the present invention relates to the construction and manufacture of an entirely new and unique method of assembly of a liquid flow meter . the meter is economically and simply constructed , has but one moving part as the measuring assembly , uses no external power source , operates entirely through the use of gravity , is capable of passing 3 inch spherical solids , suspended solids , oils , greases , waxes and is therefore useful in measuring wastewater flow . it provides an economical and cost effective means of measuring wastewater flow from every wastewater connection to a sewer collection system and meets the design standards for minimal opening sizes . this ability to measure allows the customer to be invoiced for the measured flow , thus addressing the customer &# 39 ; s claims with respect to overbilling , and conversely allows the system operator to invoice for all flows including infiltration and inflow . customers receiving invoices for more wastewater than water supplied will have a direct motivation to repair or replace defective service piping on their private property . replacement of defective service piping will allow the wastewater collection and treatment systems to operate more efficiently and effectively , and help eliminate system operational problems and violations caused by large flow variations . alternatively , wastewater collection and treatment system operators will be in a position to receive income directly proportional to the wastewater quantity produced by each customer &# 39 ; s connection to their sewer collection system . the present invention is scalable , therefore allowing different meter sizes for differing flow quantities . larger meters would be particularly useful in the study toward elimination of infiltration and inflow in wastewater collection systems . historically , run time meters at pump stations have been used to estimate the flows by applying the run time to the average pumping capacity , for lack of a more accurate flow measurement method . such studies invariably require data adjustment due to relay failures , check valve failures , pump failures and other causes . steady state flow from any pump differs from priming ( or startup ) flow , causing such measurement methods to be best estimates of actual flows . a reliable , accurate and cost effective means of measuring the flow of liquids containing mixtures of solids , oils , greases and waxes is therefore highly desirable and fulfills a currently unmet commercial need . the present invention is intended by applicants to meet this identified need and will be commercially desirable for other commercial and industrial applications requiring measurement of such fluid mixtures . the meter design is “ fail safe ” in that if the meter fails to function as designed , a clear opening is provided to allow the passage of all flow including a 3 inch diameter spherical solid . referring to the accompanying drawings , the liquid flow meter ( 10 ) is housed in a compartment enclosure , the shape of which is not important to the function of the flow meter ( fig1 ), but the shape of the outer enclosure is important to the hydraulic head at which the meter will function , with wider enclosures allowing lower hydraulic head losses through the flow metering assembly . the compartment enclosure is formed of an upper part assembly ( 12 ) and a lower case assembly ( 13 ). the preferred outer enclosure is provided with three ports : a first port or influent inlet port ( 14 ) which receives the incoming fluid stream and is fitted with a female coupling connection for pipe flow to be metered . a second port ( 17 ) which provides the discharge stream of the fluid measured and is fitted with a female coupling connection to liquid outlet piping . a third port ( 11 ) provides a connection for field flushing the meter assembly with water . the inlet port ( 14 ) is located over the centerline of the pivot ( 29 ) for the volumetric container as shown in fig5 for the purpose of counteracting and distributing the momentum force caused by the inertia of the incoming flow . effluent outlet port ( 17 ) is located with the invert , or lower point port , coincident with the invert of the outer enclosure at the lower end of the lower case assembly ( 13 ). flushing port ( 11 ) is located coincident with the invert of the enclosure at the higher end of the lower outer enclosure as shown in fig1 . other elements shown in the drawings are a meter bypass module 15 , horizontal structural reinforcing rib 16 , upper and lower case flanges 20 , an outlet flume 21 , a pivot block 28 , a pivot bearing 30 , a slot and set screw 31 , and a counterbalance weight 32 . in the preferred embodiment , a sealed cycle counter housing ( 18 ) is molded into the exterior of the upper case assembly ( 12 ) for the purpose of housing the cycle counter assembly ( 22 ), the cycle counter assembly