{"content":[{"text":"Procurement Department Bid Section \n Customer Center 1st Floor, Room 002 \n 21 W. Church Street \n Jacksonville, Florida 32202","bbox":{"left":0.369231,"top":0.115643,"width":0.2468070000000001,"height":0.06231600000000001}},{"text":"June 9, 2021","bbox":{"left":0.843431,"top":0.175707,"width":0.08308899999999997,"height":0.016877000000000003}},{"text":"ADDENDUM NUMBER: Four (4)","bbox":{"left":0.058824,"top":0.190239,"width":0.23741800000000002,"height":0.017635000000000012}},{"text":"TITLE: IFB 1410326449 Cedar Bay Water Reclamation Facility Backup Power System","bbox":{"left":0.058824,"top":0.219936,"width":0.580983,"height":0.017635000000000012}},{"text":"BID DUE DATE: June 15, 2021","bbox":{"left":0.058824,"top":0.249633,"width":0.21790200000000004,"height":0.017635000000000012}},{"text":"TIME OF RECEIPT: 12:00 PM EST","bbox":{"left":0.058824,"top":0.279254,"width":0.25472000000000006,"height":0.017635999999999985}},{"text":"THIS ADDENDUM IS FOR THE PURPOSE OF MAKING THE FOLLOWING CHANGES OR \n CLARIFICATIONS: \n 1. Question: New M-T-M breakers for MCC-100 are 4 pole to eliminate the need for Modified Differential Ground Fault. \n Should the neutral in the Gen SWBD also be switched? Drawings show utility incoming and gen-2 coming into the same \n new section of MCC-100, this cannot be done in one section.","bbox":{"left":0.088235,"top":0.309216,"width":0.8204940000000001,"height":0.082235}},{"text":"Answer: The existing Main-Tie-Main breakers of MCC-100 are 3 poles and the new replacement breakers shall be 3 poles \n as well. The same happens with the Gen SWBD breaker, it shall be 3 poles (No switching of neutral). Refer to answer in \n Addendum 3. With regards to the connection of the generator feeder to the MCC-100, it shall be connected in the section \n shown on the drawings. This was discussed with Schneider during the design phase because they were the manufacturers \n of the MCC-100.","bbox":{"left":0.117608,"top":0.403596,"width":0.808226,"height":0.07499899999999998}},{"text":"ACKNOWLEDGE RECEIPT OF THIS ADDENDUM ON THE BID FORM","bbox":{"left":0.238994,"top":0.520104,"width":0.5366399999999999,"height":0.017522000000000038}},{"text":"Page 1 of 1","bbox":{"left":0.852549,"top":0.918951,"width":0.07398700000000002,"height":0.017636000000000096}}],"images_bbox":[],"images_bbox_not_text_overlap":[]}