This section of the FEDERAL REGISTER
contains regulatory documents having generalapplicability and legal effect, most of whichare keyed to and codified in the Code ofFederal Regulations, which is published under50 titles pursuant to 44 U.S.C. 1510.
The Code of Federal Regulations is sold by
the Superintendent of Documents.Rules and RegulationsFederal Register36217 
Vol. 88, No. 106 
Friday, June 2, 2023 
DEPARTMENT OF AGRICULTURE 
Rural Utilities Service 
7 CFR Part 1735 
[Docket No. RUS–20–TELECOM–0044] 
RIN 0572–AA48 
Implementation of 
Telecommunications Provisions of the Agricultural Improvement Act of 2018; Correction 
AGENCY : Rural Utilities Service, 
Department of Agriculture (USDA). 
ACTION : Correcting amendment. 
SUMMARY : On September 10, 2021, Rural 
Development’s Rural Utilities Service (hereinafter referred to as ‘‘the Agency’’) published a document that completed modifications to existing program regulations to implement statutory provisions of the Agriculture Improvement Act of 2018 (2018 Farm Bill). Following the final implementation of the final rule, the Agency found that an amendment was necessary to clarify the meaning of a sentence. This document clarifies the final rule. 
DATES : Effective June 2, 2023. 
FOR FURTHER INFORMATION CONTACT : For 
information specific to this document contact Laurel Leverrier, Assistant Administrator Telecommunications Program, Rural Utilities Service, U.S. Department of Agriculture (USDA), email: laurel.leverrier@usda.gov, 
telephone: (202) 720–9556. 
SUPPLEMENTARY INFORMATION : The Rural 
Utilities Service is issuing a correcting amendment to provide clarification to the final rule that published September 10, 2021, at 86 FR 50604. In that rule, the wording of § 1735.23(a) was not clear. This clarifying amendment provides for clear information for readers. List of Subjects in 7 CFR Part 1735 
Loan programs—communications, 
Reporting and recordkeeping requirements, Rural areas, Telephone. 
For the reasons stated in the 
preamble, the Rural Utilities Service corrects 7 CFR part 1735 by making the following correcting amendment: 
PART 1735—GENERAL POLICIES, 
TYPES OF LOANS, LOAN REQUIREMENTS— TELECOMMUNICATIONS PROGRAM 
■1. The authority citation for part 1735 
continues to read as follows: 
Authority: 7 U.S.C. 901 et seq., 1921 et 
seq., and 6941 et seq. 
■2. Amend § 1735.23 by revising the 
introductory text of paragraph (a) to read as follows: 
§ 1735.23 Public notice. 
(a) For applications which request 
funding in which the applicant will provide retail broadband service, the Agency’s mapping tool will include the following information from each application, and be displayed for the public: 
* * * * * 
Andrew Berke, 
Administrator, Rural Utilities Service, U.S. 
Department of Agriculture. 
[FR Doc. 2023–11724 Filed 6–1–23; 8:45 am] 
BILLING CODE 3410–15–P 
DEPARTMENT OF ENERGY 
10 CFR Part 431 
[EERE–2019–BT–TP–0041] 
RIN 1904–AE57 
Energy Conservation Program: Test 
Procedure for Commercial Warm Air Furnaces 
AGENCY : Office of Energy Efficiency and 
Renewable Energy, Department of Energy. 
ACTION : Final rule. 
SUMMARY : The U.S. Department of 
Energy (DOE) is amending the Federal test procedures for commercial warm air furnaces (CWAFs) to incorporate the latest versions of the industry test standards that are currently incorporated by reference. DOE is also establishing a new metric, Thermal 
Efficiency Two (TE2), and corresponding test procedure. Use of the newly established test procedure would become mandatory at such time as compliance with amended energy conservation standards based on TE2 is required, should DOE adopt such standards. DOE also is adopting additional specifications for CWAFs with multiple flue outlets or small flue outlets. 
DATES : The effective date of this rule is 
July 3, 2023. These amendments will be mandatory for CWAF equipment testing starting May 28, 2024. The incorporation by reference of certain material listed in this rule is approved by the Director of the Federal Register on July 3, 2023. 
ADDRESSES : The docket, which includes 
Federal Register notices, public meeting attendee lists and transcripts, comments, and other supporting documents/materials, is available for review at www.regulations.gov under 
docket number EERE–2019–BT–TP– 0041. All documents in the docket are listed in the www.regulations.gov index. 
However, not all documents listed in the index may be publicly available, such as those containing information that is exempt from public disclosure. 
A link to the docket web page can be 
found at: www.regulations.gov/docket/ EERE-2019-BT-TP-0041. The docket 
web page contains instructions on how to access all documents, including public comments, in the docket. 
For further information on how to 
review the docket, contact the Appliance and Equipment Standards Program staff at (202) 287–1445 or by email: ApplianceStandardsQuestions@
ee.doe.gov. 
FOR FURTHER INFORMATION CONTACT : Ms. 
Julia Hegarty, U.S. Department of Energy, Office of Energy Efficiency and Renewable Energy, Building Technologies Office, EE–5B, 1000 
Independence Avenue SW, Washington, DC 20585–0121. Telephone: (240) 597– 6737. Email: ApplianceStandardsQuestions@ee.doe.gov. 
Mr. Eric Stas, U.S. Department of 
Energy, Office of the General Counsel, GC–33, 1000 Independence Avenue SW, Washington, DC 20585–0121. Telephone: (202) 586–5827. Email: Eric.Stas@hq.doe.gov. 
SUPPLEMENTARY INFORMATION : 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00001 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136218 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
1All references to EPCA in this document refer 
to the statute as amended through the Energy Act 
of 2020, Public Law 116–260 (Dec. 27, 2020), which reflect the last statutory amendments that impact Parts A and A–1 of EPCA. 
2For editorial reasons, upon codification in the 
U.S. Code, Part C was redesignated Part A–1. DOE incorporates by reference the 
following industry standards into part 
431: 
ANSI/AHRI 1500–2015 Performance 
Rating of Commercial Space Heating Boilers (‘‘AHRI 1500–2015’’); 
Copies of AHRI 1500–2015 can be 
obtained from the Air-Conditioning, Heating, and Refrigeration Institute (AHRI), 2311 Wilson Blvd., Suite 400, Arlington, VA 22201, (703) 524–8800, or online at: www.ahrinet.org. 
CSA/ANSI Z21.47:21, Gas-fired 
central furnaces (‘‘ANSI Z21.47–2021’’); 
ANSI/ASME PTC 19.3–1974 (R2004), 
Supplement to ASME Performance Test Codes: Part 3: Temperature Measurement, Instruments and Apparatus; 
ANSI/ASHRAE 103–2022, Method of 
Testing for Annual Fuel Utilization Efficiency of Residential Central Furnaces and Boilers (‘‘ASHRAE 103– 2022’’); 
Copies of ANSI Z21.47–2021, ANSI/ 
ASME PTC 19.3–1974 (R2004) and ANSI/ASHRAE 103–2022, can be obtained from the American National Standards Institute (ANSI), 25 W 43rd Street, 4th Floor, New York, NY 10036, (212) 642–4900, or online at: www.webstore.ansi.org. 
ASTM D240–09, Standard Test 
Method for Heat of Combustion of Liquid Hydrocarbon Fuels by Bomb Calorimeter; 
ASTM D396–14a, Standard 
Specification for Fuel Oils; 
ASTM D4809–09a, Standard Test 
Method for Heat of Combustion of Liquid Hydrocarbon Fuels by Bomb Calorimeter (Precision Method); 
ASTM D5291–10, Standard Test 
Methods for Instrumental Determination of Carbon, Hydrogen, and Nitrogen in Petroleum Products and Lubricants; 
ASTM E230/E230M–17, Standard 
Specification for Temperature- Electromotive Force (emf) Tables for Standardized Thermocouples (‘‘ASTM E230/E230M–17’’); 
Copies of ASTM D240–09, ASTM 
D396–14a, ASTM D4809–09a, ASTM D5291–10, and ASTM E230/E230M–17 can be obtained from ASTM International, 100 Barr Harbor Drive, P.O. Box C700, West Conshohocken, PA 19428, (877) 909–2786 or online at: www.astm.org. 
NFPA 97–2003, Standard Glossary of 
Terms Relating to Chimneys, Vents, and Heat-Producing Appliances. 
Copies of NFPA 97–2003 can be 
obtained from the National Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy, MA 02169– 7471, (1–800–344–3555) or online at: www.nfpa.org. UL 727, Standard for Safety Oil-Fired 
Central Furnaces (‘‘UL 727–2018’’); 
Copies of UL 727–2018 can be 
obtained from Underwriters Laboratories, Inc. (UL), 333 Pfingsten Road, Northbrook, IL 60062, (847) 272– 8800 or online at: www.standardscatalog.ul.com. 
For a further discussion of these 
standards, see section IV.N of this document. 
Table of Contents 
I. Authority and Background 
A. Authority 
B. Background 
II. Synopsis of the Final Rule III. Discussion 
A. Scope of Applicability B. Updates to Industry Standards 1. UL 727 2. HI BTS and AHRI 1500 3. ANSI Z21.47 4. ASHRAE 103 C. ‘‘Thermal Efficiency Two’’ Metric 1. Jacket Loss 2. Part-Load Performance D. Electrical Energy Consumption E. Other Test Procedure Updates and 
Clarifications 
1. Flue Temperature Measurement in 
Models With Multiple Flue Outlets 
2. Flue Temperature Measurement in 
Models With Vent Space Limitations 
3. Flue Loss Determination 4. General Approach F. Effective and Compliance Dates G. Test Procedure Costs 
IV. Procedural Issues and Regulatory Review 
A. Review Under Executive Orders 12866, 
13563, and 14094 
B. Review Under the Regulatory Flexibility 
Act 
C. Review Under the Paperwork Reduction 
Act of 1995 
D. Review Under the National 
Environmental Policy Act of 1969 
E. Review Under Executive Order 13132 F. Review Under Executive Order 12988 G. Review Under the Unfunded Mandates 
Reform Act of 1995 
H. Review Under the Treasury and General 
Government Appropriations Act, 1999 
I. Review Under Executive Order 12630 J. Review Under Treasury and General 
Government Appropriations Act, 2001 
K. Review Under Executive Order 13211 L. Review Under Section 32 of the Federal 
Energy Administration Act of 1974 
M. Congressional Notification 
N. Description of Materials Incorporated by 
Reference 
V. Approval of the Office of the Secretary 
I. Authority and Background 
CWAFs are included in the list of 
‘‘covered equipment’’ for which DOE is 
authorized to establish and amend energy conservation standards and test procedures. (42 U.S.C. 6311(1)(J)) DOE’s energy conservation standards and test procedures for CWAFs are currently prescribed at subpart D of part 431 of title 10 of the Code of Federal Regulations (CFR). The following 
sections discuss DOE’s authority to establish and amend test procedures for CWAFs and relevant background information regarding DOE’s consideration of test procedures for this equipment. 
A. Authority 
The Energy Policy and Conservation 
Act, as amended (EPCA),
1among other 
things, authorizes DOE to regulate the 
energy efficiency of a number of consumer products and certain industrial equipment. (42 U.S.C. 6291– 6317) Title III, Part C
2of EPCA, Public 
Law 94–163 (42 U.S.C. 6311–6317, as codified) added by Public Law 95–619, Title IV, section 441(a), established the Energy Conservation Program for Certain Industrial Equipment, which sets forth a variety of provisions designed to improve energy efficiency. This covered equipment includes CWAFs, the subject of this final rule. (42 
U.S.C. 6311(1)(J)) 
The energy conservation program 
under EPCA consists essentially of four parts: (1) testing, (2) labeling, (3) Federal energy conservation standards, and (4) certification and enforcement procedures. Relevant provisions of EPCA include definitions (42 U.S.C. 6311), energy conservation standards (42 U.S.C. 6313), test procedures (42 U.S.C. 6314), labeling provisions (42 U.S.C. 6315), and the authority to require information and reports from manufacturers (42 U.S.C. 6316; 42 U.S.C. 6296). 
The Federal testing requirements 
consist of test procedures that manufacturers of covered equipment must use as the basis for: (1) certifying to DOE that their equipment complies with the applicable energy conservation standards adopted pursuant to EPCA (42 U.S.C. 6316(b); 42 U.S.C. 6296), and (2) making other representations about the efficiency of that equipment (42 U.S.C. 6314(d)). Similarly, DOE uses these test procedures to determine whether the equipment complies with relevant standards promulgated under EPCA. 
Federal energy efficiency 
requirements for covered equipment established under EPCA generally supersede State laws and regulations concerning energy conservation testing, labeling, and standards. (42 U.S.C. 6316(a) and 42 U.S.C. 6316(b); 42 U.S.C. 6297) DOE may, however, grant waivers 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00002 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136219 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
3DOE determined that UL 727–1994 did not 
provide a procedure for calculating the percent flue 
loss of the furnace, which is necessary in 
calculating the TE, and, therefore, incorporated by reference provisions from HI BTS–2000 to calculate the flue loss for oil-fired CWAFs. 69 FR 61916, 61917, 61940 (Oct. 21, 2004). 
4UL 727–1994 is also incorporated by reference 
in 10 CFR 431.75 but is no longer referenced in the test method specified in 10 CFR 431.76, which references only UL 727–2006. of Federal preemption in limited 
circumstances for particular State laws or regulations, in accordance with the procedures and other provisions of EPCA. (42 U.S.C. 6316(b)(2)(D)) 
Under 42 U.S.C. 6314, EPCA also sets 
forth the criteria and procedures DOE must follow when prescribing or amending test procedures for covered equipment. Specifically, EPCA requires that any test procedures prescribed or amended under this section must be reasonably designed to produce test results which reflect energy efficiency, energy use or estimated annual 
operating cost of a given type of covered equipment (or class thereof) during a representative average use cycle and requires that test procedures not be unduly burdensome to conduct. (42 U.S.C. 6314(a)(2)) 
EPCA requires that the test procedure 
for CWAFs be those generally accepted industry testing procedures or rating procedures developed or recognized by the Air-Conditioning, Heating, and Refrigeration Institute (AHRI) or by the American Society of Heating, Refrigerating and Air-Conditioning Engineers (ASHRAE), as referenced in ASHRAE Standard 90.1, ‘‘Energy Standard for Buildings Except Low-Rise Residential Buildings’’ (ASHRAE Standard 90.1). (42 U.S.C. 6314(a)(4)(A)) Further, if such industry test procedure is amended, DOE must amend its test procedure to be consistent with the amended industry test procedure, unless DOE determines, by rule published in the Federal Register and supported by clear and convincing evidence, that such amended test procedure would not meet the requirements in 42 U.S.C. 6314(a)(2) and (3) related to representative use and test burden, in which case DOE may establish an amended test procedure that does satisfy those statutory provisions. (42 U.S.C. 6314(a)(4)(B) and (C)) 
EPCA also requires that, at least once 
every seven years, DOE evaluate test procedures for each type of covered equipment, including CWAFs, to determine whether amended test procedures would more accurately or fully comply with the requirements for the test procedures to not be unduly burdensome to conduct and be reasonably designed to produce test results that reflect energy efficiency, energy use, and estimated operating 
costs during a representative average use cycle. (42 U.S.C. 6314(a)(1)–(3)) 
In addition, if DOE determines that a 
test procedure amendment is warranted, the Department must publish proposed test procedures in the Federal Register and afford interested persons an opportunity (of not less than 45 days duration) to present oral and written data, views, and arguments on the 
proposed test procedures. (42 U.S.C. 6314(b)) If DOE determines that test procedure revisions are not appropriate, DOE must publish in the Federal Register its determination not to amend 
the test procedures. (42 U.S.C. 6314(a)(1)(A)(ii)) As discussed further in section I.B of this document, in January 2023, ASHRAE released the latest version of ASHRAE Standard 90.1 (ASHRAE Standard 90.1–2022), which updated the referenced industry standards for testing CWAFs to reflect the most recent versions of those standards that are currently available, thereby triggering DOE’s rulemaking obligations under EPCA. DOE is publishing this final rule amending the test procedure for CWAFs in satisfaction of both the ‘‘ASHRAE trigger’’ requirement under 42 U.S.C. 6314(a)(4)(B) and the 7-year-lookback review requirement specified in EPCA under 42 U.S.C. 6314(a)(1). 
