FinaL Draft 
  
 
   
متطلبات بطاقات الطاقة والحدود الدنيا لكفاءة استهلاك الطاقة 
 لمكيفات الهواء  
ENERGY LABELLING AND MINIMUM ENERGY 
PERFORMANCE REQUIREMENTS  
 FOR AIR -CONDITIONERS  
 
QS 2663 :2020    
 
  23.120  ICS:         
   
   
   
النسخة الإنجليزية                                                         English Version  
 
 
FinaL Draft 
1 
  
تـقديـم 
الهيئةة الاةة ة الريةية للاصااةةةةةةةةةةةةةةةةةط يالمرييه ميئةة يانيةة  ي  هةة هةة موااف ي  ةا   ي  ن  الاصااةةةةةةةةةةةةةةةةةط 
الريةسية ياللصائح الةنية الريةية بصاسية لجةن فنية يانية  مخصصة للاصااةةط يالارة يه. 
يقةا قةة ةل الهيئةة مةةوماةةف ال ئ ةة الةنيةة الريةيةة قق  (QS 2663:2020 )  يذلةبم ةا ة  ال ئ ةة  الةنيةة 
قق  QS SASO  2663: 2015) )  " ميل ةةط ميةةقةةط اليةةقةة يال ةايف الةانيةة لتةةة ا اسةةةةةةةةةةةةةةمه   اليةةقةة
لاكيةةط الهصا " مةللغة الانجليزية،  يالم     فقاسةةةةةةةةمهة ي  ا  هة  ضةةةةةةةةاي بةنة   وا  (اللجنة  الةنية  الصانية 
الامخصصة للاصااةةط التهةبةئية يالإلتمةينية) قق  TC05. 
يقا اومااطمذه ال ئ ة الةنية ك ئ ة فنية   قيةية مرةاق  سةةةةةةةةاةفا ي ية  المجةقا يالصةةةةةةةةنةوة   قق  (1) لسةةةةةةةةنة 
2021 مبمةقيخ 29/05/1442 مة،الاصافق 13/01/2021 م  
 ولى أن  لغ  ي        ال ئ ة الةنية الريةية (2663:2015 QS SASO). 
 
Foreword  
Qatar General Organization for standardization (QS) is the national authority 
entrusted with the preparation, updating, and adoption Qatari Standards and 
Technical regulations through specialized national technical committees (TCs).  
QS has approved   Techn ical Regulation (QS 2663 :2020 ) "Energy Labelling 
And Minimum Energy Performance Requirements  For Air-Conditioners " 
through updating (QS SASO  2663: 2015 ) "Energy Labelling And Minimum 
Energy Performance Requirements For Air -Conditioners " in English , studied 
and updated  within the work program of the Specialized National  Technical  
Committee for Electrical and Electronic Standards No. TC0 5.  
This technical regulation  has been approved as a Technical Regulation by HE the 
Minister of Commerce and Industry under Ministerial Decree No. (1 /2021 ), on     
29/05/1442  H, corresponding to 13 /01 /2021 G. 
QS 2663 :2020  cancels and replaces QS  SASO  2663 :2015   
 
 
 
 
 FinaL DraftQATAR STANDARD  QS  2663/2020  
 
2 
 ENERGY LABELLING AND MINIMUM  
ENERGY PERFORMANCE REQUIREMENTS  
FOR AIR -CONDITIONERS  
 
1. SCOPE  AND OBJECTIVE  
1.1 Scope  
 This standard specifies the energy labelling requirements and the Minimum 
Energy Performance Standard (MEPS) requirements for single -package (such as 
window type) and split -system non -ducted air conditioners using air - and water -
cooled condensers and heat pumps employing air -cooled condensers and ducted  
air-conditioners using  air-to-air heat pumps for residential , commercial and 
industrial sector as applicable in accordance with Qatari  standards.  
1.2 Objective  
 The objective of this standard is to:  
a) Provide detailed information on the performance and energy labelling 
requirements which an air conditioning  appliance has to meet in order to 
carry a valid energy efficiency label; and  
b) Provide detailed information on the performance requirements which a n 
air-conditioning appliance has to meet in order to meet minimum energy 
performance standard requirements.  
 
