{"content":[{"text":"g","bbox":{"left":0.117647,"top":0.059211,"width":0.033056,"height":0.037926}},{"text":"GE Consumer & Industrial \n Large Power Transformers \n 1140 W. INDUSTRIAL PARK DR. \n Nogales, AZ 85621","bbox":{"left":0.677745,"top":0.080857,"width":0.22317399999999998,"height":0.06830400000000002}},{"text":"GE MODEL #: \n 9T73C9876","bbox":{"left":0.177745,"top":0.183054,"width":0.10624900000000004,"height":0.034466}},{"text":"Underwriters' Laboratories Inc Listed","bbox":{"left":0.495098,"top":0.19996,"width":0.2655199999999999,"height":0.01738300000000001}},{"text":"RATING: \n CU 3PH 60HZ 150KVA 480 +2, -4(2.3% TAPS) 208Y/120 CLS-3","bbox":{"left":0.177745,"top":0.23419,"width":0.46818,"height":0.03428999999999999}},{"text":"Frame = ST376 \n Temp. Rise (C) = 150 Insulation System = 220C \n AVG. Sound Level (dB) = 50","bbox":{"left":0.308725,"top":0.285188,"width":0.43180799999999997,"height":0.05147299999999999}},{"text":"LOSS DATA @ 100% LOAD: \n Core Loss or No Load Loss @ 100% voltage (Watts) = \n Impedance Loss or Coil Loss @ Rise + 20C reference (Watts) = \n Total Loss @ Rise + 20C reference (Watts) =","bbox":{"left":0.177745,"top":0.353508,"width":0.49761099999999997,"height":0.06838099999999997}},{"text":"203.0 \n 3,882.0 \n 4,085.0","bbox":{"left":0.85598,"top":0.370415,"width":0.05468700000000004,"height":0.051473999999999964}},{"text":"DIELECTRIC AND PRODUCTION TESTING: \n Induce Test @ Twice rated voltage 400 Hz per UL1561 and NEMA ST-20 \n Hipot Test for High Voltage winding to Low Voltage and Ground @ 4000 volts 60 Hz 60 Sec. \n Hipot Test for Low Voltage winding to High Voltage and Ground @ 2500 volts 60 Hz 60 Sec. \n Polarity additive in accordance with UL1561 and NEMA ST-20","bbox":{"left":0.177745,"top":0.438736,"width":0.666809,"height":0.08542499999999997}},{"text":"EFFICIENCY: \n Efficiencies at reference temperature of Rise + 20C (Calculated). \n Load (%) Efficiency (%) \n 25 98.9 \n 35 98.9 \n 50 98.7 \n 75 98.3 \n 100 97.8","bbox":{"left":0.177745,"top":0.541008,"width":0.46814700000000004,"height":0.136563}},{"text":"IMPEDANCE: \n Impedance at reference temperature of Rise + 20C (Calculated). \n %R = 3.0 \n %X = 4.4 \n %Z = 5.4","bbox":{"left":0.177745,"top":0.694417,"width":0.466358,"height":0.08542600000000011}},{"text":"REGULATION: \n Regulation at reference temperature of Rise + 20C (Calculated). \n PF Regulation (%) \n 1.0 3.0 \n 0.8 4.8","bbox":{"left":0.177745,"top":0.79669,"width":0.463641,"height":0.085426}}],"images_bbox":[],"images_bbox_not_text_overlap":[]}