B. Background 
DOE’s current test procedure for 
CWAFs is codified at 10 CFR 431.76, 
‘‘Uniform test method for the measurement of energy efficiency of commercial warm air furnaces.’’ The currently applicable test procedure incorporates by reference two industry standards for testing gas-fired CWAFs: American National Standards Institute (ANSI) Z21.47–2012, ‘‘Standard for Gas- fired Central Furnaces’’ (ANSI Z21.47– 2012), which is used for all types of gas- fired CWAFs; and ANSI/American Society of Heating, Refrigeration, and Air-conditioning Engineers (ASHRAE) Standard 103–2007, ‘‘Method of Testing for Annual Fuel Utilization Efficiency of Residential Central Furnaces and Boilers’’ (ANSI/ASHRAE 103–2007), which is specifically used for testing condensing gas-fired CWAFs. 10 CFR 431.76 (c)(1), (d)(2), (e)(1), and (f)(1); 10 CFR 431.75(b)(1) and (c)(1). The current test procedure also incorporates by reference two industry standards for 
testing oil-fired CWAFs: Hydronics Institute Division of AHRI (HI) BTS– 
2000 Rev 06.07, ‘‘Method to Determine Efficiency of Commercial Space Heating Boilers’’ (HI BTS–2000)
3and 
Underwriters Laboratories (UL) standard UL 727–2006, ‘‘Standard for Safety Oil- Fired Central Furnaces’’ (UL 727– 2006).
410 CFR 431.76(c)(2), (d)(1), and 
(e)(2); 10 CFR 471.75(d)(1) and (e)(2). 
DOE most recently amended the test 
procedure for CWAFs in a final rule published in the Federal Register on 
July 17, 2015, which updated the test procedure for gas-fired CWAFs to incorporate by reference the latest versions of the industry standards available at the time (i.e., ANSI Z21.47– 
2012 and ANSI/ASHRAE 103–2007). 80 FR 42614 (July 2015 final rule). At the time of the July 2015 final rule, UL 727– 2006 and HI BTS–2000 were still the most recent versions of those industry standards. 
Under EPCA’s seven-year-lookback 
provision, DOE initiated a test procedure rulemaking for CWAFs by publishing a request for information (RFI) in the Federal Register on May 5, 2020 (May 2020 RFI). 85 FR 26626. The May 2020 RFI solicited public comments, data, and information on aspects of the existing DOE test procedure for CWAFs, including whether there are any issues with the current test procedure and whether it is in need of updates or revisions. Id. 
DOE published a notice of proposed 
rulemaking (NOPR) for the CWAFs test procedure in the Federal Register on 
February 25, 2022 that presented DOE’s proposals to amend that test procedure. 87 FR 10726 (February 2022 NOPR). DOE held a webinar public meeting related to this NOPR on March 29, 2022. DOE received comments in response to the February 2022 NOPR from the interested parties listed in Table I.1. 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00003 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136220 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
5The parenthetical reference provides a reference 
for information located in the docket of DOE’s 
rulemaking to develop test procedures for CWAFs. (Docket No. EERE–2019–BT–TP–0041, which is maintained at www.regulations.gov). The references are arranged as follows: (commenter name, comment docket ID number, page of that 
document). TABLE I.1—L IST OF COMMENTERS WITHWRITTEN SUBMISSIONS OR ORALCOMMENTS IN RESPONSE TO THE FEBRUARY  
2022 NOPR 
Commenter(s) Abbreviation used in this Final 
Rule Commenter type 
AAON Inc ................................................................................................ AAON ................... .......................... Manufacturer. 
Air-Conditioning, Heating, and Refrigeration Institute ............................. AHRI .............................................. Manufacturer Trade Association. 
American Gas Association and American Public Gas Association ........ AGA and APGA ............................. Utility Trade Asso ciation. 
Appliance Standards Awareness Project, and Natural Resources De-
fense Council.Joint Advocates ............................. Efficiency Advocacy Organization. 
California Energy Commission ................................................................ CEC ............................................... Efficiency Advocacy Organization. 
Carrier Corporation .................................................................................. Carrier ................... ......................... Manufacturer. 
Daikin Comfort Technologies Manufacturing .......................................... Daikin ...................................... ....... Manufacturer. 
Lennox International Inc .......................................................................... Lennox ....................... .................... Manufacturer. 
New York State Energy Research and Development Authority ............. NYSERDA ..................................... State Agency. 
Northwest Energy Efficiency Alliance ..................................................... NEEA ............................................. Efficiency Advocacy Organization. 
Pacific Gas and Electric Company, San Diego Gas and Electric, and 
Southern California Edison (collectively, the ‘‘California Investor- 
Owned Utilities’’).CA IOUs ........................................ Utilities. 
Rheem Manufacturing ............................................................................. Rheem .......................... ................. Manufacturer. 
A parenthetical reference at the end of 
a comment quotation or paraphrase 
provides the location of the item in the public record.
5To the extent that 
interested parties have provided written comments that are substantively similar to any oral comments provided during the March 29, 2022 NOPR webinar public meeting, DOE cites the written comments throughout this final rule. For the party that provided substantive oral comments at the March 29, 2022 NOPR webinar public meeting but did not submit written comments, DOE cites the public meeting transcript. 
Since publication of the February 
2022 NOPR, DOE would note the following additional developments which are relevant to this rulemaking proceeding. As discussed, EPCA requires DOE to use industry test procedures developed or recognized by AHRI or ASHRAE as referenced in ASHRAE Standard 90.1. (42 U.S.C. 6314(a)(4)(A)–(B)) The latest update to ASHRAE Standard 90.1 was released in January 2023 (ASHRAE Standard 90.1– 2022). ASHRAE Standard 90.1–2022 references ANSI Z21.47–2021 as the test method for gas-fired CWAFs and UL 727–2018 as the test method for oil-fired CWAFs. This action by ASHRAE triggered DOE’s rulemaking obligations under EPCA. As noted previously, in such cases, EPCA requires DOE to amend the Federal test procedure to be consistent with these amended industry test procedures, unless DOE determines, by rule published in the Federal Register and supported by clear and convincing evidence, that to do so would not meeting the statutory requirements related to representativeness and not being unduly burdensome. (42 U.S.C. 6314(a)(4)(B)) Furthermore, EPCA also requires that, at least once every seven years, DOE evaluate test procedures for each class of covered equipment, including those for CWAFs, to determine whether amended test procedures would more accurately or fully comply with the requirements for the test procedures to not be unduly burdensome to conduct and be reasonably designed to produce test results that reflect energy efficiency, energy use, and estimated operating costs during a representative average use cycle. (42 U.S.C. 6314(a)(1)) This rulemaking satisfies both of these statutory obligations. 
II. Synopsis of the Final Rule 
In this final rule, DOE is amending its 
test procedures for CWAFs as follows: 
(1) Reorganize the setup and testing 
provisions in 10 CFR 431.76 related to 
the determination of thermal efficiency (TE) into the newly established 10 CFR part 431, subpart D, appendix A (appendix A); 
(2) Incorporate by reference the most 
recent versions of the currently referenced industry standards: 
•UL 727–2018 (previously UL 727– 
2006) for testing oil-fired CWAFs; 
•AHRI 1500–2015 (previously HI 
BTS–2000) for performing fuel oil analysis and for calculating flue loss of oil-fired CWAFs; •ANSI Z21.47–2021 (previously 
ANSI Z21.47–2012) for testing gas-fired CWAFs; and 
•ANSI/ASHRAE 103–2022 
(previously ANSI/ASHRAE 103–2007) for testing condensing gas-fired CWAFs; 
(3) Incorporate by reference the 
standards referenced in UL 727–2018 (i.e., NFPA 97–2003 and ANSI/ASTM 
E230/230M–17), AHRI 1500–2015 (i.e., ASTM D396–14a, ASTM D240–09, ASTM D4809–09a, and ASTM D5291– 10), and ANSI Z21.47–2021 (i.e., ANSI/ 
ASME PTC 19.3–1974 (R2004)) that are necessary for performing the DOE test procedure; 
(4) Clarify how to test units with 
multiple flue outlets, and units with flue outlets having a cross-sectional area of 3.14 square inches or less; and 
(5) Establish a new test procedure at 
10 CFR part 431, subpart D, appendix B (appendix B), which generally requires testing as in appendix A, but which establishes a new metric, ‘‘TE2.’’ The new TE2 metric accounts for jacket losses and part-load operation in addition to accounting for flue losses. Manufacturers can use appendix B to make voluntary representations of TE2; representations using this test procedure are not mandatory until such time as compliance is required with amended energy conservation standards based on TE2, should DOE adopt such standards. 
The amendments adopted in this final 
rule are summarized in Table II.1 compared to the test procedure prior to amendment, as well as the reason for the change. 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00004 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136221 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
TABLE II.1—S UMMARY OF CHANGES IN THE AMENDED TESTPROCEDURE  
DOE test procedure prior to 
amendment Amended test procedures Applicable test procedure Attribution 
Referenced UL 727–2006 
for testing oil-fired CWAFs.Incorporate by reference UL 727–2018 for testing oil- 
fired CWAFs, and the standards referenced in UL 
727–2018 that are necessary in performing the DOE test procedure (i.e., NFPA 97–2003 and ANSI/ 
ASTM E230/E230M–17).appendix A and appendix 
B.Align with industry stand-
ard update. 
Referenced HI BTS–2000 
for performing fuel oil analysis and for calcu-lating flue loss of oil-fired CWAFs.Incorporate by reference AHRI 1500–2015 for per-
forming fuel oil analysis and for calculating flue loss of oil-fired CWAFs and the standards referenced in AHRI 1500–2015 that are necessary in performing the DOE test procedure (i.e., ASTM D396–14a, 
ASTM D240–09, ASTM D4809–09a, and ASTM D5291–10).appendix A and appendix 
B.Align with industry stand-
ard update. 
Referenced ANSI Z21.47– 
2012 for testing gas-fired CWAFs.Incorporate by reference ANSI Z21.47–2021 for test-
ing gas-fired CWAFs, and the standards referenced in ANSI Z21.47–2021 that are necessary in per-forming the DOE test procedure (i.e., ANSI/ASME 
PTC 19.3–1974 (R2004)).appendix A and appendix 
B.Align with industry stand-
ard update. 
Referenced ANSI/ASHRAE 
103–2007 for testing con-densing gas-fired CWAFs.Incorporate by reference ANSI/ASHRAE 103–2022 for 
testing condensing gas-fired CWAFs.appendix A and appendix 
B.Align with industry stand-
ard update. 
Did not specify how to test 
units with multiple flue outlets.Adds specifications for units with multiple flue outlets. 
Measurements made in each flue outlet shall be averaged or adjusted using a weighted average, de-pending on the input capacity of the furnace module associated with each flue outlet.appendix A and appendix 
B.Additional specification to 
improve consistency and repeatability in testing. 
Did not specify how to test 
units with flue outlets that are too small to fit nine thermocouples.Adds specifications to address units with small flue 
outlets. Units with flue outlets that are 3.14 inches or smaller in cross-sectional area may optionally use 5 thermocouples.appendix A and appendix 
B.Additional specification to 
improve consistency and repeatability in testing. 
Efficiency metric (TE) only 
accounted for flue losses and does not account for jacket losses or part-load operation.Establishes a new metric (TE2) that accounts for flue 
losses, jacket losses, and part-load operation.appendix B ........................ Improve representative-
ness. 
DOE has determined that the adopted 
amendments for the test procedure at 
appendix A described in section III of this document will not alter the measured TE of CWAFs, that the test procedures are not unduly burdensome to conduct, and that the test procedures more accurately produce test results that reflect energy efficiency, energy use, 
and estimated operating costs of CWAFs during a representative average use cycle. 
DOE has determined that the 
additional amendments for appendix B, which adopt TE2 as a new efficiency metric for CWAFs, do alter the reported efficiency of CWAFs. However, testing in accordance with the TE2 test procedure is not required until such time as compliance is required with any amended energy conservation standards based on appendix B. Prior to such date, voluntary representations of TE2 may be made, but they must be based upon use of the test procedure in appendix B. 
The amendments adopted in this final 
rule are discussed in detail in section III of this document. 
The effective date for the amended 
test procedures adopted in this final rule is 30 days after publication of this document in the Federal Register. 
Representations of energy use or energy efficiency must be based on testing in accordance with the amended test procedures beginning 360 days after the date of publication of this final rule in the Federal Register. 
III. Discussion 
In the following sections, DOE 
describes the adopted amendments to the test procedures for CWAFs. DOE also discusses issues raised by commenters on the February 2022 NOPR, along with DOE’s responses. 
A. Scope of Applicability 
This rulemaking applies to CWAFs. 
EPCA defines ‘‘warm air furnace’’ as a 
self-contained oil-fired or gas-fired furnace designed to supply heated air through ducts to spaces that require it and includes combination warm air furnace/electric air conditioning units, but does not include unit heaters and duct furnaces. (42 U.S.C. 6311(11)(A)) DOE codified the statutory definition of ‘‘warm air furnace’’ at 10 CFR 431.72. DOE defines a CWAF as a warm air furnace that is industrial equipment, and that has a capacity (rated maximum input) of 225,000 British thermal units 
(Btu) per hour or more. 10 CFR 431.72. 
In response to the February 2022 
NOPR, NEEA recommended that DOE expand the scope of CWAF coverage to include 3-phase units with a capacity less than 225,000 Btu/h. NEEA asserted that failing to do so would leave a significant portion of the CWAF market unregulated, and the commenter noted that DOE has recently proposed closing a similar regulatory gap for 3-phase small commercial air conditioners and heat pumps and variable refrigerant flow air conditioners and heat pumps with cooling capacities less than 65,000 btu/h. (NEEA, No. 24 at p. 8) 
In response, DOE notes that NEEA 
made the same recommendation in a 
comment submitted in response to a notice of proposed determination (‘‘NOPD’’) for CWAF energy conservation standards that was published in the Federal Register on 
April 26, 2022 (April 2022 NOPD). 87 FR 24455 (See Docket No. EERE–2019– BT–STD–0042, comment 34 at p. 6) Subsequently, in a final determination published in the Federal Register on 
December 23, 2022 (December 2022 Final Determination), DOE declined to 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00005 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136222 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
6The February 2022 TP NOPR proposed to 
incorporate by reference ANSI/ASHRAE 103–2017; 
however, in 2022, ASHRAE published a more recent version of the standard, ANSI/ASHRAE 103– 2022. amend the CWAF definition to include 
three-phase furnaces with capacities less than 225,000 Btu/h due to the limited potential to achieve energy savings from doing so. 87 FR 78821, 78826. DOE maintains its position from the December 2022 Final Determination that such equipment represents a small portion of the overall CWAF market, which at present does not provide an opportunity for significant energy savings. 
B. Updates to Industry Standards 
As discussed, prior to the 
amendments adopted in this final rule, 
DOE incorporated by reference in 10 CFR part 431, subpart D, the following industry test procedures: UL 727–2006, HI–BTS 2000, ANSI Z21.47–2012, and ANSI/ASHRAE Standard 103–2007. Updated versions of each of these test standards have been published since they were incorporated into the DOE test procedure. These updated test standards are UL 727–2018 (update to UL 727–2006), AHRI 1500–2015 (update to HI–BTS 2000), ANSI Z21.47–2021 (update to ANSI Z21.47–2016), and ANSI/ASHRAE Standard 103–2022
6 
(update to ANSI/ASHRAE Standard 103–2007). 
In the February 2022 NOPR, DOE 
noted several differences between versions of the industry standards incorporated by reference at that time and the more recent versions of the industry standards and sought comment on these changes. 87 FR 10726, 10730– 10735 (Feb. 25, 2022). Stakeholder comments in response these proposals in the February 2022 NOPR are discussed in the following sections. In response to the updates to the relevant industry standards, DOE is amending the Federal test procedure for CWAFs to incorporate by reference in 10 CFR part 431, subpart D, the following updated industry standards: UL 727–2018, AHRI 1500–2015, ANSI Z21.47–2021, and ANSI/ASHRAE 103–2022. 
As discussed, prior to the effective 
date of the amendments adopted in this final rule, the DOE test procedure for CWAFs was specified in 10 CFR 431.76. In this final rule, DOE is reorganizing the CWAF test procedures into two appendixes to subpart D of 10 CFR part 431: appendix A (using the current TE metric) and appendix B (using the new TE2 metric). DOE is reorganizing the test procedures in this way because, as discussed in section III.C of this document, DOE is establishing appendix B for determining the TE2. In contrast, the establishment of appendix A is editorial and for reorganization purposes. DOE has determined that creating separate appendixes for the determination of the two different metrics would help clarify which appendix corresponds to which metric. Relevant to both appendices, DOE is incorporating by reference the industry standards, as discussed in the following sections. 