being any suitable commercially available type . see fig2 . the cycle counter housing ( 18 ) is molded with the upper case assembly ( 12 ) of the meter enclosure on one end and has a clear lens ( 19 ) sealed to the cycle counter housing ( 18 ) on the opposing end as shown in fig1 . the purpose of the clear lens is to allow viewing of the cycle counter register . mounted within the cycle counter housing ( 18 ) is the cycle counter assembly formed of the cycle counter ( 22 ), cycle counter arm ( 23 ), permanent magnet ( 24 ), magnet guide ( 25 ) and meter counter housing internal radii ( 26 ). actuation of the cycle counter assembly is through the upper outer enclosure of the liquid flow meter by the use of permanent magnet ( 24 ) suspended from the cycle counter arm ( 23 ) and attached thereto , which are moved through proximity to other magnets or ferrous material mounted for the purpose on or within the enclosed pivoting volumetric container positioned within the compartment enclosure . the purpose of sealing the cycle counter assembly is to prevent water , moisture and sewer gasses from contacting the cycle counter assembly , thereby reducing the effects of corrosion upon the cycle counter assembly and allowing the lens to remain clear for ease of reading the cycle counter . within the said flow meter enclosure , and located in the lower case assembly , is a pivoting volumetric measuring bucket assembly or container ( 27 ) ( see fig4 and 5 ). the bucket assembly is proportioned to contain a specific volume and proportioned to have a long side and a short side relative to the horizontal axis about which it rotates . the short side of the bucket has the counterweight so that it is counterweighted to create a moment about the pivot axis ( 29 ) in excess of the moment about the horizontal pivot axis of the bucket caused by the long leg of the bucket and the fluid it contains until the specific volume is reached , were upon , the moment created by the weight of the volume of the fluid and the longer leg of the bucket overcomes the moment caused by the bucket counterweight , and the pivoting measuring bucket begins to rotate . as the pivoting measuring bucket begins to rotate , the center of gravity of the fluid and the suspended matter within the fluid within the bucket transfers away from the pivot , increasing the moment imbalance , and causing the bucket to be accelerated downward , causing the bucket to rapidly dump its specific volume contents including any solids , oils , grease or suspended matter into the lower case assembly in the direction of the effluent outlet port ( 17 ). the dumping cycle motion of the bucket is sensed through the meter enclosure through the use of permanent magnets and ferrous materials and registered by a mechanical tallying counter as commonly commercially available . the counterbalance weight of the short leg of the bucket returns the emptied bucket to the unfilled position , allowing the cycle to be repeated . the preferred material for construction of the enclosure and the bucket is polyvinyl chloride plastic , a material widely used for the conveyance of wastewater and desirable due to its low surface tension properties and its resistance to corrosion in wastewater environments . other synthetic plastic materials may be used to achieve similar results as will be apparent to those skilled in the art . installation of the meter assembly in the gravity flow conduit requires that it be set to the grade , level across the axis of the pivot assembly , and longitudinally level to insure the meter enclosure fully drains with a velocity sufficient to transport suspended matter . typically the longitudinal grade of the bottom of the lower enclosure will be sufficient to cause a minimum liquid flow velocity greater than 2 feet per second within said lower enclosure . when installed in a typical sewer service lateral , between for example , a residence and a gravity sewer collection system , the entire assembly will be installed below the ground surface with only the registering tallying cycle counter and the flushing attachment fitting accessible from the surface , and protected from normal surface traffic damage by a state of the art meter box with lid . it is envisioned the registering tallying cycle counter will be read monthly as is common in the industry for the reading of similar registers for water metering services . the strength of the enclosure assembly and appurtenances shall be sufficient to withstand the soil and traffic overburdens . the cycle counter enclosure may be produced in varying lengths to accommodate varying depths of burial . the flushing port will be field extendable during installation to allow ease of surface access . further modification and variations will be apparent to those skilled in the art from the foregoing and are intended to be encompassed by the claims appended hereto .