B1 = 600 mm, H1 = 300 mm, n = 12 Q = 1450 m³/h Aef = 600 x (300 -21-(7 x 12)) = 117000 mm² ≥ 0.117 m² v = (Q / 3600) / Aef = (1450 / 3600) / 0.117 = 3.44 m/s Δpcel from diagram Suply 36 Pa Outlet 28 Pa
B1 = 600 mm, H1 = 300 mm, n = 12 Q = 1450 m³/h Aef = 600 x (300 -21-(7 x 12)) = 117000 mm² ≥ 0,117 m² v = (Q / 3600) / Aef = (1450 / 3600) / 0,117 = 3,44 m/s Δpcel iz diagrama dovod 36 Pa odvod 28 Pa