1. UL 727 
The CWAF test procedure, prior to the 
amendments adopted in this final rule, 
required use of those procedures contained in UL 727–2006 that are relevant to the steady-state efficiency measurement (i.e., UL 727–2006 
sections 1 through 3; 37 through 42 (except for sections 40.4 and 40.6.2 through 40.6.7); 43.2; and 44 through 46). 
In the February 2022 NOPR, DOE 
proposed to amend the test procedure to reference UL 727–2018. 87 FR 10726, 10731 (Feb. 25, 2022). Additionally, DOE proposed to explicitly identify the provisions of UL 727–2018 that are applicable to the DOE test procedure for CWAFs, because DOE tentatively determined that the scope section of UL 727–2018 is not applicable since the scope of the DOE test procedure is defined separately in 10 CFR 431.76(a). Id. 
The February 2022 NOPR also 
discussed that UL 727–2018 has different language pertaining to temperature measurements and using potentiometers and thermocouples, and 
it also incorporates different ANSI references regarding these topics as compared to UL 727–2006. DOE tentatively determined that there was not sufficient evidence to indicate that the updates in UL 727–2018 would not meet the requirements of EPCA at 42 U.S.C. 6314(a)(2) and (3); therefore, DOE proposed to also incorporate by reference the updated ANSI standard (i.e., ANSI/ASTM E230/E230M–17) 
referenced by UL 727–2018. 87 FR 10726, 10732 (Feb. 25, 2022). 
Finally, in the February 2022 NOPR, 
DOE discussed that UL 727–2018 references NFPA 97M, ‘‘Standard Glossary of Terms Relating to Chimneys, Gas Vents and Heat Producing Appliances’’ (NFPA 97M) for definitions of the terms ‘‘combustible’’ and ‘‘noncombustible’’ but does not specify which version of NFPA 97M. DOE tentatively concluded that NFPA 97M is an outdated standard and that NFPA 97–2003, ‘‘Standard Glossary of Terms Relating to Chimneys, Vents, and Heat- Producing Appliances’’ (NFPA 97–2003) should be referenced for these definitions instead. Therefore, DOE proposed to replace references to NFPA 97M in UL 727–2018 with references to NFPA 97–2003. Id. 
DOE received comments from Daikin, 
Carrier, and AHRI supporting the proposal to reference NFPA 97–2003 rather than NFPA 97M. (Daikin, No. 25 at p. 1; Carrier, No. 22 at p. 2; AHRI, No. 17 at p. 2) DOE did not receive any comments in response to the proposals related to incorporating by reference UL 727–2018. 
For the reasons summarized in this 
document and discussed in the February 2022 NOPR, DOE is amending the DOE test procedure to incorporate by reference UL 727–2018, as well as incorporating the additional industry standards related to UL 727–2018. 
2. HI BTS and AHRI 1500 
Prior to the amendments adopted in 
this final rule, DOE’s test procedure for 
oil-fired CWAFs referenced sections of HI BTS–2000 that are relevant to fuel oil analysis and calculating percent flue loss (i.e., HI BTS–2000 sections 8.2.2, 
11.1.4, 11.1.5, and 11.1.6.2). (See 10 
CFR 431.76(c)(2) and (e)(2) in effect as of January 1, 2022.) DOE’s test procedure included these provisions because DOE previously determined that UL 727 does not provide a procedure for calculating the percent flue loss of the furnace, which is necessary in calculating the TE. Therefore, DOE incorporated by reference provisions from HI BTS–2000 to calculate the flue loss for oil-fired CWAFs. 69 FR 61916, 61917, 61940 (Oct. 21, 2004). 
In the February 2022 NOPR, DOE 
explained that in 2015, HI BTS–2000 was replaced with AHRI 1500–2015. 87 FR 10726, 10732 (Feb. 25, 2022). The February 2022 NOPR also discussed that the DOE test procedure references fuel oil analysis requirements in HI BTS– 2000 and that the fuel oil analysis requirements are different in AHRI 1500–2015. DOE tentatively determined that the differences would not impact the performance of a CWAF under test because the fuel oil analysis requirements in AHRI 1500–2015 are essentially equivalent to those in HI BTS–2000. As a result, DOE proposed to incorporate by reference AHRI 1500– 2015, including its fuel oil analysis specifications. 87 FR 10726, 10733 (Feb. 25, 2022). 
In addition, in the February 2022 
NOPR DOE noted that section 11.1.4 of HI BTS–2000 requires that the carbon dioxide (CO
2) value used in the 
calculation of the dry flue gas loss for 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00006 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136223 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
7The DOE test procedure at 10 CFR 431.76(d) 
also states that CO 2must be measured. 842 U.S.C. 6314(a)(2) requires that test 
procedures be reasonably designed to produce test 
results which reflect energy efficiency, energy use, and estimated operating costs of a type of industrial equipment (or class thereof) during a representative average use cycle (as determined by the Secretary), and shall not be unduly burdensome to conduct. 42 U.S.C. 6314(a)(3) requires that if the test procedure is a procedure for determining estimated annual operating costs, such procedure shall provide that such costs shall be calculated from measurements of energy use in a representative average-use cycle (as determined by the Secretary), and from representative average unit costs of the energy needed to operate such equipment during such cycle. oil must be the measured CO 2,7while 
section C7.2.4 of AHRI 1500–2015 
(previously section 11.1.4 in HI BTS– 2000) includes the option to calculate CO
2using the measured oxygen (O 2) 
value instead of directly measuring the CO
2value. 87 FR 10726, 10733 (Feb. 25, 
2022). DOE tentatively determined that calculating CO
2using a measured O 2 
value, as specified in AHRI 1500–2015, would provide results equivalent to the CO
2measurement currently required by 
the DOE test method, and that allowing a calculated value of CO
2would 
harmonize with the latest industry standard without increasing test burden. As such, DOE proposed to adopt the optional method specified in AHRI 1500–2015 that allows for calculation CO
2using a measured O 2value and 
requested comment on this proposal. Id. 
AHRI supported the proposal to adopt 
the optional method specified in AHRI 
1500–2015 that allows for calculation CO
2using a measured O 2value. (AHRI, 
No. 17 at p. 2) DOE did not receive any other comments related to its proposal to incorporate by reference AHRI 1500– 2015. Therefore, for the reasons discussed here and in the February 2022 NOPR, DOE is adopting the proposals related to this topic made in the February 2022 NOPR. 
3. ANSI Z21.47 
Prior to the amendments adopted in 
this final rule, the CWAF test procedure 
required the use of procedures contained in ANSI Z21.47–2012 that are relevant to the steady-state efficiency measurement (i.e., sections 1.1, 2.1 
through 2.6, 2.39, and 4.2.1 of ANSI Z21.47–2012). 
In the February 2022 NOPR, DOE 
proposed to replace the incorporation by reference of ANSI Z21.47–2012 with ANSI Z21.47–2021. 87 FR 10726, 10734 (Feb. 25, 2022). DOE explained in the February 2022 NOPR that all of the differences it had identified between the two versions of the standard were non- substantive and would not impact the test method or result. Id. However, DOE 
also noted that ANSI Z21.47–2012 requires burner operating characteristics tests to be conducted with test gas G (i.e., butane-air), while ANSI Z21.47– 
2021 allows testing for premix burners to be done with test gas H (i.e., propane- 
air) instead of test gas G at the manufacturer’s option. In the February 2022 NOPR, DOE stated that the burner operating characteristics tests (including which test gas is used for them) do not affect the TE measurement of a CWAF and requested comment on whether the option provided in section 5.4a of ANSI Z21.47–2021 to use test gas H when performing the three burner characteristics tests would impact the representativeness or burden of the thermal efficiency test. Id. 
Lennox, Daikin, Carrier, and AHRI 
stated that section 5.4a of ANSI Z21.47– 2021 is used for safety certification testing, and is unrelated to TE, and, therefore, recommended DOE should not reference this section. (Lennox, No. 19 at p. 3; Daikin, No. 25 at p. 2; Carrier, No. 22 at p. 2; AHRI, No. 17 at p. 2) Rheem also stated that the thermal efficiency test is not affected by the burner operating characteristics test. (Rheem, Public Meeting Transcript, No. 15 at p. 11) DOE received no other comments related to its proposal to incorporate by reference ANSI Z21.47– 2021. 
For the reasons discussed here and in 
the February 2022 NOPR, DOE is amending the test procedure for CWAFs to replace the incorporation by reference of ANSI Z21.47–2012 with ANSI Z21.47–2021. In addition, DOE agrees with stakeholders that section 5.4a of ANSI Z21.47–2021 does not impact TE, and, therefore, does not need to be referenced in the DOE test procedure for CWAFs. As such, DOE is not including reference to this section in the DOE test procedure. 
4. ANSI/ASHRAE 103 
Prior to adoption of the amendments 
in this final rule, DOE’s test procedure 
for gas-fired condensing CWAFs referenced ANSI/ASHRAE 103–2007. In the February 2022 NOPR, DOE proposed to amend the test procedure by removing the reference to ANSI/ ASHRAE 103–2007 and to instead reference ANSI/ASHRAE 103–2017, having determined that the only differences between the standards in the sections utilized by the CWAF test method were editorial in nature. 87 FR 10726, 10735. An updated version of ANSI/ASHRAE 103, ANSI/ASHRAE 103–2022, has since been released. DOE reviewed ANSI/ASHRAE 103–2022 and determined that, for the sections utilized in the test methods for CWAFs, there is no difference between the two versions of the standard. 
DOE did not receive any comments in 
response to its proposal to reference ANSI/ASHRAE 103–2017. 
Accordingly, for the reasons 
explained previously and because DOE has found there is no difference between ANSI/ASHRAE 103–2017 and ANSI/ ASHRAE 103–2022 in the sections utilized for the CWAFs test procedure, DOE is amending the test procedures for CWAFs to incorporate by reference 
ANSI/ASHRAE 103–2022. 
C. Thermal Efficiency Two Metric 
As previously discussed, EPCA 
requires that the test procedures for 
CWAFs be those generally accepted industry testing procedures or rating procedures developed or recognized by AHRI or ASHRAE, as referenced in ASHRAE Standard 90.1. (42 U.S.C. 6314(a)(4)(A)) If such an industry test procedure or rating procedure is amended, the Secretary shall amend the test procedure for the product as necessary to be consistent with the amended industry test procedure or rating procedure unless the Secretary determines, by rule, published in the Federal Register and supported by clear and convincing evidence, that to do so would not meet the requirements in 42 U.S.C. 6314(a)(2) and (3) related to representative use and test burden.
8(42 
U.S.C. 6314(a)(4)(B)) 
In the February 2022 NOPR, DOE 
tentatively determined that a test procedure that includes jacket loss and accounts for part-load operation would better produce test results that reflect energy efficiency, energy use, and estimated operating costs of CWAFs during a representative average use cycle. 87 FR 10726, 10735 (Feb. 25, 2022). Therefore, DOE proposed to account for these factors by establishing a new test procedure and metric for CWAFs, termed TE2. DOE proposed to establish appendix A to subpart D of 10 CFR part 431 as the test method for calculating TE and to establish a new appendix B to subpart D of 10 CFR part 431, which would contain the new test method for TE2. The proposed test procedure at appendix B would generally adopt the same changes proposed for the current test procedure at appendix A but would additionally account for jacket losses and part load operation. 87 FR 10726, 10735–10737 (Feb. 25, 2022). Additionally, DOE proposed that manufacturers would be 
permitted to make voluntary representations using TE2, and that mandatory use of the TE2 test procedure 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00007 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136224 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
would be required at such time as 
compliance is required with amended energy conservation standards based on TE2, should DOE adopt such standards. 87 FR 10726, 10737. 
DOE received several comments 
supporting DOE’s proposed test procedure for TE2 in the February 2022 NOPR. NYSERDA generally supported DOE’s efforts to establish the TE2 metric because it will improve representativeness of CWAF field performance. (NYSERDA, No. 16 at p. 2) The Joint Advocates supported DOE’s proposal to establish the TE2 metric, noting that the current TE metric only accounts for flue losses, which provides little incentive to manufacturers to adopt technologies that impact efficiency in the field, and not just TE. The Joint Advocates, therefore, stated that the TE2 metric would better reflect a representative average use cycle and would encourage design changes that would reduce energy consumption. (Joint Advocates, No. 21 at p. 1) 
DOE also received several comments 
opposing the proposed test procedure for TE2. Lennox stated that the proposed new TE2 efficiency metric and methodology is a significant change that would significantly increase the test burden, with the commenter asserting that DOE has not provided supporting data that would justify these changes. Lennox argued that introducing such changes at the NOPR stage did not allow stakeholders sufficient time to fully evaluate their impacts and provide comment. Lennox noted that in standards rulemakings, DOE has declined to adopt or propose more- stringent standards due to lack of clear and convincing evidence that standards would be economically justified, and the commenter asserted that in their review of current CWAF test procedure and standards rulemakings, DOE has not provided clear and convincing evidence to establish the TE2 metric. Therefore, Lennox recommended that DOE should limit its test procedure amendments to those related to TE; otherwise, if DOE continues to pursue TE2, the commenter argued that DOE should revert back to the RFI stage so as to allow for more stakeholder engagement regarding the proposals in the TE2 metric. Lennox also argued against adoption of the TE2 metric because of the associated cumulative regulatory burden. (Lennox, No. 19 at pp. 1–2) AHRI opposed adoption of the TE2 test procedure and metric because there was no reference to such a proposal for a new metric or any form of part-load testing in the May 2020 RFI and because DOE failed to 
include key stakeholders in the development of TE2. In addition, the commenter stated that there is not sufficient data or justification indicating that such a change to the metric would result in any additional energy savings. AHRI stated that the proposal to adopt the TE2 metric is premature, and that if DOE wishes to do so, DOE should go back to the RFI stage, conduct tests, and release data showing the new test procedure is significantly more representative than the current test procedure. AHRI also argued that the proposed TE2 metric is not economically justified, and that if DOE were to adopt energy conservation standards based on such a metric, a crosswalk would run the risk of inadvertently pushing compliant units out of the market to produce a standard that can only be met through use of condensing technology. Therefore, AHRI urged DOE to continue using the current TE metric. (AHRI, No. 17 at pp. 2–3) Daikin agreed with AHRI on this issue. (Daikin, No. 25 at p. 2) AGA and APGA stated that while they are supportive of AHRI’s comments overall, they wish to reiterate that they do not support DOE adopting the TE2 metric because it is not clear that it is more representative than the existing DOE test procedure, and because there is no evidence to support that the proposed TE2 test procedure would result in a significant change in energy savings. AGA and APGA also expressed concern that adopting energy conservation standards based on the TE2 metric would result in a standard that could only be met through use of condensing technology. (AGA and APGA, No. 23 at p. 2) Carrier acknowledged that including jacket loss and part load operation in the thermal efficiency metric would create a more representative metric but asserted that more investigation and analysis needs to be completed before doing so. (Carrier, No. 22 at p. 2) 
In response, DOE notes that the TE 
metric only accounts for flue losses as measured while the CWAF is operating at its maximum input rate. Through testing of other similar appliances (e.g., consumer furnaces), DOE has found that the efficiency can vary when the unit operates at different fuel input rates; hence, test methods for such appliances require testing at multiple fuel input rates. Therefore, DOE concludes that including more than one fuel input rate will improve representativeness of CWAF energy efficiency as compared to only testing at the maximum input rate, since it will capture performance at additional operating points. Regarding jacket losses, DOE has found that CWAFs are often installed outside, and as a result, jacket losses can contribute 
significantly to overall equipment energy use. Thus, DOE concludes that accounting for jacket losses results in a metric that is more representative of CWAF performance than a metric that ignores such losses. Further, DOE notes that the methods proposed for determining TE2, which require testing to determine jacket loss and TE, are already in use in either industry standards (e.g., ANSI Z21.47) or DOE’s 
own test method for CWAFs. Therefore, manufacturers should be familiar with the methods of testing such that reverting to an RFI would not be necessary to provide time for additional input. While DOE recognizes that additional testing at the minimum input rate and for jacket loss would increase test burden, which is discussed in more detail in section III.G, of this document, DOE has concluded that the benefit of the increased representativeness offsets the additional test burden. Additionally, DOE would make clear that representations using the TE2 metric are not mandatory until such time as compliance with a standard denominated in terms of the TE2 metric is required, should DOE adopt such a standard. In this rulemaking, DOE is not amending standards to be based on TE2; rather, DOE is making available an optional test method, should manufacturers wish to make representations of efficiency using a more comprehensive metric. If, in a future energy conservation standards rulemaking, DOE considers whether to adopt an energy conservation standard based on the TE2 metric, DOE would further weigh the benefits and burdens of doing so at that time, including the potential additional energy savings that could be achieved through use of TE2 as the regulatory metric as compared to TE and whether there is economic justification for doing so. Based on these considerations, DOE has determined to adopt the proposals in the February 2022 NOPR regarding establishing TE2 and appendix B. The following sections discuss the different components of TE2 (i.e., jacket loss and part-load operation) 
and specific comments from interested parties on those topics in more detail. 