2. NORMATIVE REFERENCES  
         Updated editions of the following normative ref erences  are applied  (Including any  
         changes on these normat ive references).  
 
2.1 QS ISO :5151 “Non-ducted air conditioners and heat Pumps -Testing and rating 
for Performance” . 
2.2 QS ISO :13253 “Ducted air -conditioners and air -to-air heat Pumps - Testing and 
rating for Performance ”. 
 
3. TERMS AND DEFIN ITIONS  
 For the purposes of this standard, the terms and definitions given in QS 
mentioned in sub -clauses 2.1 and 2.2 and those below are considered.  
3.1 Ducted air conditioners  
 An air conditioner  model configuration where the indoor side is situated remote 
to the space to the conditioned.  The conditioned air is supplied or extracted via 
a duct.  
3.2 Non-ducted air conditioner  
 An air conditioner  model configuration where the indoor side is situate d partly 
or wholly within the space to be conditioned.  The conditioned air is supplied 
and extracted directly to and from the conditioned space.  FinaL DraftQATAR STANDARD  QS  2663/2020  
 
3 
 3.3 Rated capacity  
 The nominal rated capacity claimed by the manufacturer of an air conditioner  
model determi ned as follows, as applicable:  
(a) Rated total cooling capacity   as claimed by the manufacturer for 
temperature condition T1 and T3.  (Units: Btu/h).  
(b) Rated heating capacity   as claimed by the manufacturer for temperature 
condition H1.  (Units Btu/h).  
 The rated capacity appears on the energy label as ‘Capacity Output’ (heating 
and/or cooling as applicable.  (Units: Btu/h).  
3.4 Rated power  
 Effective power input of the air conditioner  model as claimed by the 
manufacturer during the determination of rated cooling capacity and rated 
heating capacity, as applicable.  (Units: W or kW.)  
3.5 Split system  
 An air conditioner  with separate indoor and outdoor components that are 
connected with refrigerant piping.  The indoor unit usually lies within the 
conditioned space and may be installed or portable/mobile.  
3.6 Star rating  
 The number of stars displayed on the energy label.  Available stars are between 
a minimum of one and a maximum of six.  It is considered as an indication of 
the claimed energy efficiency of a model at rated conditions.  A higher star rating 
indicates a higher energy efficiency.  It is derived from the measured EER.  
3.7            Estimated annual energy consumption  
                 Rated power expected within 2700 working hour with a full load annually.  
                 Formula to calculate  the Estimated Annual Energy Consumption:  
                 Estimated Annual Energy Consumption = (Total  Input Power i n KW at (T1) 
conditions)  x (2700  hours/year ).   
 
 
4. REGISTRATION REQUIREMENT S 
4.1       The information about registration requirement for energy labelling and  
                   MEPS will be available in QATA R GENERAL ORAGANIZTION   
STANDAR DIZATION  (QS)  
 
4.2 For registration of an air conditioner  for energy labelling and MEPS with a test 
report in accordance with re cent edition of QS ISO 5151 or QS ISO 13253 , as 
applicable.  An application shall be provided for each model, in accordance with 
Appendix A, and submitted to the registration body.  
 FinaL DraftQATAR STANDARD  QS  2663/2020  
 
4 
  
4.3 Energy Label Validity (Check Testing)  
 The energy label shall be accepted as valid when a single sample of an ap pliance 
or unit model, tested for an initial screening test, meets the following criteria for 
cooling and heating, as applicable:  
              a)      Tested effective power input ………….........… …. ≤1.05 x rated power.  
b) Tested cooling and heating capacity ……… …. ….0.95 x rated capacity.  
c) Tested EER …………………………………….… ….0.95 x rated EER.  
d) Tested COP …………………………………….……. 0.95 x rated COP.  
        e)      Tested voltage ..................... 240-volt single phase or 415-volt three 
phase.  
f) Tested freq uency …………………………………… ……………. 50 Hz. 
              g)      Testing conditions ( T1, T3 ) ......  (refer to the standards mentioned in 
clause 2).  
 
