section_path: Methods of refrigeration/Cyclic refrigeration/Vapor-compression cycle
section_name: Vapor-compression cycle
paragraph_text: Vapor-compression cycle
  
  The vapor-compression cycle is used in most household refrigerators as well as in many large commercial and industrial refrigeration systems. Figure 1 provides a schematic diagram of the components of a typical vapor-compression refrigeration system.
  
  The thermodynamics of the cycle can be analyzed on a diagram as shown in Figure 2. In this cycle, a circulating refrigerant such as a low boiling hydrocarbon or hydrofluorocarbons enters the compressor as a vapour. From point 1 to point 2, the vapor is compressed at constant entropy and exits the compressor as a vapor at a higher temperature, but still below the vapor pressure at that temperature. From point 2 to point 3 and on to point 4, the vapor travels through the condenser which cools the vapour until it starts condensing, and then condenses the vapor into a liquid by removing additional heat at constant pressure and temperature. Between points 4 and 5, the liquid refrigerant goes through the expansion valve (also called a throttle valve) where its pressure abruptly decreases, causing flash evaporation and auto-refrigeration of, typically, less than half of the liquid.
  
  That results in a mixture of liquid and vapour at a lower temperature and pressure as shown at point 5. The cold liquid-vapor mixture then travels through the evaporator coil or tubes and is completely vaporized by cooling the warm air (from the space being refrigerated) being blown by a fan across the evaporator coil or tubes. The resulting refrigerant vapour returns to the compressor inlet at point 1 to complete the thermodynamic cycle.
  
  The above discussion is based on the ideal vapour-compression refrigeration cycle, and does not take into account real-world effects like frictional pressure drop in the system, slight thermodynamic irreversibility during the compression of the refrigerant vapor, or non-ideal gas behavior, if any. Vapor compression refrigerators can be arranged in two stages in cascade refrigeration systems, with the second stage cooling the condenser of the first stage. This can be used for achieving very low temperatures.
  
  More information about the design and performance of vapor-compression refrigeration systems is available in the classic Perry's Chemical Engineers' Handbook.