1. Jacket Loss 
In the February 2022 NOPR, DOE 
proposed to adopt section 5.40 of ANSI 
Z21.47–2021 for the purpose of measuring jacket loss for the TE2 metric. 87 FR 10726, 10737 (Feb. 25, 2022). 
DOE also proposed to incorporate the jacket loss into the TE2 metric by subtracting it (along with flue losses) from 100 percent after applying a jacket loss factor to account for installation 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00008 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136225 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
9RTUs are packaged units that can include both 
a commercial unitary air conditioner (CUAC) and a CWAF and are designed for installation on the 
rooftop of commercial buildings. location. DOE proposed to apply a 
jacket loss factor of 1.7 for CWAFs designed for indoor installation in an unheated space (i.e., isolated 
combustion system), 3.3 for CWAFs designed for outdoor installation (including, but not limited to, CWAFs that are weatherized, or approved for resistance to wind, rain, or snow), or 0 for CWAFs designed for installation indoors within a heated space, which is consistent with the values found in ANSI/ASHRAE 103–2017. Id. DOE 
received multiple comments regarding the proposed jacket loss test procedure to be used in determining TE2. 
NEEA, the CA IOUs, and the CEC 
generally supported DOE’s proposals to include jacket loss in the TE2 metric. (NEEA, No. 24, at p. 1; CA IOUs, No. 20, at p. 1; CEC, No. 18, at p. 2) The CA IOUs and the CEC also specifically noted that the jacket loss factors are appropriate. (CA IOUs, No. 20, at p. 1; CEC, No. 18, at p. 2) 
Daikin, Carrier, and AHRI generally 
opposed DOE’s proposal to include jacket loss in the TE2 metric. (Daikin, No. 25 at p. 2; Carrier No. 22 at pp. 2– 3; AHRI No. 17 at p. 3) More specifically, Daikin stated that the burden for conducting a jacket loss test is excessive and is duplicative given that ASHRAE Standard 90.1 already requires a maximum jacket loss of 0.75 percent. (Daikin, No. 25 at p. 2) Carrier also stated that the jacket loss test, in particular the setup and data acquisition, creates additional burden on manufacturers, and that this increases with the size of the unit being tested. (Carrier No. 22 at pp. 2–3) Additionally, Carrier stated that more clarity is needed on how to properly run the test, as the industry has several methods to conduct it. (Id.) Carrier stated that while other equipment includes jacket loss in their calculation of efficiency (e.g., residential furnaces 
and AFUE), it is hard to scale this to CWAFs. Carrier also noted that with ASHRAE Standard 90.1 limiting jacket loss to 0.75 percent, many large CWAFs may be very close to this value. Additionally, Carrier stated that including the 3.3 factor for weatherized equipment creates a sizeable impact to the thermal efficiency, and that if a future energy conservation standard for TE2 is not set correctly, it would require products to operate in a range that condensing may occur. (Id.) AHRI stated that jacket losses are measured on the furnace jacket, not on the rooftop unit (RTU) jacket,
9and that furnace jackets are typically embedded far inside the RTU, which requires the CUAC/HP to be taken apart in order to reach the CWAF jacket. AHRI stated that this is an extremely burdensome task, and that manufacturers are already required to comply with ASHRAE Standard 90.1, which requires jacket loss to be less than 0.75 percent (although AHRI also noted that only the worst-case models are tested). AHRI also stated that the additional granularity of a thermal efficiency rating that incorporates jacket loss would be negligible. (AHRI No. 17 at p. 3 and 5) Rheem stated that jacket losses have to be below 1.5 percent for equipment sold in Canada and below 0.75 percent for equipment to comply with ASHRAE Standard 90.1. (Rheem, Public Meeting Transcript, No. 15 at p. 24) 
In response, DOE recognizes that 
performing an additional test to determine the jacket loss of a CWAF is more burdensome than not testing for jacket loss; however, as previously discussed, DOE has concluded that including jacket loss in the TE2 metric will provide a more representative measure of energy efficiency. DOE disagrees with AHRI that jacket losses would be negligible, as the percentage loss is included directly in the TE2 calculation. As noted by Carrier, many CWAFs may be close to the 0.75 percent requirement. Because the jacket loss percentage is multiplied by the jacket loss factor, for weatherized CWAFs designed to be installed outdoors (which represent the majority of CWAFs on the market and which have a jacket loss factor of 3.3) a jacket loss of 0.75 percent could result in a difference in TE2 of nearly 2.5 percent as compared to a unit with negligible jacket losses, which DOE considers significant. 
Regarding Carrier’s concerns that 
burden increases with the size of the unit, DOE acknowledges that additional testing burden would be incurred if manufacturers decide to test according to TE2, and may increase more significantly for larger units. However, DOE has concluded that this burden would be outweighed by the anticipated improvement in representativeness. DOE also notes that CWAFs are eligible to use alternative efficiency determination methods (AEDMs,), which are typically used by manufacturers to mitigate burden, especially for testing larger commercial equipment. Further discussion of the testing burden posed by TE2 is included in section III.G. of this document. Although DOE recognizes that TE2 
testing would be more burdensome as 
compared to TE, DOE has concluded that the TE2 test method is not unduly burdensome. Further discussion of the cost of testing is included in section III.G of this document. Additionally, DOE notes that the use of TE2 is optional at this time, and this final rule does not amend or otherwise impact the energy conservation standards for CWAFs. If DOE should propose amended standards in the future denominated in terms of the TE2 metric, DOE would consider concerns regarding condensing operation at that time. Lastly, DOE agrees with Carrier that additional clarity regarding how to conduct the test is warranted. In particular, DOE notes that section 5.40 of ANSI Z21.47–2021 is not specific as to what constitutes the ‘‘jacket.’’ Therefore, DOE clarifies that it applies the term as defined by the CSA Group standard CSA P.8–2022, ‘‘Thermal Efficiencies of Industrial and Commercial Gas-Fired Package Furnaces.’’ CSA P.8–2022 defines the jacket as the surfaces surrounding the heating section of the furnace. The jacket includes all surfaces separating the heating section from the supply air, outside air, or condenser section, including the bottom surface separating the heating section from the basepan. DOE has included a description of the jacket in accordance with this definition in section 1.2 of appendix B. 
2. Part-Load Performance 
In the February 2022 NOPR, DOE 
proposed to require that, for CWAFs 
with two-stage or modulating burners, the flue loss be determined at both the maximum and minimum input rates on the nameplate of the unit and that the jacket loss be determined at the maximum input rate and optionally at the minimum input rate. If the jacket loss were determined only at the maximum input rate, DOE proposed to assign an equivalent value at the minimum input rate. DOE proposed that TE2 would then be calculated as the average of the efficiencies determined at both the maximum and minimum input 
rates using the flue loss and jacket loss determined at each input rate, which reflects an average use case of 50 percent of the time operating at full load and 50 percent of the time operating at part-load. 87 FR 10726, 10738 (Feb. 25, 2022). 
In response to the February 2022 
NOPR, AHRI stated that unlike for air- conditioning equipment, the range in variability in performance between part- load and full-load is small and that adding part-load performance into the 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00009 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136226 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
measurement of CWAF performance 
would not add to market clarity, especially given the burden of retesting all CWAFs on the market to assess performance according to such a test procedure. (AHRI, No. 17 at pp. 3–4) 
DOE also received comments from 
several stakeholders supporting the inclusion of part-load performance in TE2. Specifically, NEEA supported the inclusion of part-load operation in the proposed TE2 metric and noted that they have observed cases where CWAFs have had reduced efficiency at part-load when compared to full-load. Therefore, NEEA concluded that including part- load efficiency in TE2 will create a more representative efficiency metric. (NEEA, No. 24 at p. 6) The CA IOUs supported DOE’s efforts to incorporate part-load operation within the TE2 metric and agreed with DOEs assertion in the February 2022 NOPR that most CWAFs have two or more stages of heating, that CWAFs spend a substantial time operating in part-load, and that including part-load performance in a TE2 metric would increase representativeness. (CA IOUs, No. 20 at pp. 1–2) The CEC supported including part-load performance in the TE2 metric and noted that CWAFs spend a large percentage of time in part-load operation. (CEC, No. 18 at p. 2) Carrier stated that part-load performance should be part of the CWAF test procedure. (Carrier, No. 22 at pp. 3–4) 
As discussed previously, DOE has 
observed during testing of similar products that efficiency can differ at full load as compared to part load and has concluded that adding testing during part-load operation would improve representativeness as compared to a test method that only requires operation at the maximum input. Therefore, DOE is adopting part-load testing in the TE2 metric, as initially proposed in the February 2022 NOPR. Regarding the need to re-test CWAFs currently rated to the TE metric, DOE notes that testing to 
determine TE2 would not be required until the compliance date of any energy conservation standards based on that metric. However, DOE concludes that the improved representativeness of the TE2 metric would outweigh the additional test burden. 
DOE also received several comments 
regarding the proposal to weight both full-load and part-load operation at 50 percent when calculating TE2. 
The CA IOUs encouraged DOE to 
continue to evaluate what full-load and part-load weighting factors would improve representativeness of an average use cycle; however, the CA IOUs stated that they do not oppose DOE’s proposal to use 50 percent weighting factors, given the lack of 
national data on such full-load and part- load performance. (CA IOUs, No. 20 at p. 2) The CEC supported the DOE’s proposal to equally weight full-load and part-load operation, but also stated that DOE should continue to evaluate the average use cycle of CWAFs. (CEC, No. 18 at p. 2) 
NEEA recommended DOE reconsider 
the proposed weighting of low and high fire in the TE2 metric. NEEA presented a figure showing the modeled proportion of time at high fire and low fire for three locations in Canada (Winnipeg, Montreal, and Toronto) and two building types (retail and warehouse). The commenter stated that modeling has shown that, in colder North American climate zones (5A, 6A, and 7), the ratio of high fire to low fire is only close to 50/50 for warehouses in these cold climates, but for other use types, the ratio was closer to 30 percent at low fire and 70 percent at high fire. NEEA stated that because the U.S. generally has warmer climate zones than Canada, NEEA would expect increased part-load operation in the U.S., and, therefore, it argued that a 50/ 50 weighting would not be representative of CWAFs in the U.S. (NEEA, No. 24 at pp. 6–7) 
The Joint Advocates encouraged DOE 
to further consider alternative weighting factors for full-load and part-load operation that they argue may be more representative of average use. The Joint Advocates also noted that the February 2022 NOPR refers to an estimate from NEEA that CWAFs spend about 10 to 20 percent of their time operating at full load, but that DOE did not use that estimate because the Department tentatively determined that the climate regions from which the estimate was derived were not representative of the U.S. The Joint Advocates urged DOE to reconsider the NEEA estimate because they understand that while total operating hours will vary significantly based on climate region, the percentage of time spent at full load is relatively constant across climate regions. (Joint Advocates, No. 21 at p. 2) 
Rheem stated that it is not appropriate 
to average the maximum and minimum thermal efficiencies and noted that in ANSI/ASHRAE 103 (i.e., the ASHRAE 
test method for consumer furnaces) 
there is a method for determining the weightings, and the unit does not run at the maximum input very often. Rheem suggested that the minimum input rate should be weighted more than the maximum input rate. (Rheem, Public Meeting Transcript, No. 15 at pp. 27–28) Daikin also stated that 50 percent weighting factors for full-load and part- load performance are not appropriate. Further, Daikin stated that the approach to weighting full-load and part-load operation in ANSI/ASHRAE 103 cannot be used for CWAFs because it was generated for residential products and the operational profile of commercial products is radically different. (Daikin, No. 25 at p. 2) Carrier commented that time spent at part-load is much longer than full-load, and, therefore, DOE’s proposed 50 percent weighting factor is not appropriate. Carrier recommended that more investigation and analysis should be performed to determine appropriate weighting factors that account for all types of furnaces (i.e., two-stage, multi-stage, and modulating). (Carrier, No. 22 at pp. 3–4) AHRI also stated that the 50 percent weighting factors proposed by DOE in the February 2022 NOPR are not representative. (AHRI, No. 17 at p. 4) 
In response, DOE notes that the 
modeling presented by NEEA shows that in the three regions in Canada, the percentage of time a CWAF could operate at high fire versus low fire varied greatly, with CWAFs in some applications operating as little as approximately 25 percent of time in high fire (and 75 percent in low fire), while CWAFs in other applications were modeled to operate more than 70 percent of time in high fire (and 30 percent in low fire). Warehouses in all three locations were modeled to operate in high fire over 50 percent of the time, while retail buildings in all three locations were modeled to operate in high fire less than 50 percent of the time. Although NEEA claimed that the warmer climate in the U.S. would result in less time operating at full load, that is not necessarily the case as CWAFs in the U.S. would likely be sized differently from those in Canada due to the reduced heating loads. As noted by the Joint Advocates, while total operating hours will vary significantly based on climate region, the percentage of time spent at full load could remain relatively constant across climate regions. Although several commenters asserted that weighting equally at 50 percent in full-load and in part-load is not representative, no other commenters presented alternative data, nor is DOE aware of any data that would be useful to better characterize the appropriate weighting factors. Therefore, in this final rule, DOE is adopting a calculation method that weights full-load and part- load operation equally. Should DOE become aware of any new data regarding time spent operating at each input rate or data specific to different furnace types in the future, DOE could consider 
VerDate Sep<11>2014 17:22 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00010 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136227 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
revising the calculation accordingly in a 
subsequent rulemaking. 
D. Electrical Energy Consumption 
In the February 2022 NOPR, DOE 
tentatively determined not to account 
for electrical energy consumption of CWAF auxiliary power components (e.g., controls and/or combustion 
blowers/fans) or the supply air fan in the CWAF test procedure. 87 FR 10726, 10739 (Feb. 25, 2022). Specifically, regarding supply fan energy consumption, DOE noted that CWAFs are typically installed within the same cabinet as a CUAC and that this energy is generally accounted for in the current CUAC test procedure, although furnace- only operation hours are not included. As such, DOE tentatively determined that energy consumption during furnace-only operation hours would be better addressed in a future amendment to the CUAC test procedure. Id. Regarding auxiliary power consumption, DOE tentatively determined that including such power consumption into a CWAF performance metric would have a negligible impact on the measured energy efficiency of a CWAF. Id. 
In response to the February 2022 
NOPR, NYSERDA encouraged DOE to measure fan energy consumption during furnace-only operation in the CWAF test procedure. (NYSERDA, No. 16 at p. 2) NEEA also recommended that DOE account for electricity consumption used in a CUAC, including fan and auxiliary energy use, that relates to CWAF energy consumption. In relation to DOE’s tentative determination in the February 2022 NOPR that such energy consumption would be better addressed in a future amendment to the CUAC test procedure, NEEA stated such an approach would likely leave out the portion of the hours during the year where fan energy is consumed when 
only the CWAF is operating. NEEA stated that it understands DOE’s desire for fan energy to ‘‘be captured in a single test procedure,’’ but the commenter argued that this goal is not achievable when cooling and heating efficiencies are regulated separately and also not achievable in a market as diverse as that for commercial HVAC. Additionally, NEEA mentioned that because fan and other auxiliary electrical end uses are integral to the function of any CWAF, it is critical than any CWAF TP and performance metric account for them. (NEEA, No. 24 at p. 4) 
After carefully considering these 
comments, DOE maintains its position presented in February 2022 NOPR that, at present, integrating the auxiliary electrical energy consumption into the 
efficiency metric for CWAF would result in negligible impact. Further, DOE also maintains that the fan efficiency is better accounted for in a single test method that addresses all fan energy consumption. Accordingly, DOE is proposing to address the supply air fan energy use for CWAFs, including during operation in heating-only mode, in the ongoing CUACs test procedure rulemaking. Therefore, DOE is not adopting measures of auxiliary electrical energy use or the electrical energy use of the supply air fan in this final rule. 
