If the general water speed or the degree of local turbulence in an installation is high, the protective film that would normally be formed on a copper tube as a result of slight initial corrosion, may be torn off the surface locally, permitting further corrosion to take place at that point. If this process continues it can produce deep localised attack of the type known as erosion-corrosion or impingement damage. The actual attack on the metal is by the corrosive action of the water to which it is exposed while the erosive factor is the mechanical removal of the corrosion product from the surface.
Impingement attack produces highly characteristic water-swept pits, which are often horseshoe shaped, or it can produce broader areas of attack. The leading edge of the pit is frequently undercut by the swirling action of the water. Usually, the surface of the metal within the pits or areas of attack is smooth and carries no substantial corrosion product. Erosion-corrosion is known to occur in pumped-circulation hot water distribution systems, and even in cold water distribution systems, if the water velocities are too high. The factors influencing the attack include the chemical character of the water passing through the system, the temperature, the average water velocity in the system and the presence of any local features likely to induce turbulence in the water stream.
It is unusual for the general water velocity in a system to be so high that impingement attack occurs throughout the whole of the copper pipework. More commonly, the velocity is just sufficiently low for satisfactory protective films to be formed and to remain in position on most of the system, with impingement damage more likely to occur where there is an abrupt change in the direction of water flow giving rise to a high degree of turbulence, such as at tee pieces and elbow fittings. It is not generally realised how great an effect small obstructions can have on the flow pattern of water in a pipe-work system and the extent to which they can induce turbulence and cause corrosion-erosion. For example, it is most important, as far as possible, to ensure that copper tubes cut with a tube cutter are deburred before making the joint. Also a gap between the tube end and the stop in the fitting, due to the tube not having been cut to the correct length and fully inserted into the socket of the fitting, can also induce turbulence in the water stream.