5. MEPS  
The minimum energy performance standard MEPS value for the air conditioner in the 
scope of this standard shall be  greater than or equal to the value of Energy Efficiency  Ratio 
(EER ), When calculating the cooling capacity at test conditions ( T1) and test co ndition 
(T3) as follows:  
 
 
 
 
Air Conditioner 
appliance type   
Cooling 
Capacity 
limit (CC)  
(Btu/h)  
At test 
condition 
(T1) (EER) Value  
(Btu/h)/watt  
To be applied 
mandatory  
 
 First Stage  (EER) Value  
(Btu/h)/watt  
To be applied 
mandatory  
 
Second Stage  
T1 T3 T1 T3 
 
 
Window Type  18000 > CC  8.5 6.12 8.5 6.12 
18000     CC 
< 24000  8.5 6.12 8.5 6.12 
CC     24000  8.5 6.12 8.5 6.12 
Split Type and the 
other types  All Capacities  9.5 6.84 11.5 8.28 
 
6. NAME PLATE AND INSTRUCTION SHEET OR MANUAL  
 In addition to any information needed to be displayed on the air -conditioner unit, 
the following information shall be marked on the name plate of the air -
conditioner, in Arabic or English or both. The marking  shall not be on a 
detachable part of the unit and shall be indelible, durable and easily legible.  FinaL DraftQATAR STANDARD  QS  2663/2020  
 
5 
  Any information related energy performance added showed in any part of the 
air-conditioner unit or packaging shall not have any ambiguity or lead to miss 
understand of the performance of the unit.  
6.1 The information on the name plate in Arabic or English or both shall include at 
least:  
– Manufacturer’s name and/or trademark.  
– Country of origin.  
– Manufacturer’s model or type reference and serial numb er of the unit.  
– Rated voltage or rated voltage range (Volts).  
– Rated frequency (Hz).  
– For each of cooling test conditions T1 and T3 according to the standard 
stated in clauses 2.1 and 2.2, as applicable:  
• Rated current in Amperes.  
• Rated power input in watts or kilowatts.  
• Net total room cooling capacity in Btu/h (and any units of kW or 
Kcal/h) when tested according to conditions stated in clauses 2.1 and 
2.2. 
• Energy Efficiency Ratio (EER) in (Btu/ hr.)/Watt.  
– For heating test conditions according to the standard stated in clauses 2.1 
and 2.2, as applicable.  
• Current rating (Amperes).  
• Input power rating (watts or kilowatts).  
• Heating capacity in W when tested according to conditions stated in 
clauses 2.1 and 2.2, as applicable.  
• Coeff icient of Performance (COP) (watt/watt).  
– Refrigerant used and mass of refrigerant charge in kg.  
6.2 An instruction sheet or manual in both Arabic and English shall be delivered 
with each air -conditioner, including the following information:  
– The informa tion specified in clause 6.1.  
– Dimensions of the unit and its method of mounting.  
– Minimum clearances between the various parts of the unit and the 
surrounding framework.  
– Instructions necessary for the correct operation of the unit and any special 
precautions to be observed to ensure its safe use and maintenance.  
– Instruction for packing and unpacking the unit.  
– Weight of the unit.  
– Any other additional information.  FinaL DraftQATAR STANDARD  QS  2663/2020  
 
6 
                        –        Annual energy consumption for calculating the expected rated power  
                                 within 2700 working  hour with full load annually.  
 
 
7. ENERGY RATING CLASSIFICATION  
7.1 The energy efficiency class  rating is  used for the comparative label used with 
window type and split type  air-cooled  air-conditioner with cooling capacity less 
than and including 70000 Btu/h (20000 W).  
7.2 The energy efficiency class is then determined in accordance with the following 
table, where the EER (energy efficiency ratio) is determined in accordance with 
the test procedures of the harmonized standards referred to in Article 2 at 
condition T1 & T 3. 
 7.3           Stars No. on Label For 1st & 2ed Stages : 
  a) 1st Stage : 
EER limits  
(Btu/h)/w at T 1 EER limits  
(Btu/h)/w at T 3 Star Rating  Status  
EER     12.5 EER      9.00 8 Applied  
12.5    > EER      11.5 9.00   > EER       8.28 7 Applied  
11.5    > EER      10.0 8.28   > EER       7.20 6 Applied  
10.0    > EER       9.5 7.20   > EER       6.84 5 Applied  
9.5      > EER       9.0 6.84   > EER       6.48 4 Applied  
9.0      > EER       8.5 6.48   > EER       6.12 3 Applied for  
 Window Type only  
 