E. Other Test Procedure Updates and 
Clarifications 
In the February 2022 NOPR, DOE 
used the terms ‘‘vent hoods,’’ ‘‘vent pipes,’’ and ‘‘flue outlets’’ to describe the section of a CWAF that carries the flue gas away from the unit. DOE received a comment from AAON recommending DOE use the term ‘‘flue outlets,’’ because it is the most accurate way to describe those components. (AAON, No. 14 at p. 1) In response, DOE has determined it appropriate to use only the term ‘‘flue outlet(s)’’ in order to prevent confusion associated with using multiple terms to refer to the same outlet. As such, DOE will use the term ‘‘flue outlet(s)’’ in this final rule, as well as in appendix A and appendix B. 
1. Flue Temperature Measurement in 
Models With Multiple Flue Outlets 
In the February 2022 NOPR, DOE 
proposed to add instructions to clarify 
the test method for models with multiple flue outlets. 87 FR 10726, 10740 (Feb. 25, 2022). DOE proposed that measurements used to calculate TE (e.g., flue gas temperature, CO
2in flue 
gasses), be made separately for each flue outlet, and that they are weighted proportionally to the size of each flue outlet when calculating flue loss. Further, DOE proposed that test requirements, such as determining when equilibrium conditions occur based on the flue gas temperature, are determined based these weighted measurements. DOE noted that this proposal is predicated on the assumption that the amount (i.e., mass 
flow) of flue exhaust exiting each flue outlet is proportional to the outlet size. DOE recognized that ‘‘size’’ of the flue outlet may be measured in various ways, and, therefore, the Department proposed to specify that flue outlet size would be determined by calculating the outlet face area. DOE sought comments on these proposals. Id. 
Lennox stated that the size of the flue 
outlet may not be representative of the amount of flue exhaust passing through the flue outlet, and that DOE should 
consider relying on the supplemental testing instructions or review the input capacity for each heating section as the weighted average instead of the cross- sectional area of the flue outlet. (Lennox, No. 19 at p. 3) AHRI and Carrier supported clarifying how to test units with multiple flue outlets but recommended that the measurement and performance rating for each flue outlet should be based on input rating of each furnace module instead of the size of the flue outlet. (AHRI, No. 17 at p. 4; Carrier, No. 22 at p. 4) 
Based on these comments DOE 
understands that the flue outlet size may not directly correspond to the mass flow of flue gases exiting from that outlet. Consequently, DOE agrees that the fuel input rating for each furnace module would be a better indicator of the flue gases exiting the outlet for that specific module. Therefore, DOE amends the test procedure to clarify that for units with multiple flue gas outlets, the measurements used to calculate TE (e.g., flue gas temperature, CO
2in flue 
gasses) are to be made separately for each flue outlet, and are to be weighted proportionally to the input capacity associated with the furnace module. 
2. Flue Temperature Measurement in 
Models With Vent Space Limitations 
In the February 2022 NOPR, DOE 
noted that section 5.16 of ANSI Z21.47– 2021 specifies measuring the flue gas temperature using nine individual thermocouples placed in specific locations; however, these sections do not provide guidance on how to measure the flue gas temperature if the vent size constrains the space where the thermocouples are to be placed to the point that normal operation of the unit is inhibited when nine thermocouples are installed. 87 FR 10726, 10740 (Feb. 25, 2022). DOE proposed to specify in 
the DOE test procedure that when testing gas-fired and oil-fired CWAFs, the flue gas temperatures shall be measured using nine individual thermocouples when the flue outlet is larger than 2 inches in diameter and may optionally be measured using five individual thermocouples when the flue outlet is 2 inches or smaller in diameter, which DOE noted aligns with the approach in ANSI/ASHRAE 103–2017. Id. at 87 FR 10741. 
AAON stated that flue outlet geometry 
in CWAFs can vary in shape and that the diagram referenced in ANSI/ ASHRAE 103 only accounts for a circular geometry. Consequently, AAON recommended that the number thermocouples needed for testing should be determined by the cross- 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00011 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136228 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
10Heating value for natural gas or propane must 
be 970–1100 Btu/ft3or 2466–2542 Btu/ft3, 
respectively. Specific gravity for natural gas or 
propane must be 0.57–0.70 or 1.522–15.74, respectively. Ultimate carbon dioxide for natural gas or propane must be 11.7–12.2% or 13.73– 13.82%, respectively. 11CSA P.8–2022 is available for purchase at: 
www.csagroup.org/store/product/CSA%20P.8:22/. (Last accessed Jan. 31, 2023). sectional area of the flue outlet. (AAON, 
No. 14 at p. 1) Similarly, Lennox noted that not all flue outlets are round, and, therefore, the commenter suggested that the number of thermocouples used during the test should be determined using the face area of the flue outlet. (Lennox, No. 19 at p. 3) Carrier agreed that fewer thermocouples should be used for units with smaller flue outlets, but also recommended the determination be based on cross- sectional face area, not diameter, since flue outlets are not always circular. (Carrier, No. 22 at p. 4) AHRI supported DOE’s proposal that the number of thermocouples used be dependent on the flue outlet size; however, similar to other commenters, AHRI recommend that DOE base the determination of how many thermocouples to use on the cross-sectional area of the outlet, rather than the diameter. AHRI also further recommended DOE review and align its provisions with the requirement outlined in Figure 10 of AHRI 103. (AHRI, No. 17 at p. 4) 
DOE agrees that the determination of 
the number of thermocouples used in 
the flue outlet should be based on the area of the flue outlet, rather than diameter, because some flue outlets may not be circular. Therefore, DOE is adopting a modification to its February 2022 proposal so that the optional allowance to use 5 thermocouples rather than 9 in models with flue outlets that are 2 inches or less in diameter applies based on the cross-sectional area of the flue outlet. For a circular flue with a diameter of 2 inches, the area would be 3.14 square inches; thus, DOE is amending the test procedure to allow optional use of 5 thermocouples when testing models with a flue outlet that has a cross sectional area of 3.14 square inches or less. 
3. Flue Loss Determination 
Section 2.39 of ANSI Z21.47–2012 
and section 5.40 of ANSI Z21.47–2021 
reference Annex I for the determination of flue loss that is used in the TE calculation. Annex I includes two methods for determining flue loss—one method that uses a calculation, and one method that uses nomographs shown in Figures I.1 and I.2 of ANSI Z21.47– 2021. The nomograph method may only be used when the heating value, specific gravity, and flue gas CO
2of a CWAF fall 
within a specified range.10If these conditions are met, either calculation method may be used. In the February 2022 NOPR, DOE proposed to require that the calculation method must be used when determining flue loss because the nomograph method is not applicable for all tests, and the calculation method is likely to provide better repeatability by eliminating subjective differences in interpreting the nomograph. 87 FR 10726, 10741 (Feb. 25, 2022). 
DOE received comments from Daikin, 
Carrier, Lennox, Rheem, and AHRI that supported this proposal, and received no other comments on this topic. (Daikin, No. 25 at p. 3; Lennox, No. 19 at p. 3; Carrier, No. 22 at p. 5; Rheem, Public Meeting Transcript, No. 15 at p. 21; AHRI, No. 17 at p. 4) Based on the previously discussed rationale, DOE has determined that requiring the calculation method will help improve test repeatability. As such, DOE is requiring that the calculation method, not the nomograph method, from Annex I in ANSI Z21.47–2021 be used for the determination of flue loss. 
4. General Approach 
In response to the February 2022 
NOPR, DOE received several comments 
regarding its general approach to the test method for CWAFs. 
AGA and APGA recommend DOE 
consider implementing the recommendations for the recent National Academies of Sciences Engineering and Medicine (NASEM) on appliance standards rulemakings, whether for test procedures or energy conservation standards. (AGA and APGA, No. 23 at pp. 2–3) 
Given that this is a test procedure 
rulemaking for which DOE must meet specific statutory criteria as outlined in 42 U.S.C. 6314, the recommendations in the NASEM report, which pertain specifically to the processes by which DOE analyzes energy conservation standards, are not applicable. DOE will consider this comment in a separate rulemaking considering all covered product and covered equipment categories. 
DOE also received comments from the 
Joint Advocates and NEEA recommending that DOE consider a ‘‘whole box’’ approach for measuring the performance of CWAFs, similar to the approach found in CSA P.8–2022, ‘‘Thermal Efficiencies of Industrial and Commercial Gas-fired Package Furnaces.’’
11(Joint Advocates, No. 21 at 
pp. 1–2, NEEA, No. 24 at pp. 1–5) More specifically, the Joint Advocates and NEEA stated that while they supported DOE’s efforts to establish TE2, they encouraged DOE to evaluate the potential use of CSA P.8–2022. They asserted that CSA P.8 would more accurately represent overall efficiency of a CWAF because the new heating metric in that standard (i.e., ‘‘total heating 
season coefficient of performance’’) calculates the efficiency of a CWAF using a more holistic approach, by incorporating factors such as burner efficiency, total enclosure heat losses, fan energy consumption, and heat gains from heat recovery. Id. Similarly, 
NYSERDA also encouraged DOE to consider any forthcoming updates that may better measure the holistic energy use of CWAFs. (NYSERDA, No. 16 at p. 2) 
As discussed in section I.A of this 
document, EPCA requires that the test procedures for CWAFs be those generally accepted industry testing procedures or rating procedures developed or recognized by AHRI or ASHRAE, as referenced in ASHRAE Standard 90.1. (42 U.S.C. 6314(a)(4)(A)) If such an industry test procedure or rating procedure is amended, the Secretary shall amend the test procedure for the product as necessary to be consistent with the amended industry test procedure or rating procedure unless the Secretary determines, by rule, published in the Federal Register and supported by clear and convincing evidence, that to do so would not meet the requirements in 42 U.S.C. 6314(a)(2) and (3) related to representative use and test burden. (42 U.S.C. 6314(a)(4)(B)) In this case, the industry test standards referenced by ASHRAE Standard 90.1 are ANSI Z21.47 for gas-fired CWAFs and UL 727 for oil-fired CWAFs. The test methods adopted in this final rule incorporate by reference those industry standards, and are generally consistent with and build upon those industry standards by providing clarifications or other modifications, as necessary, to meet the requirements of EPCA. DOE has determined that the test procedures for CWAFs adopted in this final rule will produce test results which reflect energy efficiency of CWAFs during a representative average use cycle, are not unduly burdensome to conduct, as required by EPCA. Further, DOE notes that the scope of CSA P.8–2022 indicates that the standard is intended to provide ‘‘cold climate’’ performance criteria that is representative of use in colder climates found in Canada and other northern locations, which may not be representative of the U.S. as a whole. 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00012 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136229 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
12Per the sampling requirements specified at 10 
CFR 429.11(b), manufacturers are required to test at 
least two units to determine the rating for a basic model, except if only one unit of the basic model is produced. 
13DOE’s estimated initial cost to develop and 
validate an AEDM includes (1) 80 hours to develop the AEDM based on existing simulation tools; (2) an additional 16 hours to validate the AEDM for two basic models at the cost of an engineering calibration technician wage of $46 per hour; and (3) the cost of third-party testing of two units per validation class (as required in 10 CFR 429.70(c)(2)(iv)). DOE estimated the additional per basic model cost to determine efficiency using an AEDM assuming 1 hour per basic model at the cost of an engineering calibration technician wage of $46 per hour. Therefore, DOE did not find it necessary 
to move to a test method that uses the approach taken by CSA P.8–2022. In response to NYSERDA, DOE will continue to monitor future applicable industry test standard updates related to CWAFs. 
F. Effective and Compliance Dates 
The effective date for the adopted 
CWAFs test procedure amendments is 
30 days after the date of publication of this final rule in the Federal Register. 
Regarding the compliance date, EPCA 
prescribes that all representations of energy efficiency and energy use, including those made on marketing materials and product labels, must be made in accordance with an amended test procedure for CWAFs, beginning 360 days after the date of publication of 
this final rule in the Federal Register. (42 U.S.C. 6314(d)(1)) 
To the extent the modified test 
procedure adopted in this final rule is required only for the evaluation under updated CWAF energy conservation standards (i.e., standards denominated 
in terms of the new TE2 metric), compliance with the amended test procedure does not require use of such modified test procedure provisions until the compliance date of such updated standards, if adopted. 
G. Test Procedure Costs 
EPCA requires that the test 
procedures for CWAFs be those 
generally accepted industry testing procedures or rating procedures developed or recognized by either AHRI or ASHRAE, as referenced in ASHRAE Standard 90.1. (42 U.S.C. 6314(a)(4)(A)) Further, if such an industry test procedure is amended, DOE must amend its test procedure to be consistent with the amended industry test procedure unless DOE determines, by rule published in the Federal Register and supported by clear and 
convincing evidence, that such an amended test procedure would not meet the requirements in 42 U.S.C. 6314(a)(2)–(3) related to representative use and test burden. (42 U.S.C. 6314(a)(4)(B)) 
In this final rule, DOE is amending 
the test procedure for CWAFs for determining TE by incorporating by reference the most up-to-date versions of the industry test standards referenced in the DOE test procedure, and by providing additional detail for the test setup for models with multiple flue outlets and models with flue outlets having space limitations. DOE has determined that these amendments to the test procedure for determining TE would not be unduly burdensome for manufacturers to conduct, and that the 
test procedures for this equipment are consistent with the industry test procedure updates. DOE has also determined that the amendments to the test procedure for determining TE would improve the representativeness, accuracy, and reproducibility of the test results and would not be unduly burdensome to conduct. DOE expects that the test procedure in appendix A for determining TE will not increase testing costs. 
DOE is also establishing a new metric 
for CWAFs, TE2, and a new appendix B, which includes the test procedure for determining TE2. In the February 2022 NOPR, DOE estimated that the additional test cost due to the additional part-load test and jacket loss test required for the TE2 metric would be $2,200, compared to the DOE test procedure using the TE metric, which DOE estimated to be $4,200 at a third- party laboratory (i.e., a total estimated 
cost of $6,400 per tested unit for the amended TE2 test procedure). Therefore, assuming two units are tested per basic model,
12DOE estimated the 
testing cost associated with the newly proposed appendix B test procedure to 
be $12,800 per basic model. 87 FR 10726, 10741–10742 (Feb. 25, 2022). DOE also noted that in accordance with 10 CFR 429.41, CWAF manufacturers may elect to use an AEDM to rate models for the TE2 metric, which significantly reduces testing costs to industry. DOE estimated the per- manufacturer cost to develop and validate an AEDM to determine TE2 for CWAF equipment to be $17,300. DOE estimated a cost of $46 per basic model for determining energy efficiency using a validated AEDM.
1387 FR 10726, 
10742 (Feb. 25, 2022). Additionally, DOE has determined that the appendix B test procedure and TE2 calculation would alter the measured energy efficiency of a CWAF. 
DOE received multiple comments on 
the test cost and burden associated with performing the TE2 test procedure. Rheem generally stated that measuring 
jacket loss is very labor-intensive due to the need to take apart the unit and presents a burden to manufacturers. (Rheem, Public Meeting Transcript, No. 15 at pp. 23–24) AHRI asserted that there are external costs associated with this proposed test procedure change that DOE has not accounted for, including bandwidth limitations at laboratory facilities that would cause manufacturers to test internally and which could delay testing of new units while existing models are retested. (AHRI, No. 17 at p. 5) AHRI also asserted that DOE did not accurately account for the cost of performing a jacket loss test at full-load and part-load because determining compliance with ASHRAE Standard 90.1 requires that only the worst-case unit in a product 
line needs to be tested, but TE2 would require manufacturers to run the jacket loss test twice every time a unit is tested. AHRI also stated that there are no AEDMs currently available for TE2 and developing an AEDM is extremely costly due to the number of variables that need to be accounted for and modeled accurately (e.g., fan capacity, 
cabinet geometry, variation in size of the heater, and the inclusion of dampers, energy recovery ventilators (ERVs), and heat recovery ventilators (HRVs) in the airflow path). AHRI also disagreed with the Department’s estimate that the associated rerating costs would be approximately $17,400, because manufacturers will need to validate any new AEDM by testing at least two (2) basic models, which will have associated manufacturing and test costs. Instead, AHRI estimated that the cost of the test samples alone will reach upwards of $30,000 (without accounting for the AEDM development cost or test time), and that the test time must include a minimum of several days to set up for each sample, with laboratory time being very expensive. (Id.) Daikin supported AHRI’s comments on this topic and added that testing cost and burden will increase substantially if manufacturers must assess part-load conditions and jacket loss. Daikin noted that if ambient conditions must be controlled in psychometric rooms to conduct jacket loss testing, it could impact availability of those test rooms for other equipment such as commercial unitary air conditioners and heat pumps. (Daikin, No. 25 at p. 3) Carrier stated that DOE underestimated the cost to validate an AEDM, because CWAF sizes vary between 225,000 Btu/h and 2,000,000 Btu/h (which can lead to an extremely large variation in cost). Carrier stated that to create an accurate 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00013 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136230 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
14Under 42 U.S.C. 6313(a)(6)(C)(iv), if DOE 
amends standards pursuant to a six-year-lookback 
review initiated under 42 U.S.C. 6313(a)(6)(C)(i), amended standards apply a minimum of three years after publication of the amended standards. Under 42 U.S.C. 6313(a)(6)(D)(i), if DOE amends standards pursuant to an amendment to ASHRAE Standard 90.1 levels, amended standards apply a minimum of 2 years after the effective date of the minimum energy efficiency requirement in the amended ASHRAE Standard 90.1. 
