{"content":[{"text":"Generator Inspection Checklist \n By Generator Help Online","bbox":{"left":0.346944,"top":0.088942,"width":0.30635700000000005,"height":0.05652200000000002}},{"text":"I have been servicing generators for over 40 years. The Generator Inspection \n Checklist I have created comes from customers who have been tagged for these \n same items as well as conversations I have had with fire marshals, health \n department officials, insurance adjusters, and Medicare/Medicaid staff. \n Is your paperwork ready? \n (Most paperwork should go back 2 years. The 4-hour load tests required \n every 3 years should have records going back past 2 tests, or 6 years.) \n Click on the links for more information.","bbox":{"left":0.117686,"top":0.184843,"width":0.7549750000000001,"height":0.20568599999999995}},{"text":"o","bbox":{"left":0.205915,"top":0.428184,"width":0.013767000000000001,"height":0.02008199999999999}},{"text":"You should have an appropriate maintenance log. You can download \n my Inspection & Testing Log at: Download. It comes with written \n instructions. \n ▪ I also have posted the Kansas log. Download I made a video on \n how to fill this one out at: Emergency Generator Operating \n Log \n • Your state may have a log they prefer. The state logs are \n all similar. \n ▪ Your log needs to include the inspections and tests that I have \n noted. I made videos about how to conduct these procedures. \n Go to the Weekly and Monthly videos. Pay particular attention \n to the 30-minute monthly load test. Keep these records for at \n least 2 years. \n Gather any maintenance records and invoices you have collected from \n outside vendors. Keep your invoices as proof of maintenance and \n repairs for 2 years. \n ▪ Make sure your vendor completes the Required 30-minute \n Load Test Following Every Maintenance or Repair \n Procedure. \n Make sure you have record of your required 4-hour test that must be \n conducted every three years. See my video on How to Conduct a 4- \n Hour Load Test. I also provide here a 4-hour Load Test Form.","bbox":{"left":0.235327,"top":0.424275,"width":0.644055,"height":0.48677}},{"text":"o","bbox":{"left":0.205915,"top":0.714762,"width":0.013767000000000001,"height":0.020082000000000044}},{"text":"o","bbox":{"left":0.205915,"top":0.846302,"width":0.013767000000000001,"height":0.020082000000000044}}],"images_bbox":[],"images_bbox_not_text_overlap":[]}