\r\n    -2.471798046,                           !- Heating Capacity Coefficient 2\r\n    4.173164514,                            !- Heating Capacity Coefficient 3\r\n    0.640757401,                            !- Heating Capacity Coefficient 4\r\n    0,                                      !- Heating Capacity Coefficient 5\r\n    -2.176941116,                           !- Heating Power Consumption Coefficient 1\r\n    0.832114286,                            !- Heating Power Consumption Coefficient 2\r\n    1.570743399,                            !- Heating Power Consumption Coefficient 3\r\n    0.690793651,                            !- Heating Power Consumption Coefficient 4\r\n    0;                                      !- Heating Power Consumption Coefficient 5"}}