15The size standards are listed by NAICS code 
and industry description and are available at: www.sba.gov/document/support-table-size- standards (Last accessed Feb. 8, 2022). AEDM, a manufacturer would need to 
consider a ‘‘worst case’’ model, and that this can cost upwards of $50,000. (Carrier, No. 22 at p. 5) 
In response, DOE notes that the 
estimated cost of testing for TE2 presented in the February 2022 NOPR is based on actual price quotations from third-party laboratories. Additionally, the estimated cost to develop an AEDM reflects 80 hours to develop the AEDM based on existing simulation tools, plus an additional 16 hours to validate the AEDM at a rate of $46 per hour, plus the cost to conduct the test on two units as required by 10 CFR 429.70(c)(2)(iv). DOE recognizes that depending on each individual manufacturer’s approach to testing and rating their models (whether based on actual testing, AEDMs, or a combination of approaches) and the number of models they would need to rate with TE2, test costs could vary significantly. DOE’s estimates are intended to represent the typical or most likely costs given the various pathways available for rating TE2. However, DOE recognizes that the costs could be higher. Although TE2 testing will be cost more than the current TE test method due to the need to perform jacket loss testing and testing at the minimum input capacity, DOE has concluded that the additional costs are not unduly burdensome and are justified due to the improved representativeness of TE2 as compared to TE. Further, because there is no requirement to make representations with TE2 at this time, DOE does not view laboratory bandwidth limitations as a significant issue. However, if DOE were to transition to standards based on the TE2 metric in the future, which would require manufacturers to make representations of TE2, DOE notes that it would provide a lead time before compliance is required, consistent with the requirements of EPCA,
14which 
should alleviate any laboratory bandwidth issues. 
IV. Procedural Issues and Regulatory 
Review 
A. Review Under Executive Orders 
12866, 13563, and 14094 
Executive Order (E.O.) 12866, 
‘‘Regulatory Planning and Review,’’ 58 FR 51735 (Oct. 4, 1993), as 
supplemented and reaffirmed by E.O. 13563, ‘‘Improving Regulation and Regulatory Review,’’ 76 FR 3821 (Jan. 21, 2011) and amended by E.O. 14094, ‘‘Modernizing Regulatory Review,’’ 88 FR 21879 (April 11, 2023), requires agencies, to the extent permitted by law, to: (1) propose or adopt a regulation only upon a reasoned determination that its benefits justify its costs (recognizing that some benefits and costs are difficult to quantify); (2) tailor regulations to impose the least burden on society, consistent with obtaining regulatory objectives, taking into account, among other things, and to the extent practicable, the costs of cumulative regulations; (3) select, in choosing among alternative regulatory approaches, those approaches that maximize net benefits (including potential economic, environmental, public health and safety, and other advantages; distributive impacts; and equity); (4) to the extent feasible, specify performance objectives, rather than specifying the behavior or manner of compliance that regulated entities must adopt; and (5) identify and assess available alternatives to direct regulation, including providing economic incentives to encourage the desired behavior, such as user fees or marketable permits, or providing information upon which choices can be made by the public. DOE emphasizes as well that E.O. 13563 requires agencies to use the best available techniques to quantify anticipated present and future benefits and costs as accurately as possible. In its guidance, the Office of Information and Regulatory Affairs (OIRA) in the Office of Management and Budget (OMB) has emphasized that such techniques may include identifying changing future compliance costs that might result from technological innovation or anticipated behavioral changes. For the reasons stated in the preamble, this final regulatory action is consistent with these principles. 
Section 6(a) of E.O. 12866 also 
requires agencies to submit ‘‘significant 
regulatory actions’’ to OIRA for review. OIRA has determined that this final regulatory action does not constitute a ‘‘significant regulatory action’’ under section 3(f) of E.O. 12866. Accordingly, this action was not submitted to OIRA for review under E.O. 12866. 
B. Review Under the Regulatory 
Flexibility Act 
The Regulatory Flexibility Act (5 
U.S.C. 601 et seq.) requires preparation 
of a final regulatory flexibility analysis (FRFA) for any final rule where the agency was first required by law to publish a proposed rule for public comment, unless the agency certifies that the rule, if promulgated, will not have a significant economic impact on a substantial number of small entities. As required by Executive Order 13272, ‘‘Proper Consideration of Small Entities in Agency Rulemaking,’’ 67 FR 53461 (August 16, 2002), DOE published procedures and policies on February 19, 2003, to ensure that the potential impacts of its rules on small entities are properly considered during the DOE rulemaking process. 68 FR 7990. DOE has made its procedures and policies available on the Office of the General Counsel’s website: www.energy.gov/gc/ office-general-counsel. DOE reviewed 
this final rule under the provisions of the Regulatory Flexibility Act and the procedures and policies published on February 19, 2003. 
On February 25, 2022, DOE published 
in the Federal Register a notice of proposed rulemaking (February 2022 NOPR) proposing to update the references in the Federal test procedure to the most recent version of the relevant industry test procedures as they relate to CWAFs, as well as to adopt a new TE2 metric. Specifically, DOE proposed to adopt two appendices to 10 CFR 431.76—appendix A for determining TE and appendix B for determining TE2. The TE test method in appendix A is similar to the current method for TE, with several clarifications and updates to incorporate by reference the most recent versions of appliable industry test standards. The TE2 test method in appendix B builds upon the TE test method in appendix A, but also accounts for jacket losses and operation at the minimum input rating. 
As part of the February 2022 NOPR, 
DOE conducted its initial regulatory flexibility analysis (IRFA). 87 FR 10726, 10742–10744 (Feb. 25, 2022). DOE used the Small Business Administration (SBA) small business size standards to determine whether manufacturers qualify as small businesses, which are listed by North American Industry Classification System (NAICS).
15The 
SBA considers a business entity to be a small business, if, together with its affiliates, it employs less than a threshold number of workers specified in 13 CFR part 121. CWAF manufacturers are classified under NAICS code 333415, ‘‘Air-Conditioning and Warm Air Heating Equipment and Commercial and Industrial Refrigeration Equipment Manufacturing.’’ In 13 CFR 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00014 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136231 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
16MAEDbS can be accessed at 
cacertappliances.energy.ca.gov/Pages/ 
ApplianceSearch.aspx (Last accessed Feb. 8, 2022). 
17Certified equipment in the CCD is listed by 
product class and can be accessed at www.regulations.doe.gov/certification-data/ #q=Product_ Group_ s%3A* (Last accessed July 15, 
2021). 
18The Dun & Bradstreet Hoovers subscription 
login is accessible online at app.dnbhoovers.com/ 
(Last accessed Feb. 8, 2023). 121.201, the SBA sets a threshold of 
1,250 employees or fewer for an entity to be considered as a small business for this category. 
DOE relied on publicly-available 
databases to identify potential small businesses that manufacture equipment covered by this rulemaking. DOE utilized the California Energy Commission’s Modernized Appliance Efficiency Database System (MAEDbS)
16and DOE’s Certification 
Compliance Database (CCD)17to 
identify potential small businesses that manufacture CWAFs covered by this rulemaking. DOE identified eight original equipment manufacturers (OEMs) of CWAFs affected by this rulemaking. DOE screened out companies that do not meet the definition of a ‘‘small business’’ or are foreign-owned and operated. DOE identified one small, domestic OEM for consideration. DOE used subscription- based business information tools (e.g., Dun & Bradstreet reports
18) to 
determine headcount and revenue of the small business. 
In the February 2022 NOPR, DOE 
determined the one small manufacturer had average annual revenues of approximately $3.3 million. Additionally, DOE identified four basic models from the small manufacturer. DOE estimated the re-rating costs for the manufacturer to be approximately $17,400 when making use of AEDMs. The cost for this small manufacturer to re-rate all basic models was estimated to be less than 1 percent of annual revenue. DOE also estimated the re- rating cost for the small manufacturer based on physical testing of all four models based on third-party laboratory testing. Relying on pricing quotes from third-party laboratories, DOE estimated costs of approximately $51,200 for the small business. The cost for this small manufacturer to re-rate all basic models with physical testing was estimated to be less than 1.6 percent of annual revenue. 87 FR 10726, 10744 (Feb. 25, 2022). 
DOE did not receive any comments on 
the number of small entities in response to the February 2022 NOPR. As discussed in section III.G of this document, DOE received several comments that suggested that the February 2022 NOPR underestimated the cost of testing for TE2 generally. However, as discussed previously, the estimated cost of testing for TE2 presented in the February 2022 NOPR is based on actual price quotations from third-party laboratories. Additionally, the estimated cost to develop an AEDM reflects 80 hours to develop the AEDM based on existing simulation tools, plus an additional 16 hours to validate the AEDM at a rate of $46 per hour, plus the cost to conduct the test on two units as required by 10 CFR 429.70(c)(2)(iv). Although DOE recognizes that each individual manufacturer’s approach to testing and rating their models (whether based on actual testing, AEDMs, or a combination of approaches) could cause test costs to vary significantly, DOE’s estimates are intended to represent the typical or most likely costs given the various pathways available for rating TE2, and, therefore, DOE maintained its estimates from the February 2022 NOPR for this final rule. 
On the basis of the de minimis 
compliance burden, DOE concludes and certifies that the cost effects accruing from this test procedure final rule would not have a ‘‘significant economic impact on a substantial number of small entities,’’ and that the preparation of a FRFA is not warranted. DOE will transmit a certification and supporting statement of factual basis to the Chief Counsel for Advocacy of the Small Business Administration for review under 5 U.S.C. 605(b). 
C. Review Under the Paperwork 
Reduction Act of 1995 
Manufacturers of CWAFs must certify 
to DOE that their products comply with any applicable energy conservation standards. To certify compliance, manufacturers must first obtain test data for their products according to the DOE test procedures, including any amendments adopted for those test procedures. DOE has established regulations for the certification and recordkeeping requirements for all covered consumer products and commercial equipment, including CWAFs. (See generally 10 CFR part 429.) The collection-of-information 
requirement for the certification and recordkeeping is subject to review and approval by OMB under the Paperwork Reduction Act (PRA). This requirement has been approved by OMB under OMB control number 1910–1400. Public reporting burden for the certification is estimated to average 35 hours per response, including the time for reviewing instructions, searching existing data sources, gathering and maintaining the data needed, and completing and reviewing the collection 
of information. 
DOE is not amending the certification 
or reporting requirements for CWAFs in this final rule. Instead, DOE may consider proposals to amend the certification requirements and reporting for CWAFs under a separate rulemaking regarding appliance and equipment certification. DOE will address changes to OMB Control Number 1910–1400 at that time, as necessary. 
Notwithstanding any other provision 
of the law, no person is required to respond to, nor shall any person be subject to a penalty for failure to comply with, a collection of information subject to the requirements of the PRA, unless that collection of information displays a currently valid OMB Control Number. 
D. Review Under the National 
Environmental Policy Act of 1969 
DOE has analyzed this regulation in 
accordance with the National Environmental Policy Act of 1969 (42 U.S.C. 4321 et seq.; NEPA) and DOE’s NEPA implementing regulations (10 CFR part 1021). In this final rule, DOE establishes test procedure amendments 
that it expects will be used to develop and implement future energy conservation standards for CWAFs. DOE has determined that this rule falls into a class of actions that are categorically excluded from review under NEPA and DOE’s implementing regulations, because it is a rulemaking that interprets or amends an existing rule or regulation that does not change the environmental effect of the rule or regulation being amended. Specifically, DOE has determined that adopting test procedures for measuring energy efficiency of consumer products and industrial equipment is consistent with activities identified in 10 CFR part 1021, subpart D, appendix A, sections A5 and A6. Accordingly, neither an environmental assessment nor an environmental impact statement is required. 
E. Review Under Executive Order 13132 
Executive Order 13132, ‘‘Federalism,’’ 
64 FR 43255 (August 10, 1999), imposes 
certain requirements on agencies formulating and implementing policies or regulations that preempt State law or that have federalism implications. The Executive order requires agencies to examine the constitutional and statutory authority supporting any action that would limit the policymaking discretion of the States and to carefully assess the necessity for such actions. The Executive order also requires agencies to have an accountable process to ensure meaningful and timely input by State 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00015 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136232 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
and local officials in the development of 
regulatory policies that have federalism implications. On March 14, 2000, DOE published a statement of policy describing the intergovernmental 
consultation process it will follow in the development of such regulations. 65 FR 13735. DOE examined this final rule and has determined that it will not have a substantial direct effect on the States, on the relationship between the national government and the States, or on the distribution of power and responsibilities among the various levels of government. EPCA governs and prescribes Federal preemption of State regulations as to energy conservation for the products that are the subject of this final rule. States can petition DOE for exemption from such preemption to the extent, and based on criteria, set forth in EPCA. (42 U.S.C. 6297(d)) No further action is required by Executive Order 13132. 
F. Review Under Executive Order 12988 
Regarding the review of existing 
regulations and the promulgation of 
new regulations, section 3(a) of Executive Order 12988, ‘‘Civil Justice Reform,’’ 61 FR 4729 (Feb. 7, 1996), imposes on Federal agencies the general duty to adhere to the following requirements: (1) eliminate drafting errors and ambiguity; (2) write regulations to minimize litigation; (3) provide a clear legal standard for affected conduct rather than a general standard; and (4) promote simplification and burden reduction. Section 3(b) of Executive Order 12988 specifically requires that executive agencies make every reasonable effort to ensure that the regulation: (1) clearly specifies the preemptive effect, if any; (2) clearly specifies any effect on existing Federal law or regulation; (3) provides a clear legal standard for affected conduct while promoting simplification and burden reduction; (4) specifies the retroactive effect, if any; (5) adequately defines key terms; and (6) addresses other important issues affecting clarity and general draftsmanship under any guidelines issued by the Attorney General. Section 3(c) of Executive Order 12988 requires Executive agencies to review regulations in light of applicable standards in sections 3(a) and 3(b) to determine whether they are met or it is unreasonable to meet one or more of them. DOE has completed the required review and determined that, to the extent permitted by law, this final rule meets the relevant standards of Executive Order 12988. G. Review Under the Unfunded 
Mandates Reform Act of 1995 
Title II of the Unfunded Mandates 
Reform Act of 1995 (UMRA) requires each Federal agency to assess the effects of Federal regulatory actions on State, local, and Tribal governments and the private sector. Public Law 104–4, sec. 201 (codified at 2 U.S.C. 1531). For a regulatory action resulting in a rule that may cause the expenditure by State, local, and Tribal governments, in the aggregate, or by the private sector of $100 million or more in any one year (adjusted annually for inflation), section 202 of UMRA requires a Federal agency to publish a written statement that estimates the resulting costs, benefits, and other effects on the national economy. (2 U.S.C. 1532(a), (b)) The UMRA also requires a Federal agency to develop an effective process to permit timely input by elected officers of State, local, and Tribal governments on a proposed ‘‘significant intergovernmental mandate,’’ and requires an agency plan for giving notice and opportunity for timely input to potentially affected small governments before establishing any requirements that might significantly or uniquely affect small governments. On March 18, 1997, DOE published a statement of policy on its process for intergovernmental consultation under UMRA. 62 FR 12820; also available at www.energy.gov/gc/office-general- counsel. DOE examined this final rule 
according to UMRA and its statement of policy and determined that the rule contains neither an intergovernmental mandate, nor a mandate that may result in the expenditure of $100 million or more in any year, so these requirements do not apply. 