EER   ˂ 8.5  
EER ˂ 6 .12  
Not Applicable  
 
  
 
 
 
 
 
 
 
 
 FinaL DraftQATAR STANDARD  QS  2663/2020  
 
7 
  
 
b) 2ed Stage for split type:  
EER limits  
(Btu/h)/w at T 1 EER limits  
(Btu/h)/w at T 3 Star 
Rating  Status  
EER     14.5 EER      10.44  9  
 
 
 
Applied for  
split Type only  14.5    > EER      
13.5 10.44   > EER      
9.72 8 
13.5    > EER      
12.5 9.72   > EER       
9.00 7 
12.5    > EER       
11.5 9.   > EER           
8.28 6 
EER  ˂ 11.5 EER ˂ 8.28 _ Not Applicable  
 
C) 2ed Stage for window type:  
EER limits  
(Btu/h)/w at T1  EER limits  
(Btu/h)/w at T3  Star Rating  
Status  
11    > EER       10 7.92   > EER       7.20 5 
Applied for  
Window Type only  10      > EER       9.0 7.20 > EER       6.48 4 
9.0      > EER       8.5 6.48 > EER       6.12 3 
 
EER   ˂ 8.5  
EER ˂ 6 .12  
_  
Not Applicable  
8.  ENERGY LABELLING REQUIREMENTS  
8.1 Information and Values Contained in the Energy Labels   
The font should be written “ AXt ALMANAL Bold ” for Arabic and “ Arial” for  
Engli sh as well as the Sticker Color Pallete are as illustrated in the Figure 7&8 
entitled  (Colors,  Fonts  & Dimensions of the Stickers ) Figure 7&8.  
 Note :  The cooling capacity and power input values shown on the energy label are based on the 
tested  cooling capacity and the tested  power , as declared by the manufacturer as well as shown 
in the nameplate for condition T1 for cooling capacity in accordance with the standard mentioned 
in clause 2.1  and 2.2. 
8.2 Sample Labels  
 Example of printed energy label for air -conditioning applia nces are shown in 
Figures 2, 3, 4, & 5. FinaL DraftQATAR STANDARD  QS  2663/2020  
 
8 
                   Qatar General Organization for Sta ndardization  has right to modify the form  of 
the label.  
8.3 Dimensions of Labels  
 Figure 8&9 shows the dimensions of label for  the split & window type . 
8.4 Placement of Energy Labels  
 The label shall be adhered, or attached as a swing tag, on the front of the unit.  
Additional label may be attached to the exterior of the packaging.  The label shall 
be existed on the unit when the unit is removed from its packaging for display 
purposes.  
8.5 Material and Shape of Energy Labels  
 The label shall be of durable cardboard, if it is to be attached as a swing tag, or 
be self -adhesive, and shall be cut to the outline shown in Figure 8&9. A trim or 
die cut margin of up to 5 mm around the label is acceptable.  
 
 
 
  FinaL DraftQATAR STANDARD  QS  2663/2020  
 
9 
  
FIGURE 1: Example of Label For Window type & Cooling Unit – 3 stars  
 
 
 
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
10 
  
FIGURE 2: Example of Label For Window type & Cooling Unit – 4 stars  
 
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
11 
  
FIGURE 3: Example of Label For Window type & Cooling Unit – 5 stars  
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
12 
  
FIGURE 4: Example of Label  for split  type& Cooling Unit – 6 stars  
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
13 
  
FIGURE 5: Example of Label for split type & Cooling Unit – 7stars  
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
14 
  
FIGURE 6: Example of Label for split type & Cooling Unit – 8 stars  
 
 
 
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
15 
  
FIGURE 7: Example of Label for split type & Cooling Unit – 9 stars  
 
 
 
 
 
 
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
16 
  
 
FIGURE  8: Colors , Fonts & Dimensions of Sticker for split type  
 
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
17 
  
FIGURE  9:Colors, Fonts & Dimensions of Sticker for window  type 
 
 
 
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
18 
  
 
 
 
 
 
 
 
 
 
 
 
 
 
 
 
 
 
 
 
 
 
 
 
FinaL DraftQATAR STANDARD  QS  2663/2020  
 
19 
 APPENDIX A  
APPLICATION FOR REGISTRATION OF  
AIR-CONDITIONERS FOR ENERGY LABELLING AND MEPS  
(please type or print)  
 
 
This Appendix sets out the required format for submitting an application for registration. 
Application for registration of an air -conditioner for energy efficiency.  
 
