Friction loss takes place as a gas, say air, flows through duct work.
The difference in the character of the flow from the case of water in a pipe stems from the differing Reynolds number Re and the roughness of the duct.
The friction loss is customarily given as pressure loss for a given duct length, Δp / L, in units of (US) inches of water for 100 feet or (SI) kg / m / s.
For specific choices of duct material, and assuming air at standard temperature and pressure (STP), standard charts can be used to calculate the expected friction loss. The chart exhibited in this section can be used to graphically determine the required diameter of duct to be installed in an application where the volume of flow is determined and where the goal is to keep the pressure loss per unit length of duct S below some target value in all portions of the system under study. First, select the desired pressure loss Δp / L, say 1 kg / m / s (0.12 in HO per 100 ft) on the vertical axis (ordinate). Next scan horizontally to the needed flow volume Q, say 1 m / s (2000 cfm): the choice of duct with diameter D = 0.5 m (20 in.) will result in a pressure loss rate Δp / L less than the target value. Note in passing that selecting a duct with diameter D = 0.6 m (24 in.) will result in a loss Δp / L of 0.02 kg / m / s (0.02 in HO per 100 ft), illustrating the great gains in blower efficiency to be achieved by using modestly larger ducts.
The following table gives flow rate Q such that friction loss per unit length Δp / L (SI kg / m / s) is  0.082, 0.245, and 0.816, respectively, for a variety of nominal duct sizes. The three values chosen for friction loss correspond to, in US units inch water column per 100 feet, 0.01, .03, and 0.1. Note that, in approximation, for a given value of flow volume, a step up in duct size (say from 100mm to 120mm) will reduce the friction loss by a factor of 3. 
Note that, for the chart and table presented here, flow is in the turbulent, smooth pipe domain, with R* < 5 in all cases.