The manufacture and installation of pressure piping is tightly regulated by the ASME "B31" code series such as B31.1 or B31.3 which have their basis in the ASME Boiler and Pressure Vessel Code (BPVC). This code has the force of law in Canada and the US. Europe and the rest of the world has an equivalent system of codes. Pressure piping is generally pipe that must carry pressures greater than 10 to 25 atmospheres, although definitions vary. To ensure safe operation of the system, the manufacture, storage, welding, testing, etc. of pressure piping must meet stringent quality standards.
Manufacturing standards for pipes commonly require a test of chemical composition and a series of mechanical strength tests for each heat of pipe. A heat of pipe is all forged from the same cast ingot, and therefore had the same chemical composition. Mechanical tests may be associated to a lot of pipe, which would be all from the same heat and have been through the same heat treatment processes. The manufacturer performs these tests and reports the composition in a mill traceability report and the mechanical tests in a material test report, both of which are referred to by the acronym MTR. Material with these associated test reports is called traceable. For critical applications, third party verification of these tests may be required; in this case an independent lab will produce a certified material test report(CMTR), and the material will be called certified.
Some widely used pipe standards or piping classes are:
* The API range – now ISO 3183. E.g.: API 5L Grade B – now ISO L245 where the number indicates yield strength in MPa
* ASME SA106 Grade B (Seamless carbon steel pipe for high temperature service)
* ASTM A312 (Seamless and welded austenitic stainless steel pipe)
* ASTM C76 (Concrete Pipe)
* ASTM D3033/3034 (PVC Pipe)
* ASTM D2239 (Polyethylene Pipe)
* ISO 14692 (Petroleum and natural gas industries. Glass-reinforced plastics (GRP) piping. Qualification and manufacture)
* ASTM A36 (Carbon steel pipe for structural or low pressure use)
* ASTM A795 (Steel pipe specifically for fire sprinkler systems)
API 5L was changed in the second half of 2008 to edition 44 from edition 43 to make it identical to ISO 3183.  It is important to note that the change has created the requirement that sour service, ERW pipe, pass a hydrogen induced cracking (HIC) test per NACE TM0284 in order to be used for sour service.   
* ACPA [American Concrete Pipe Association]
* AWWA [American Water Works Association]
* AWWA M45