I hereby apply for registration of an electrical appliance/s for the purpose of energy la belling.  
 
In the Country of  ................................ ................................ ................................ ...............................   
(specify the country in which this application is made ) 
 
 
 
 
   PART 1   APPLICANT INFORMATION  
 
   Applicant Name:  ……………………………… ...........................................................................  
   Company Name:  ……………………… ........................................................................... ………  
   Company Address:  ………… ................................................... ........................ ………………....  
   P.O. Box               : …………………………....   Post Code: .......................................................  
   Contact Person:  (Name and Addr ess and workplace in each sales country)  
   Job Title:  ……………………………………  
   Phon e: ……………………       Fax: ………………….       Electronic Mail:  ..........................  
 
     Supplier or Vendor in Qatar : 
 
              No.    Supplier or 
Vendor Name  Contact Address  
(Mail Address, 
Phone, Fax, 
Electronic Mail)  License Number or 
Commercial 
Licen ses (related to 
import and sale of 
goods in Qatar .  
    
    FinaL DraftQATAR STANDARD  QS  2663/2020  
 
20 
 Part 2 DESCRIPTION  OF THE APPLIANCE  
Model Name (if available)   
Model Number or Family Number:   
Model Number:  
(on indoor unit for split systems)   
Model Number on Outdoor Unit:  
 (split systems only)   
Other Model Numbers to be included under this registration:   
Country of Manufacture:   
Year in which model first available in Qatar :  
Model Number(s) to appear on the Energy Label:  
  
Date of manufacture traceability (of package unit or indoor 
unit if split system):  
Is the date of manufacture permanently marked on the rating 
plate in a non -encrypted format?  
If yes, provide an example of the date format.  
If no, provide details on how to determine (from the 
serial number or other permanent markings for this 
model)  
 Yes 
Date format:  No Provide details:  
'Date of manufacture traceability (of outdoor unit if split 
system):  
Is the date of manufacture permanently marked on the rating 
plate in a non -encrypted format?  
If yes, provide an example of the date format.  
If no, provide details on how to be determined (from the 
serial number or other permanent markings for this model)  Yes 
Date format : No                 Provide details:  
Does this model or family replace or supplement another 
model or family with identical energy consumption and 
energy efficiency rating?  
(indicate correct answer)  Yes No 
If yes, indicate relevant details:  
 
 
 Model 
name  
 Model 
number  Registration number  
Information  about the components used in the 
manufacturing : 
There must be complementary  documents for the 
materials used in the Manufacturing including 
drawings and figures and technical specifications 1- Compressor  
Country of origin: …………………………..  
Name of Manu facturer or his trading mark: ……  
Compressor model number: ………………… … 
Compressor type: …………………….………….  FinaL DraftQATAR STANDARD  QS  2663/2020  
 
21 
 and product model accreditation (if any) for each 
of the components mentioned here.   
2- Fan 
Country of origin:…… …. 
Name of Manu facturer or his trading mark: … …. 
Fan Model number: ………..  
Fan type: …………………….  
 
3- Heat Exchanger  
Volume and des cription of the heat exchanger: …. 
 