H. Review Under the Treasury and 
General Government Appropriations Act, 1999 
Section 654 of the Treasury and 
General Government Appropriations Act, 1999 (Pub. L. 105–277) requires Federal agencies to issue a Family Policymaking Assessment for any rule that may affect family well-being. This final rule will not have any impact on the autonomy or integrity of the family as an institution. Accordingly, DOE has concluded that it is not necessary to prepare a Family Policymaking Assessment. 
I. Review Under Executive Order 12630 
DOE has determined under Executive 
Order 12630, ‘‘Governmental Actions 
and Interference with Constitutionally Protected Property Rights,’’ 53 FR 8859 (March 18, 1988), that this regulation will not result in any takings that might require compensation under the Fifth Amendment to the U.S. Constitution. 
J. Review Under Treasury and General 
Government Appropriations Act, 2001 
Section 515 of the Treasury and 
General Government Appropriations Act, 2001 (44 U.S.C. 3516 note) provides for agencies to review most disseminations of information to the public under guidelines established by each agency pursuant to general guidelines issued by OMB. OMB’s guidelines were published at 67 FR 8452 (Feb. 22, 2002), and DOE’s guidelines were published at 67 FR 62446 (Oct. 7, 2002). Pursuant to OMB Memorandum M–19–15, ‘‘Improving Implementation of the Information Quality Act’’ (April 24, 2019), DOE published updated guidelines which are available at www.energy.gov/sites/prod/ 
files/2019/12/f70/DOE%20Final
%20Updated%20IQA%20Guidelines%20Dec%202019.pdf. DOE has 
reviewed this final rule under the OMB and DOE guidelines and has concluded that it is consistent with applicable policies in those guidelines. 
K. Review Under Executive Order 13211 
Executive Order 13211, ‘‘Actions 
Concerning Regulations That 
Significantly Affect Energy Supply, Distribution, or Use,’’ 66 FR 28355 (May 22, 2001), requires Federal agencies to prepare and submit to OMB, a Statement of Energy Effects for any significant energy action. A ‘‘significant energy action’’ is defined as any action by an agency that promulgated or is expected to lead to promulgation of a final rule, and that: (1) is a significant regulatory action under Executive Order 12866, or any successor order; and (2) is likely to have a significant adverse effect on the supply, distribution, or use of energy; or (3) is designated by the Administrator of OIRA as a significant energy action. For any significant energy action, the agency must give a detailed statement of any adverse effects on energy supply, distribution, or use if the regulation is implemented, and of reasonable alternatives to the action and their expected benefits on energy supply, distribution, and use. 
This regulatory action to amend the 
test procedure for measuring the energy efficiency of CWAFs is not a significant regulatory action under Executive Order 12866. Moreover, it would not have a significant adverse effect on the supply, distribution, or use of energy, nor has it been designated as a significant energy action by the Administrator of OIRA. Therefore, it is not a significant energy 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00016 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136233 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
action, and, accordingly, DOE has not 
prepared a Statement of Energy Effects. 
L. Review Under Section 32 of the 
Federal Energy Administration Act of 1974 
Under section 301 of the Department 
of Energy Organization Act (Pub. L. 95– 
91; 42 U.S.C. 7101), DOE must comply with section 32 of the Federal Energy Administration Act of 1974, as amended by the Federal Energy Administration Authorization Act of 1977. (15 U.S.C. 788; FEAA) Section 32 essentially provides in relevant part that, where a proposed rule authorizes or requires use of commercial standards, the notice of proposed rulemaking must inform the public of the use and background of such standards. In addition, section 32(c) requires DOE to consult with the Attorney General and the Chairman of the Federal Trade Commission (FTC) concerning the impact of the commercial or industry standards on competition. 
The amendments to the Federal test 
procedure for CWAFs contained in this final rule adopt testing methods contained in certain sections of the following commercial standards: AHRI 1500–2015 (which in turn references ASTM D240–09, ASTM D396–14a, ASTM D4809–09a, and ASTM D5291– 10), ANSI Z21.47–2021 (which in turn references ANSI/ASME PTC 19.3–1974 (R2004)), ANSI/ASHRAE 103–2022, and UL 727–2018 (which in turn references ASTM E230/E230M–17 and NFPA 97– 2003). DOE has evaluated these standards and is unable to conclude whether they fully comply with the requirements of section 32(b) of the FEAA (i.e., whether they were 
developed in a manner that fully provides for public participation, comment, and review). DOE has consulted with both the Attorney General and the Chairman of the FTC about the impact on competition of using the methods contained in these standards and has received no comments objecting to their use. 
M. Congressional Notification 
As required by 5 U.S.C. 801, DOE will 
report to Congress on the promulgation 
of this rule before its effective date. The report will state that it has been determined that the final rule is not a ‘‘major rule’’ as defined by 5 U.S.C. 804(2). 
N. Description of Materials Incorporated 
by Reference 
In this final rule, DOE incorporates by 
reference the following test standards: 
AHRI 1500–2015 provides instruction 
for how to perform fuel oil analysis and for how to calculate flue loss of oil-fired CWAFs. 
Copies of AHRI 1500–2015 can be 
obtained from the Air-Conditioning, Heating, and Refrigeration Institute (AHRI), 2311 Wilson Blvd., Suite 400, Arlington, VA 22201, (703) 524–8800, or online at: www.ahrinet.org. 
ANSI Z21.47–2021 provides 
instruction for how to test gas-fired CWAFs. 
ANSI/ASHRAE 103–2022 provides 
instruction for how to test residential furnaces and boilers, which DOE is referencing for the purpose of providing instruction for testing condensing gas- fired CWAFs. 
ANSI/ASME PTC 19.3–1974 (R2004) 
is referenced by ANSI Z21.47–2021 and specifies thermocouple requirements for when testing gas-fired CWAFs. 
Copies of ANSI Z21.47–2021, ANSI/ 
ASHRAE 103–2022, and ANSI/ASME PTC 19.3–1974 (R2004), can be obtained the from the American National Standards Institute (ANSI), 25 W 43rd Street, 4th Floor, New York, NY 10036, (212) 642–4900, or online at: www.webstore.ansi.org. 
ASTM D240–09 is referenced in AHRI 
1500–2015, and it contains fuel oil heating value requirements. 
ASTM D396–14a is referenced in 
AHRI 1500–2015, and it contains general fuel oil requirements. 
ASTM D4809–09a is referenced in 
AHRI 1500–2015, and it contains fuel oil hydrogen and carbon content requirements. 
ASTM D5291–10 is referenced in 
AHRI 1500–2015, and it contains fuel oil density requirements. 
ASTM E230/E230M–17 is referenced 
in UL 727–2018, and it specifies thermocouple requirements for when testing oil-fired CWAFs. 
Copies of ASTM D240–09, ASTM 
D396–14a, ASTM D4809–09a, ASTM D5291–10, and ASTM E230/E230M–17 can be obtained from ASTM International, 100 Barr Harbor Drive, P.O. Box C700, West Conshohocken, PA 19428, (877) 909–2786 or online at: www.astm.org. 
NFPA 97–2003 is referenced in UL 
727–2018 and provides definitions for the terms ‘‘combustible’’ and ‘‘noncombustible.’’ 
Copies of NFPA 97–2003 can be 
obtained from the National Fire Protection Association (NFPA), 1 Batterymarch Park, Quincy, MA 02169– 7471, 1–800–344–3555 or online at: www.nfpa.org. 
UL 727–2018 provides instruction for 
how to test oil-fired CWAFs. 
Copies of UL 727–2018 can be 
obtained from Underwriters Laboratories, Inc. (UL), 333 Pfingsten Road, Northbrook, IL 60062, (847) 272– 8800, or online at: www.standardscatalog.ul.com. 
V. Approval of the Office of the 
Secretary 
The Secretary of Energy has approved 
publication of this final rule. 
List of Subjects in 10 CFR Part 431 
Administrative practice and 
procedure, Confidential business 
information, Energy conservation test procedures, Incorporation by reference, and Reporting and recordkeeping requirements. 
Signing Authority 
This document of the Department of 
Energy was signed on May 22, 2023, by 
Francisco Alejandro Moreno, Acting Assistant Secretary for Energy Efficiency and Renewable Energy, pursuant to delegated authority from the Secretary of Energy. That document with the original signature and date is maintained by DOE. For administrative purposes only, and in compliance with requirements of the Office of the Federal Register, the undersigned DOE Federal Register Liaison Officer has been authorized to sign and submit the document in electronic format for publication, as an official document of the Department of Energy. This administrative process in no way alters the legal effect of this document upon publication in the Federal Register. 
Signed in Washington, DC, on May 23, 
2023. 
Treena V. Garrett, Federal Register Liaison Officer, U.S. 
Department of Energy. 
For the reasons stated in the 
preamble, DOE amends part 431 of 
chapter II of title 10, Code of Federal Regulations as set forth below: 
PART 431—ENERGY EFFICIENCY 
PROGRAM FOR CERTAIN COMMERCIAL AND INDUSTRIAL EQUIPMENT 
■1. The authority citation for part 431 
continues to read as follows: 
Authority: 42 U.S.C. 6291–6317; 28 U.S.C. 
2461 note. 
■2. Amend § 431.72 by adding in 
alphabetical order a definition for ‘‘Thermal efficiency two’’ to read as follows: 
§ 431.72 Definitions concerning 
commercial warm air furnaces. 
* * * * * 
Thermal efficiency two for a 
commercial warm air furnace equals 100 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00017 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136234 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
percent minus percent flue loss and 
jacket loss. 
* * * * * 
■3. Revise § 431.75 to read as follows: 
§ 431.75 Materials incorporated by 
reference. 
(a) Certain material is incorporated by 
reference into this subpart with the 
approval of the Director of the Federal Register in accordance with 5 U.S.C. 552(a) and 1 CFR part 51. To enforce any edition other than that specified in this section, DOE must publish a document in the Federal Register and the material must be available to the public. All approved incorporation by reference (IBR) material is available for inspection at DOE, and at the National Archives and Records Administration (NARA). Contact DOE at: the U.S. Department of Energy, Office of Energy Efficiency and Renewable Energy, Building Technologies Program, 1000 Independence Ave. SW, EE–5B, Washington, DC 20585, (202) 586–9127, Buildings@ee.doe.gov, www.energy.gov/ eere/buildings/building-technologies- office. For information on the 
availability of this material at NARA, visit: www.archives.gov/federal-register/ 
cfr/ibr-locations.html or email: 
fr.inspection@nara.gov. The material 
may be obtained from the sources in the following paragraphs of this section. 
(b) AHRI. Air-Conditioning, Heating, 
and Refrigeration Institute, 2311 Wilson Blvd., Suite 400, Arlington, VA 22201, (703) 524–8800, or online at: www.ahrinet.org. 
(1) ANSI/AHRI 1500–2015 (‘‘AHRI 
1500–2015’’), Performance Rating of 
Commercial Space Heating Boilers, ANSI-approved November 28, 2014; IBR approved for appendix A to this subpart. 
(2) [Reserved] 
(c) ANSI. American National 
Standards Institute. 25 W 43rd Street, 
4th Floor, New York, NY 10036. (212) 642–4900 or online at: www.ansi.org. 
(1) CSA/ANSI Z21.47:21, (‘‘ANSI 
Z21.47–2021’’), Gas-fired central 
furnaces, ANSI-approved April 21, 
2021; IBR approved for appendices A and B to this subpart. 
(2) [Reserved] 
(d) ASHRAE. American Society of 
Heating, Refrigerating and Air- 
Conditioning Engineers Inc., 180 Technology Parkway NW, Peachtree Corners, Georgia 30092, (404) 636–8400, or online at: www.ashrae.org. 
(1) ANSI/ASHRAE 103–2022 
(‘‘ASHRAE 103–2022’’), Method of Testing for Annual Fuel Utilization Efficiency of Residential Central Furnaces and Boilers, approved January 10, 2022; IBR approved for appendix A to this subpart. 
(2) [Reserved] 
(e) ASME. American Society of 
Mechanical Engineers, Service Center, 
22 Law Drive, P.O. Box 2900, Fairfield, NJ 07007, (973) 882–1170, or online at: www.asme.org. 
(1) ANSI/ASME PTC 19.3–1974 
(R2004), Supplement to ASME 
Performance Test Codes: Part 3: Temperature Measurement, Instruments and Apparatus, reaffirmed 2004; IBR approved for appendix A to this subpart. 
(2) [Reserved] 
(f) ASTM. ASTM International, 100 
Barr Harbor Drive, P.O. Box C700, West 
Conshohocken, PA 19428, (877) 909– 2786, or online at: www.astm.org/. 
(1) ASTM D240–09, Standard Test 
Method for Heat of Combustion of Liquid Hydrocarbon Fuels by Bomb Calorimeter, approved July 1, 2009; IBR 
approved for appendix A to this subpart. 
(2) ASTM D396–14a, Standard 
Specification for Fuel Oils, approved October 1, 2014; IBR approved for appendix A to this subpart. 
(3) ASTM D4809–09a, Standard Test 
Method for Heat of Combustion of Liquid Hydrocarbon Fuels by Bomb Calorimeter (Precision Method); approved September 1, 2009; IBR approved for appendix A to this subpart. 
(4) ASTM D5291–10, Standard Test 
Methods for Instrumental Determination of Carbon, Hydrogen, and Nitrogen in Petroleum Products and Lubricants, approved May 1, 2010; IBR approved for appendix A to this subpart. 
(5) ASTM E230/E230M–17 (‘‘ASTM 
E230/E230M–17’’), Standard 
Specification for Temperature- Electromotive Force (emf) Tables for Standardized Thermocouples, approved November 1, 2017; IBR approved for appendix A to this subpart. 
(g) NFPA. National Fire Protection 
Association, 1 Batterymarch Park, Quincy, MA 02169–7471, 1–800–344– 3555, or online at: www.nfpa.org. 
(1) NFPA 97 (‘‘NFPA 97–2003’’), 
Standard Glossary of Terms Relating to Chimneys, Vents, and Heat-Producing Appliances; copyright 2023; IBR 
approved for appendix A to this subpart. 
(2) [Reserved] 
(h) UL. Underwriters Laboratories, 
Inc., 333 Pfingsten Road, Northbrook, IL 
60062, (847) 272–8800, or online at: www.ul.com. 
(1) UL 727 (‘‘UL 727–2018’’), 
Standard for Safety Oil-Fired Central Furnaces, Tenth Edition, published January 31, 2018; IBR approved for appendix A to this subpart. 
(2) [Reserved] 
■4. Revise § 431.76 to read as follows: 
§ 431.76 Uniform test method for the 
measurement of energy efficiency of commercial warm air furnaces. 
(a) Scope. This section prescribes the 
test requirements used to measure the 
energy efficiency of commercial warm air furnaces with a rated maximum input of 225,000 Btu per hour or more. 
(b) Testing and calculations—(1) 
Thermal efficiency. Test in accordance with appendix A to subpart D of this part when making representations of thermal efficiency. 
(2) Thermal efficiency two. Test in 
accordance with appendix B to subpart D of this part when making representations of thermal efficiency two. 
■5. Appendix A to subpart D of part 
431 is added to read as follows: 
Appendix A to Subpart D of Part 431— 
Uniform Test Method for Measurement of the Energy Efficiency of Commercial Warm Air Furnaces (Thermal Efficiency) 
Note: On and after May 28, 2024, any 
representations made with respect to the 
energy use or efficiency of commercial warm air furnaces must be made in accordance with the results of testing pursuant to this section. At that time, manufacturers must use the relevant procedures specified in this appendix, which reference ANSI Z21.47– 2021, ASHRAE 103–2022, UL 727–2018, or AHRI 1500–2015. On and after July 3, 2023 and prior to May 28, 2024, manufacturers must test commercial warm air furnaces in accordance with this appendix or 10 CFR 431.76 as it appeared on January 1, 2023. DOE notes that, because testing under this section is required as of May 28, 2024, manufacturers may wish to begin using this amended test procedure as soon as possible. Any representations made with respect to the energy use or efficiency of such commercial warm air furnaces must be made in accordance with whichever version is selected. 
Manufacturers must use the results of 
testing under appendix B to this subpart to determine compliance with any standards for commercial warm air furnaces that use the thermal efficiency 2 (TE2) metric. 
0. Incorporation by reference. In § 431.75, DOE incorporated by reference 
the entire standard for AHRI 1500–2015, ANSI Z21.47–2021, ASHRAE 103–2022, ASME PTC 19.3–1974 (R2004), ASTM D240– 09, ASTM D396–14a, ASTM D4809–09a, ASTM D5291–10, ASTM E230/E230M–17, NFPA 97–2003, and UL 727–2018. However, for standards AHRI 1500–2015, ANSI Z21.47–2021, ASHRAE 103–2022, and UL 727–2018, only the enumerated provisions of those documents apply to this appendix, as follows: 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00018 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136235 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
0.1 ANSI Z21.47–2021 
(a) Sections 5.1, 5.1.4, 5.2, 5.3, 5.4, 5.5, 
5.5.1, 5.6, and 7.2.1 as specified in section 1.1 of this appendix; 
(b) Section 5.40 as specified in sections 1.1 
and 3.1 of this appendix; 
(c) Section 5.2.8 as specified in section 4.1 
of this appendix; 
(d) Annex I as specified in section 3.1 of 
this appendix. 
0.2 ASHRAE 103–2022 (a) Sections 7.2.2.4, 7.8, and 9.2 as 
specified in section 2.2 of this appendix; 
(b) Sections 11.3.7.1 and 11.3.7.2 as 
specified in section 4.1 of this appendix. 
0.3 UL 727–2018 (a) Sections 2, 3, 37, 38 and 39, 40, 40.6, 
41, 42, 43.2, 44, 45, and 46 as specified in section 1.2 of this appendix; 
(b) Figure 40.3 as specified in section 2.1 
of this appendix. 
0.4 AHRI 1500–2015 
(a) Section C3.2.1.1 as specified in section 
1.2 of this appendix; 
(b) Sections C7.2.4, C7.2.5, and C7.2.6.2 as 
specified in section 3.2 of this appendix. 
1. Test setup and Testing. Where this 
section prescribes use of ANSI Z21.47–2021 or UL 727–2018, perform only the procedures pertinent to the measurement of the steady- state efficiency, as specified in this section. 
1.1 Gas-fired commercial warm air 
furnaces. The test setup, including flue 
requirement, instrumentation, test conditions, and measurements for determining thermal efficiency are as specified in section 1.3 of this appendix, and the following sections of ANSI Z21.47–2021: 5.1 (General, including ASME PTC 19.3–1974 (R2004) as referenced in Section 5.1.4), 5.2 (Basic test arrangements), 5.3 (Test ducts and plenums), 5.4 (Test gases), 5.5 (Test pressures and burner adjustments), 5.6 (Static pressure and air flow adjustments), 5.40 (Thermal efficiency), and 7.2.1 (Basic test arrangements for direct vent central furnaces). If section 1.3 of this appendix and ANSI Z21.47–2021 have conflicting provisions (e.g., the number of 
thermocouples that should be used when testing units with flue outlets that have a cross-sectional area of 3.14 square inches or less), follow the provisions in section 1.3 of this appendix. The thermal efficiency test must be conducted only at the normal inlet test pressure, as specified in section 5.5.1 of ANSI Z21.47–2021, and at the maximum hourly Btu input rating specified by the manufacturer for the product being tested. 
1.2 Oil-fired commercial warm air 
furnaces. The test setup, including flue 
requirement, instrumentation, test conditions, and measurement for measuring thermal efficiency is as specified in section 1.3 of this appendix and the following sections of UL 727–2018: 2 (Units of Measurement), 3 (Glossary, except that the definitions for ‘‘combustible’’ and ‘‘non- combustible’’ in sections 3.11 and 3.27 shall be as referenced in NFPA 97–2003), 37 (General), 38 and 39 (Test Installation), 40 (Instrumentation, except 40.4 and 40.6.2 through 40.6.7 which are not required for the thermal efficiency test, and including ASTM E230/E230M–17 as referenced in Sections 40.6), 41 (Initial Test Conditions), 42 (Combustion Test—Burner and Furnace), 43.2 (Operation Tests), 44 (Limit Control 
Cutout Test), 45 (Continuity of Operation Test), and 46 (Air Flow, Downflow or Horizontal Furnace Test). If section 1.3 of this appendix and UL 727–2018 have conflicting provisions (e.g., the number of 
thermocouples that should be used when testing units with flue outlets that have a cross-sectional area of 3.14 inches or less), follow the provisions in section 1.3 of this appendix. Conduct a fuel oil analysis for heating value, hydrogen content, carbon content, pounds per gallon, and American Petroleum Institute (API) gravity as specified in section C3.2.1.1 of AHRI 1500–2015, including the applicable provisions of ASTM D240–09, ASTM D4809–09a, ASTM D5291– 10, and ASTM D396–14a, as referenced. The steady-state combustion conditions, specified in section 42.1 of UL 727–2018, are attained when variations of not more than 5 °F in the 
measured flue gas temperature occur for 
three consecutive readings taken 15 minutes apart. 
1.3 Additional test setup requirements for 
gas-fired and oil-fired commercial warm air furnaces 
1.3.1 Thermocouple setup for gas-fired 
and oil-fired commercial warm air furnaces with flue outlets that have a cross-sectional area of 3.14 square inches or less. For units with flue outlets having a cross-sectional area of 3.14 square inches or less, the flue gas temperatures may optionally be measured using five individual thermocouples, instead of nine thermocouples. 
1.3.2 Procedure for flue gas 
measurements when testing units with multiple flue outlets. For units that have multiple flue outlets, record flue gas measurements (e.g., flue gas temperature, 
CO
2in the flue gasses) separately for each 
individual flue outlet and calculate a weighted-average value based on the readings of all flue outlets. To determine the weighted average for each measurement, first determine the input rating of the furnace module associated with each flue outlet. Then multiply the ratio of the input rating for the furnace module associated with each individual flue outlet to the total nameplate input rating of the furnace (i.e., the input 
rating associated with each individual flue outlet divided by the total nameplate input rating) by that flue outlet’s respective component measurement and the sum of all of the products of the calculations for all of the flue outlets to determine the weighted- average values. Use the weighted-average values to determine flue loss, and whether equilibrium conditions are met before the official test period. 
2. Additional test measurements 2.1 Determination of flue CO
2(carbon 
dioxide) or O 2(oxygen) for oil-fired 
commercial warm air furnaces. In addition to the flue temperature measurement specified in section 40.6.8 of UL 727–2018, locate one or two sampling tubes within six inches downstream from the flue temperature probe (as indicated on Figure 40.3 of UL 727–2018). If an open end tube is used, it must project into the flue one-third of the chimney connector diameter. If other methods of sampling the flue gas are used, place the sampling tube so as to obtain an average sample. There must be no air leak between 
the temperature probe and the sampling tube location. Collect the flue gas sample at the same time the flue gas temperature is recorded. The CO
2or O 2concentration of the 
flue gas must be as specified by the manufacturer for the product being tested, with a tolerance of ±0.1 percent. Determine the flue CO
2or O 2using an instrument with 
a reading error no greater than ±0.1 percent. 
2.2 Procedure for the measurement of 
condensate for a gas-fired condensing commercial warm air furnace. The test procedure for the measurement of the condensate from the flue gas under steady- state operation must be conducted as specified in sections 7.2.2.4, 7.8, and 9.2 of ASHRAE 103–2022 under the maximum rated input conditions. This condensate 
measurement must be conducted for an additional 30 minutes of steady-state operation after completion of the steady-state thermal efficiency test specified in section 1.1 of this appendix. 
3. Calculation of thermal efficiency 3.1 Gas-fired commercial warm air 
furnaces. Use the calculation procedure 
specified in Section 5.40, Thermal efficiency, of ANSI Z21.47–2021. When determining the flue loss that is used in the calculation of thermal efficiency, the calculation method specified in Annex I of ANSI Z21.47–2021 shall be used. 
3.2 Oil-fired commercial warm air 
furnaces. Calculate the percent flue loss (in 
percent of heat input rate) by following the procedure specified in sections C7.2.4, C7.2.5, and C7.2.6.2 of the AHRI 1500–2015. The thermal efficiency must be calculated as: Thermal Efficiency (percent) = 100 percent ¥ flue loss (in percent). 
4. Procedure for the calculation of the 
additional heat gain and heat loss, and adjustment to the thermal efficiency, for a condensing commercial warm air furnace. 
4.1 Calculate the latent heat gain from the 
condensation of the water vapor in the flue gas, and calculate heat loss due to the flue condensate down the drain, as specified in sections 11.3.7.1 and 11.3.7.2 of ASHRAE 103–2022, with the exception that in the equation for the heat loss due to hot condensate flowing down the drain in section 11.3.7.2, the assumed indoor temperature of 70 °F and the temperature 
term T
OAmust be replaced by the measured 
room temperature as specified in section 5.2.8 of ANSI Z21.47. 
4.2 Adjustment to the thermal efficiency 
for condensing commercial warm air furnaces. Adjust the thermal efficiency as 
calculated in section 3.1 of this appendix by adding the latent gain, expressed in percent, from the condensation of the water vapor in the flue gas, and subtracting the heat loss (due to the flue condensate down the drain), also expressed in percent, both as calculated in section 4.1 of this appendix, to obtain the thermal efficiency of a condensing furnace. 
■6. Appendix B to subpart D of part 431 
is added to read as follows: 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00019 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES136236 Federal Register / Vol. 88, No. 106 / Friday, June 2, 2023 / Rules and Regulations 
Appendix B to Subpart D of Part 431– 
Uniform Test Method for Measurement of the Energy Efficiency of Commercial Warm Air Furnaces (Thermal Efficiency Two) 
Note: Manufacturers must use the results of 
testing under this appendix B to determine 
compliance with any standards for commercial warm air furnaces that use the thermal efficiency 2 (TE2) metric. In addition, manufacturers may optionally make representations of energy use or efficiency of this equipment using TE2 as determined using this appendix starting on July 3, 2023. 
0. Incorporation by Reference. In § 431.75, DOE incorporates by reference 
the entire standard ANSI Z21.47–2021. However, only section 5.40 and Appendix J of ANSI Z21.47–2021 apply, as specified in sections 1.2 and 1.6 of this appendix. 
1. Testing 1.1 Set up and test the unit according to 
sections 0 through 4 of appendix A to this subpart, while operating the unit at the maximum nameplate input rate (i.e., full 
load). Calculate thermal efficiency (TE) using 
the procedure specified in sections 3 and 4 of appendix A to this subpart. 
1.2 For commercial warm air furnaces 
that are designed for outdoor installation (including but not limited to CWAFs that are weatherized, or approved for resistance to wind, rain, or snow), or indoor installation within an unheated space (i.e., isolated 
combustion systems), determine the jacket loss using Section 5.40 and Annex J of ANSI Z21.47–2021 while the unit is operating at the maximum nameplate input. The jacket shall consist of the surfaces surrounding the heating section of the furnace. The jacket includes all surfaces separating the heating section from the supply air, outside air, or condenser section, including the bottom surface separating the heating section from the basepan. 
1.3 For commercial warm air furnaces 
that are designed only for indoor installation within a heated space, jacket loss shall be zero. For commercial warm air furnaces that are designed for indoor installation within a heated or unheated space, multiply the jacket loss determined in section 1.2 of this appendix by 1.7. For all other commercial warm air furnaces, including commercial warm air furnaces that are designed for outdoor installation (including but not limited to CWAFs that are weatherized, or approved for resistance to wind, rain, or snow), multiply the jacket loss determined in section 1.2 of this appendix by 3.3. 
1.4 Subtract the jacket loss determined in 
section 1.3 of this appendix from the TE determined in section 1.1 of this appendix to determine the full-load efficiency. 
1.5 Set up and test the unit according to 
sections 0 through 4 of appendix A to this subpart, while operating the unit at the nameplate minimum input rate (i.e., part 
load). Calculate TE using the procedure specified in sections 3 and 4 of appendix A to this subpart. 
1.6 For commercial warm air furnaces 
that are designed for outdoor installation (including but not limited to CWAFs that are weatherized, or approved for resistance to wind, rain, or snow), or indoor installation within an unheated space (i.e., isolated 
combustion systems), determine the jacket loss using Section 5.40 and Annex J of ANSI Z21.47–2021 while the unit is operating at the minimum nameplate input. Alternatively, the jacket loss determined in section 1.2 of this appendix at the maximum nameplate input may be used. 
1.7 For commercial warm air furnaces 
that are designed only for indoor installation within a heated space, jacket loss shall be zero. For commercial warm air furnaces that are designed for indoor installation within a heated or unheated space, multiply the jacket loss determined in section 1.6 of this appendix by 1.7. For all other commercial warm air furnaces, including commercial warm air furnaces that are designed for outdoor installation (including but not limited to CWAFs that are weatherized, or approved for resistance to wind, rain, or snow), multiply the jacket loss determined in section 1.6 of this appendix by 3.3. 
1.8 Subtract the jacket loss determined in 
section 1.7 of this appendix from the TE determined in section 1.5 of this appendix to determine the part-load efficiency. 
1.9 Calculate TE2 by taking the average of 
the full-load and part-load efficiencies as determined in sections 1.4 and 1.8 of this appendix, respectively. 
[FR Doc. 2023–11341 Filed 6–1–23; 8:45 am] 
BILLING CODE 6450–01–P 
DEPARTMENT OF TRANSPORTATION 
Federal Aviation Administration 
14 CFR Part 39 
[Docket No. FAA–2023–0434; Product 
Identifier 91–NM–255–AD; Amendment 39– 22450; AD 92–02–14 R1] 
RIN 2120–AA64 
Airworthiness Directives; Airbus SAS 
Airplanes 
AGENCY : Federal Aviation 
Administration (FAA), DOT. 
ACTION : Final rule; removal. 
SUMMARY : The FAA is removing 
Airworthiness Directive (AD) 92–02–14, which applied to certain Airbus SAS Model A320 series airplanes. AD 92– 02–14 required inspection for correct installation of the flexible control cables on the overwing emergency escape slides. The FAA issued AD 92–02–14 to prevent failure of the overwing emergency escape slides to deploy, which would compromise use of the exit during an emergency. Since the FAA issued AD 92–02–14, no new occurrences of incorrect cable installations have been reported, and existing maintenance activities are adequate to prevent new occurrences. Therefore, the FAA has determined that AD 92–02–14 is no longer necessary. Accordingly, AD 92–02–14 is removed. 
DATES : This AD becomes effective June 
2, 2023. 
ADDRESSES : 
AD Docket: You may examine the AD 
docket at regulations.gov under Docket 
No. FAA–2023–0434; or in person at Docket Operations between 9 a.m. and 5 p.m., Monday through Friday, except Federal holidays. The AD docket contains this final rule, mandatory continuing airworthiness information (MCAI), any comments received, and other information. The address for Docket Operations is U.S. Department of Transportation, Docket Operations, M– 30, West Building Ground Floor, Room W12–140, 1200 New Jersey Avenue SE, Washington, DC 20590. 
FOR FURTHER INFORMATION CONTACT : Dan 
Rodina, Aerospace Engineer, International Validation Branch, FAA, 2200 South 216th St., Des Moines, WA 98198; phone 206–231–3225; email Dan.Rodina@faa.gov. 
SUPPLEMENTARY INFORMATION : 
Background 
The FAA issued a notice of proposed 
rulemaking (NPRM) to amend 14 CFR part 39 by removing AD 92–02–14, Amendment 39–8150 (57 FR 5375, February 14, 1992) (AD 92–02–14). AD 92–02–14 applied to certain Airbus SAS Model A320 series airplanes. The NPRM was published in the Federal Register on March 24, 2023 (88 FR 17751). The NPRM was prompted by the determination that AD 92–02–14 is no longer necessary. AD 92–02–14 required inspection for correct installation of the flexible control cables on the overwing emergency escape slides. The FAA issued AD 92–02–14 to prevent failure of the overwing emergency escape slides to deploy, which would compromise use of the exit during an emergency. Since the FAA issued AD 92–02–14, no new occurrences of incorrect cable installations have been reported, and existing maintenance activities are adequate to prevent new occurrences. The NPRM proposed to remove AD 92– 02–14. The FAA is issuing this AD to remove AD 92–02–14. 
Discussion of Final Airworthiness 
Directive 
Comments 
The FAA received a comment from 
The Air Line Pilots Association, 
International (ALPA), in support of the NPRM without change. 
VerDate Sep<11>2014 16:04 Jun 01, 2023 Jkt 259001 PO 00000 Frm 00020 Fmt 4700 Sfmt 4700 E:\FR\FM\02JNR1.SGM 02JNR1lotter on DSK11XQN23PROD with RULES1