 
Part 3 TESTING  AND TEST REPORT   
Test Laboratory Type:  
(put () inside the appropriate box)  
   Own 'in -house' laboratory:  
 Independent laboratory:  
Test Laboratory Name:   
Test Laboratory Address:   
Test Laboratory Location:  
 
  Qatar   
 Other — (please specify):  
Test Laboratory Accreditation:  
   Accredited from a body member in (ILAC)  
 
Test Standard Used:  
 
  QS ISO 5151 (the standard mentioned in 2.1)  
 QS ISO 13253 (the standard mentioned in 2.2)  
Other — (please specify)  
 
Does this air conditioner  have separate indoor 
and outdoor units   Yes 
 No 
Serial number of test units/s and date tested:  SERIAL NUMBER 
Unitary unit or 
indoor unit if split 
system  SERIAL 
NUMBER 
Outdoor unit if 
split system  Test date  
   
Rated voltage and frequency of tested unit  Package unit  Unitary unit or 
indoor unit if 
split system  Outdoor unit if split system  
Rated voltage or  
Rated voltage range 
(V)   
Rated frequency  
(Hz)   
Tested voltage and frequency of tested unit   Unitary unit or 
indoor unit if 
split system  Outdoor unit if split system  
Tested voltage (V)    
Test frequency (Hz)    FinaL DraftQATAR STANDARD  QS  2663/2020  
 
22 
  
 
 
 
  Part 4 SPECIFIC  APPLICANCE DETAILS  
Air-conditioner dimensions (Advisory 
only):  
(for split systems note only dimensions of the 
internal unit)  Width (mm):  
 Height (mm):  
 Depth (mm):  
 
Air-conditioner type:  
  Cooling only  
 Reverse cycle  
 Heating only  
 Other (please specify)  
 
Power supply:  
  Single -phase  
 Three -phase  
Rated Voltage ( V):  
Rated Frequency  (Hz):   
Refrigerant Number:  
  R22,  
 Other (please specify)  
 
A/C Configuration 1 —Air Distribution  
 
  Ducted  
 Non ducted  
A/C Configuration 2 —Type  
 
  Window/Wall,  
 Spot cooler,  
 Portable cooler,  
 Single split system  
 Double/triple split system,  
 Multiple split system,  
 Packaged  
 
Does this air -conditioner use a variable speed 
drive (inverter) or a multi -speed compressor?  
  Yes 
 No 
 FinaL DraftQATAR STANDARD  QS  2663/2020  
 
23 
  
Part 5 TEST  RESULTS  
 
TEST RESULTS —COOLING —CONDITION T1  
 
COOLING POWER  
 Rated Effective Power 
Input (kW)*  
  
Tested Cooling Power 
Input ( kW)**  
  
COOLING CAPACITY  
 Rated Total Cooling 
Capacity (Btu)*  
  
Tested Total Cooling 
Capacity ( Btu)**  
  
EER (Btu/h)/W  
 Rated EER **   
Tested EER **   
The class rating number according  to clause  7 of QS 
2663 :2020  (This standard)  
  Yes 
 No 
 
 
*     to 2 decimal places  
**   to 3 decimal places   FinaL DraftQATAR STANDARD  QS  2663/2020  
 
24 
  
TEST RESULTS —COOLING —CONDITION T3  
 
COOLING POWER  
 Rated Effective Power 
Input (kW)*  
  
Tested Cooling Power 
Input ( kW)**  
  
COOLING CAPACITY  
 Rated Total Cooling 
Capacity (kW)*  
  
Tested Total Cooling 
Capacity ( kW)**  
  
EER (Btu/h)/W  
 Rated EER **   
Tested EER **   
The class rating number according to clause 7 of QS 
2663/ 2020  (This standard)   Yes 
 No 
 
*    to 2 decimal places  
** to 3 decimal places  
 
 
 
 
 
 
 
 
 FinaL DraftQATAR STANDARD  QS  2663/2020  
 
25 
 TEST RESULTS —HEATING — 
Does this model incorporate electric resistance heating?   Yes 
 No 
HEATING POWER  
 Rated Effective Power 
Input (kW)*   
Tested Heating Power 
Input ( kW)**   
HEATING CAPACITY  
 Rated Total Heating 
Capacity ( kW)*   
Tested Heating Capacity 
(kW)**   
COP (w/w)  
 Rated COP **    
Tested COP **  
* to 2 decimal places  
** to 3 decimal places  
 
 
DECLARATION  
 
I declare that the details stated above are correct.  
Signature of Applicant: .............................................       Date: ...................................  
Office use only  
 Date received: .............................             Registration number: ..................................  
 
 
 
  